1 /2010 US/CA (en) For the user User s Instructions Condensing gas boiler Logamax plus GB162-L.B. 80 kw/100 kw Please read thoroughly before operating This manual is available in the English and French language. This manual must be retained for future use.
2 Warning: If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. Do not store or use gasoline or other flammable vapors and liquids in the vicinity of this or any other boiler. What to do if you smell gas Do not try to light any boiler. Do not touch any electrical switch; do not use any phone in your building. Immediately call your gas supplier from a neighbor s phone. Follow the gas supplier s instructions. If you cannot reach your gas supplier, call the fire department. Installation and service must be performed by a qualified installer, service agency or the gas supplier. CAUTION! The operating manual is part of the documentation that is delivered to the installation's operator. Go through the information in this manual with the owner/operator and make sure that he or she is familiar with all the necessary operating instructions. 2
3 Contents 1 For your safety Designated use Safety instructions Quality of the heating system water Lighting Instructions Operating the BC10 basic controller General Switching ON and OFF Setting the DHW temperature value Setting the space heating water temperature "Burner ON" LED Other functions and economic heating 17 4 Starting up the boiler Boiler settings Check the system pressure Fill the heating system Frost protection Shutting down the boiler Operating and error messages Normal operation menu Manual Operation menu Settings menu Display codes Identifying and resetting faults
4 Preface About these instructions These user's Instructions contain important information for the safe and proper operation of Logamax plus GB162-L.B. 80kW/100kW condensing gas boilers. If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. Subject to technical changes! Changes may be made following technical improvements! Updating of documentation Please contact us if you have any suggestions for improvements or corrections. 4
5 For your safety 1 For your safety Logamax plus GB162 L.B. condensing gas boilers are designed and built according to the latest technological advances and safety requirements. The design is specifically focused on ease of use. To ensure the safe, economical and environmentally friendly use of the heating system we urge you to read and observe the User's Instructions. 1.1 Designated use The boiler was designed for heating water for a central heating system and generating domestic hot water. The boiler can be installed either as a single system or as part of a multiple system (cascade system) with a maximum of 8 boilers connected together. Hazard definitions A DANGER Indicates the presence of hazards that will cause severe personal injury, death or substantial property damage. A WARNING Indicates the presence of hazards that can cause severe personal injury, death or substantial property damage. A CAUTION Indicates presence of hazards that will or can cause minor personal injury or property damage. H CAUTION Risk of electric shock. Indicates presence of hazards due to electric shock. 5
6 For your safety I NOTICE Indicates special instructions on installation, operation or maintenance that are important but not related to personal injury or property damage. 1.2 Safety instructions Make sure to observe these safety instructions. Failure to do so can result in property damage, personal injury or loss of life. Installation, gas and flue connection, commissioning, electrical connection and maintenance activities must only be carried out by a trained service provider. Certain work, e.g. on gas lines, may require a professional license. Only carry out such work if you are licensed to do so. Only use the boiler for its intended purpose and only when it is in working order. Have a trained service provider check, clean and service the heating system once a year. Buderus recommends a contract for annual service and maintenance. The condensate collection and disposal system must be periodically cleaned by a trained service technician. Have your trained service provider give you detailed instructions about the operation of the heating system. Carefully read these user's instructions. Immediately have all defects to the heating system repaired. Ensure that air intake and outlet openings are open and free from obstructions at all times. 6
7 Do not store any flammable material or liquids in the immediate vicinity of the boiler. Never use chlorinated detergents or halogenated hydrocarbons (e.g. in spraycans, solvents and detergents, paints, adhesives) in the room where the boiler is installed. When Calcium Chloride is present in concrete floors (when poured in winter) it is necessary to seal the floor with a suitable paint. Do not allow too much dust to collect on the device. Do not use the boiler if any part has been under water. Immediately call a trained service technician to inspect the boiler and to replace any part of the control system and any gas control which has been under water. For your safety Should overheating occur or the gas supply fails to shut off, do not turn off or disconnect the electrical supply to the pump. Instead, shut off the gas supply at a location external to the boiler. The venting system must be inspected annually. Replace any parts which show deterioration from corrosion or any other sources. This boiler does not have a pilot. It has an ignition device which automatically lights the burner. Check for smell of gas around the boiler area. Be sure to smell next to the floor because propane gas is heavier than air and will settle on the floor. Use only your hand to turn the gas control knob (fig. 4 on page 18). Never use tools. If the knob will not turn by hand, don't try to 7
8 For your safety repair it, call a trained service technician. Force or attempted repair may result in a fire or an explosion. When the vent system is blocked, this boiler will shut off automatically with code '3C'. Immediately call a trained service technician to inspect and reset the boiler. 1.3 Quality of the heating system water Use only untreated tap water when filling or topping up the heating system. The use of unsuitable heating system water will lead to build-ups of sludge and corrosion, which can in turn result in the malfunctioning of the boiler and damage to the heat exchanger. DO NOT treat the water with products such as ph-adjusting substances (chemical additives) and antifreeze or water softeners. 8
9 Lighting Instructions 2 Lighting Instructions A STOP! Read the chapter "For your safety" on page 5 before lighting the boiler. Follow the instructions to start up the boiler in Starting up the boiler on page
10 3 Operating the BC10 basic controller Operating the BC10 basic controller Fig. 1 Logamatic BC10 basic controller Controls 1: Main power switch 5: Service Tool connector 2: "Reset" button 6: LED "Burner operation" 3: "Chimney sweep" button 7: LED "Heating system status" 4: "Service" button 8: Space heating water temperature knob 9: Display 10: DHW temperature knob 11: LED "DHW status" 10
11 3.1 General The boiler is equipped with a control unit, the BC10 basic controller (fig. 2). This controller can be used to control the heating system. Operating the BC10 basic controller I NOTICE If your heating system consists of several boilers (cascade system), you have to carry out the settings on the control units of all individual boilers. Push on the control panel to open it (fig. 2) and get access to the controller. Fig. 2 Opening the control panel 3.2 Switching ON and OFF Set the main switch on the BC10 to position "1" (ON) to switch ON the boiler and set it to "0" to switch the boiler OFF. 11
12 Operating the BC10 basic controller H CAUTION Risk of electric shock. If a hazardous situation occurs, shut OFF power to the boiler using the emergency shutoff switch or the boiler circuit breaker (see chapter 4 "Starting up the boiler", page 18). Make yourself familiar with the location of the emergency shutoff switch and the boiler loop circuit breaker. 3.3 Setting the DHW temperature value Check the local code for the max. DHW temperature. Turn the "DHW temperature" rotary knob to set the desired temperature of the hot water in the DHW tank
13 Operating the BC10 basic controller Condition Explanation LED 0 OFF No hot water supply (only heating mode). OFF Eco 1 Economy mode, Hot water temperature 140 F (60 C) The DHW will only be reheated to 140 F (60 C), if the temperature has signifcantly fallen. This reduces the number of burner starts and saves energy. As a result the water may be a bit cooler initially. ON Direct setting on BC10 in F Aut Entry via thermostat (presetting) The temperature set on the BC10 is a fixed temperature that cannot be changed using a RC thermostat. The temperature setting defaults to the maximum DHW temperature of 140 F (60 C). ON 2 ON 2 Table 1 Settings of "DHW temperature" knob 1 This function has been optimized for boilers with combined DHW heating (combi-units). 2 The LED under the rotary knob lights if the DHW temperature is below the target value (heat request for DHW). 13
14 Operating the BC10 basic controller Anti-scald table Temperature of water Minimum time for first degree burn Minimum time for second or third degree burn 111 F (44 C) 5 hours 7 hours 116 F (47 C) 35 minutes 45 minutes 118 F (48 C) 10 minutes 14 minutes 122 F (50 C) 1 minute 5 minutes 131 F (55 C) 5 seconds 25 seconds 140 F (60 C) 2 seconds 5 seconds 149 F (65 C) 1 second 2 seconds 158 F (70 C) 1 second Table 2 Temperature/Time/Burn Chart 14
15 Operating the BC10 basic controller 3.4 Setting the space heating water temperature Turn the "space heating water temperature" knob to set the upper limit value of the heater water for the heating operation. This limitation does not apply to DHW preparation
16 Operating the BC10 basic controller Condition Explanation LED 0 OFF No supply to heating system (only DHW heating operation). OFF Direct setting on BC10 in F The temperature set on the BC10 acts as a high limit. ON 1 With a AM10 or RC10 control, the water temperature will be at a equal or lesser value. With a On/Off thermostat the water temperature will always be the set temperature. Supply temperature never rises above the set temperature. Aut Entry via thermostat (presetting) The temperature high limit setting defaults to the ON 1 maximum boiler water temperature of 180 F (82 C). Table 3 Settings of "space heating water temperature" rotary knob 1 The LED under the rotary knob lights when the heating system is switched ON and heat is requested. In summer mode the heating system is switched OFF (LED OFF). 16
17 Operating the BC10 basic controller 3.5 "Burner ON" LED The LED indicates the operating condition of the burner. LED Condition Explanation ON Burner active The water in the boiler is being heated. OFF Burner OFF The water in the boiler has reached the required temperature or there is no heat request. Table 4 LED indication 3.6 Other functions and economic heating The functions described above are basic functions, carried out directly on the boiler using the BC10 basic controller. 17
18 Starting up the boiler 4 Starting up the boiler 4.1 Boiler settings Turn the "space heating water temperature" and "DHW temperature" rotary knobs to "Aut" (automatic mode). The control unit will now take control Slowly open the gas valve by pushing on the gas valve and turning it ¼ rotation in an counterclockwise direction (fig. 3, pos. 1). The gas valve is open when it is in its vertical position. Open the pump group isolating valves (fig. 3, pos. 2). 1 2 Fig. 3 Opening gas- and isolating valves 18
19 Starting up the boiler Set the main switch on the basic controller to position "1" (ON). The basic controller checks the current system status and the burner becomes operational as soon as there is a heat request. This procedure takes approx. 30 seconds. Adjust the settings on the control unit (see the Operating Instructions for the control unit). 4.2 Check the system pressure If the heating system has just been filled, the system pressure must initially be checked every day, for 1 week. The maximum pressure in the heating system, measured directly at the boiler, must not exceed 51 psi (3.5 bar). Press the "Service" button (fig. 1, pos. 4) until the system pressure ("P22") is shown in the display (pos. 9). 19
20 Starting up the boiler Fill the heating system if the system pressure has dropped below 15 psi (1.0 bar) according to paragraph Fill the heating system on page Fill the heating system Remove the lower casing from the pump group (fig. 4). Fig. 4 Removing the lower casing 20
21 Starting up the boiler Unscrew the sealing cap (fig. 5). Fig. 5 Removing cap from drain cock 21
22 Starting up the boiler Fill the heating system to a pressure of appx. 20 psi (1.5 bar). Read the pressure from the pressure gauge on the pump group or on the 10 psi control panel of the BC10 (fig. 6). 110 The pressure in the heating system, which is measured directly at the boiler, must be at least 140 P22 equal to the required pre-pressure of the expansion vessel plus 7 psi (0.5 bar). The minimum pressure 1 must not be less than 15 psi (1.0 bar) (if the heating system is cold). The maximum pressure in the heating system must not exceed 50 psi (3.5 bar). Fig. 6 Reading the pressure gauge I NOTICE It is very important that the heating system is now purged, since all air will collect at the highest point of the heating system when the system is slowly filled with water
23 Purge the heating system via the air vents/valves on the heating bodies. Start at the first floor of the premises and then work your way up (fig. 7). The pressure loss in a heating system is caused by air bubbles escaping via fittings and (automatic) air vents. The oxygen contained in the fresh heating water will also escape from the heating water after some time and cause a pressure loss. Topping up once a year is normal. If it is necessary to top up more frequently, there might be a leak in the system or a defective expansion vessel. This must be remedied as soon as possible. 4.4 Frost protection When switched on, the boiler has an integrated frost protection system. This means that no further frost protection facilities should be installed on the boiler. The frost protection switches the boiler on at a flow temperature of 45 F (7 C) and off at a flow temperature of 59 F (15 C). The heating system itself is not protected against frost. Fig. 7 Starting up the boiler Purging a radiator (example) 23
24 Shutting down the boiler 5 Shutting down the boiler Set the main switch on the basic controller to position "0" (OFF). Close the gas shut-off valve and disconnect the boiler from the power supply. A DANGER The heating system may freeze if it is not operational in times of freezing weather. Protect the heating system against freezing if there is a danger of frost affecting the system. Drain the heating system water from the lowest point of the heating system using the boiler filling and draining cock. The vent screw at the highest point of the heating system must then be open. 24
25 Operating and error messages 6 Operating and error messages In normal operating mode, the display shows the current heater water temperature. You can display other information using the "Service" button. Also see section 6.4. Push the "Service" button (pos. 4) a number of times to switch between the various status displays Normal operation menu Fig. 8 Basic controller BC10 Normal Operation menu [\/2/4 Shows currently measured space heating water temperature in F. e [p/2/2 Shows currently measured system pressure in psi. e [-/h/\ Current display code. In this case: Operating phase: Boiler in heating mode. Table 5 Normal operation 25
26 Operating and error messages 6.2 Manual Operation menu In manual mode, the heating system can be operated independent of a room controller (e. g. RC35). I NOTICE Re-start manual operation after switching on the heating system, so that the system is permanently in operation (especially if there is a risk of freezing). Manual Operation menu To activate manual operation: Press and hold the d button for more than 5 seconds. d [\/2/4} A flashing dot in the right-hand bottom corner of the display shows manual operation is active. This means that the boiler is permanently in heating mode: Space heating water temperature is as set on the BC10 basic controller. The LED "Heating system status" lights. DHW mode is possible during manual operation. e [p/1.6} Shows currently measured system pressure in psi(pounds per square inch). Table 6 Manual operation 26
27 Operating and error messages Manual Operation menu e [-/h/\} Display code: Operating phase: Also see section 6.4. The boiler is in manual operation mode. During manual operation the "Settings" menu (table 7 from step 2) can be used to temporarily change the target boiler performance. Notice: If the boiler output has been changed temporarily, this must be set again after ending manual operation, according to the "Settings" menu (table 7). e [\/2/4}Shows currently measured space heating water temperature in F. After a power interruption manual operation ends automatically. To end manually press and hold the d button for more than 2 seconds until the dot disappears. Table 6 Manual operation (continued) 27
28 Operating and error messages 6.3 Settings menu Three settings can be made in the Settings menu: Modulation rate Post purge time DHW mode (On/off). I NOTICE The modulation rate and the DHW mode should be set by a trained installer. If you will be on vacation for a long period while there is a risk of freezing, the post purge time will have to be set (section 4.1 on page 18). Settings menu d e Table 7 To open the "Settings" menu: Press and hold the d+ e buttons for more than 2 seconds. [l/?/? This shows the "Settings" menu is open. You can adjust the setting of this parameter. Settings 28
29 Settings menu e Table 7 Operating and error messages [l/?/? modulation rate. Adjust as follows, or press e: Lower:Decrease the modulation rate with the c button. The minimum setting is [l/3/6 = 36 % with an 80-kW boiler and [l/3/0 = 30 % with a 100-kW boiler. Higher: Increase the modulation rate with the d button. The maximum setting is [l/?/? = 100 %. This is equal to the factory setting. [f/\/5 Pump run-over time in minutes (starts when the heating mode has ended). Adjust as follows or or go to the next step: Lower: Decrease the time with the c button. The minimum setting is [f/\/0 = 0 minutes. The factory default setting is 5 minutes. CAUTION Do not set the post purge time to less than 5 minutes. Higher: Increase the time with the d button. The maximum setting is [f/6/0 = 60 minutes or [f/1/d = 24 hours. Settings (continued) 29
30 Operating and error messages Settings menu e [c/\/1 DHW mode status setting. Adjust as follows, or press e: DHW mode can be switched OFF or ON. This setting has priority over other DHW mode settings, such as those made on the room thermostat. Set the DHW mode with the c or d buttons. [c/\/1 means "ON", [c/\/0 means "OFF". NOTE: Setting [c/\/0 also switches OFF the hot water cylinder frost protection. After 5 seconds or after a power interruption the settings menu ends automatically. To end manually press the e button. Any adjustments that you have made have been confirmed. Table 7 Settings (continued) 30
31 Operating and error messages 6.4 Display codes The display shows the condition of the boiler with a code. The table below shows normal operation codes. If a different code shows, please refer to section 6.5, "Identifying and resetting faults" on page 34. Display codes [\/-/\ [-/a/\] dot [-/h/\ Communication test while starting up. Any display code with a dot in the bottom right-hand corner. The boiler is in flue gas test or service mode. The boiler is in heating mode. [-/h/} Any display code with a flashing dot in the bottom right-hand corner. flashing The boiler is in manual operation mode. dot Table 8 Display codes 31
32 Operating and error messages Display codes [=/h/\ [0/a/\ [0/c/\ [0/e/\ [0/h/\ [0/l/\ Table 8 The boiler is in DHW (domestic hot water) mode, or The boiler is in pump run-over time via the external hot water cylinder 130 seconds at the minimum speed. The "Burner" LED (On/Off) is off. Boiler interval circuit. The boiler cannot start-up more than once every 10 minutes. This program is activated if there has been a DHW request from an RC regulator more frequently than once every 10 minutes. The boiler prepares for a burner start-up. There is a current heat demand or a DHW request. The boiler is standby. There is a current heat demand, but too much energy has been supplied. The boiler is standby. There is no current heat demand. Ignition phase. The gas valve is activated. Display codes (continued) 32
33 [0/u/\ [0/y/\ [2/e/\ Operating and error messages Start-up phase. The boiler starts up after activation of the main power supply or completion of a system reset. The flow temperature is higher than set. Fault (subcode [2/0/7 ). The system pressure is too low (less than 3 psi (0.2 bar)). [8/8/8 Display test during start-up phase (max. 1 second). [h/\/7 Display codes The system pressure is too low (less than 12 psi (0.8 bar)). [h/\/7 [p/?/? The system pressure is too low (less than 12 psi (0.8 bar)). The system pressure is too high (higher than 58 psi (4.0 bar)). [\/r/e The boiler is resetting. Table 8 Display codes (continued) 33
34 Operating and error messages 6.5 Identifying and resetting faults If a fault occurs, the error code flashes ON and OFF on the display of the BC10 basic controller. Push the "Reset" button for approx. 5 seconds to reset the fault. The display shows "re" while resetting. Reset is only possible if there is a flashing error message. If the display then shows a normal operation message from tabel 8, this means that the fault has been remedied. If the fault recurs, you must repeat resetting two or three more times. If the fault cannot be reset: Write down the error message and contact your heating equipment service company. Make sure that the heating system is not damaged by frost (see the safety instructions in chapter Shutting down the boiler on page 24). 34
Service Instructions Condensing gas boiler WARNING! Improper installation, adjustment, alteration, service or maintenance can cause injury, loss of life or property damage. Refer to this manual. For assistance
User manual Gas boiler WARNING! If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. B Do not store or use
6 720 804 891 2012/10 EN-US For the installer Operating instructions Sealed combustion boiler Logano GA124 SC If these instructions are not followed exactly, a fire or explosion may be caused with serious
Operating instructions Gas-fired condensing boiler Logano plus GB312 For the user Please read carefully before use 7 747 009 296-01/2007 EN Contents 1 For your safety..............................................
Gas-fired Water boiler Series 2 NOTICE: Series 1/Series 2 identification Read the boiler rating plate to determine the series number. The rating plate is located on the right side of the boiler. User s
FB-USER Rev C User s Information Manual Models:1.5-5.0 WARNING: If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury
Operating instructions For the operator Operating instructions ecotec plus Gas-fired wall-hung high-efficiency boiler GB, IE Publisher/manufacturer Vaillant GmbH Berghauser Str. 40 D-42859 Remscheid Telefon
User s Information Manual CONDENSING GAS BOILER 220/299/300/399 If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage, personal injury or loss
7215 3200-02/2006 GB (EN) For the user Users Manual Gas wall hung Boiler condensing Buderus 500-24/S Please read thoroughly before operating the unit Introduction Please read these instructions and follow
USER S INFORMATION MANUAL Model: HSE 125 N/P, HSE 145 N/P Gas-fired, Condensing Boiler and Instantaneous Water Heater Contents Section Page Major Components... 2 1 About Our Manual... 2 2 Refractory Handling...
prestige User s Information Manual If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. FOR YOUR SAFETY Do
7215 3500-02/2005 GB(EN) For the user Users manual Wall-mounted condensing gas combi boiler Buderus 500-24/C, 500-28/C Please read thoroughly before operating the unit Introduction Please read these instructions
USERS INFORMATION MANUAL FOR GAS FIRED BOILERS CATALOG NO.: 2000.52G Effective: 06-01-00 Replaces: 07-01-94 WARNING: If the information in this manual is not followed exactly, a fire or explosion may result
TM User s Information Manual Commercial Condensing Gas-fired water boilers If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage, personal injury
720 12 481-00.1R oiler Energy Management System FW 200 Operating Instructions for the User 2 US/CA Dear Customer, The controls are the brain of your heating system. We have set it at the factory so that
Operating instructions for system users VIESMANN Heating system with control unit for constant temperature operation VITODENS 100 2/2005 Please keep safe Safety instructions For your safety Please follow
WBII-USER Rev D User s Information Manual Models: 51-211 If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life.
User s Information Manual Gas-fired water boilers Series 4 Featuring Flexibility Series 4 If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage,
TM GOLD CGt Natural gas-fired water boiler with tankless heater User s Information Manual If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage,
USERS GUIDE LOGIC+ Combi 24, 30, 35 When replacing any part on this appliance, use only spare parts that you can be assured conform to the safety and performance specification that we require. Do not use
Combination Boiler and/ or User s Information Manual Water Heater If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss
E-COMBI EVO E-SYSTEM EVO User s manual CONDENSING WALL-HUNG GAS BOILER G.C.N.:47-116-68 (24 kw) G.C.N.:47-116-69 (30 kw) G.C.N.:47-116-70 (38 kw) G.C.N.:41-116-39 (24 kw) G.C.N.:41-116-40 (30 kw) Country
MC Series Gas-Fired Heating Appliance USER S INFORMATION MANUAL MC Series Models MC50 / MC80 MC99 / MC120 NOTICE: HTP reserves the right to make product changes or updates without notice and will not be
WH-USER Rev F User s Information Manual Models: WH 55-399 If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life.
Residential Gas fired Hot Water Boilers User s Information Manual VICTRY VSPH SERIES GAS BILERS Sealed Combustion - Direct Vent Models FR YUR SAFETY: Before operating this boiler, READ this manual. D NT
Model GWC Gas-Fired Water Boilers User s Information Manual If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage, personal injury or loss of
USER MANUAL AND INSTRUCTIONS Riva ADVANCE COMBI WALL HUNG GAS BOILER FOR CENTRAL HEATING SUPPLY Please Read Instructions Carefully Save for Future Reference WARNING: If the information in this manual is
6 720 607 823 GB (06.06) SM Installation and Operating Instructions Gas Instantaneous Water Heater WR10..B... WR11..B... With electronic ignition and triple safety system consisting of ionisation detector,
Combination Boiler and/ or User s Information Manual Water Heater To maintain the safety & longevity of your appliance read and follow the maintenance schedule information throughout this manual. If the
Packaged Gas/Electric Units Owner s Guide to Operating and Maintaining Your Gas/Electric Unit ELECTRICAL SHOCK HAZARD. FIRE OR EXPLOSION HAZARD Disconnect power at fuse box or service panel before performing
Operating instructions for the system user VIESMANN Heating system with control unit for constant temperature or weather-compensated mode VITODENS 100-W 1/2012 Please keep safe. Safety instructions For
GOLD GV Water boiler Series 3 User s information manual If the information in this manual is not followed exactly, a fire or explosion may result, causing property damage, personal injury or loss of life.
User Manual for model RK 18 RK 25 RK 34 Premix condensing boiler User instruction CE 0694 RK 18_25_34 - RAD - ING - MAN.UT - 1104A - DIGITECH 2 - REGNO UNITO - EXTRAHEAT - CBD Technical specification by
Maximiser SE USER S INSTRUCTIONS Natural gas only INSTALLER: TELEPHONE: 705.276A-3233 11-2000 INTRODUCTION It is essential that the instructions in this booklet are strictly followed, for safe and economic
Combination Boiler User s Information Manual Getting Service If your boiler requires service, you have several options for getting service: Contact Technical Support at 1-800-519-8794 or on the website:
95M-200 Gas-Fired Direct Vent Modulating Hot Water Boiler Control Manual And Troubleshooting Guide P/N 24000604, Rev. C [04/09] WARNING! Revise boiler control parameters only if you fully understand the
D2CND024A1AA D2CND024A4AA D2TND012A4AA D2TND018A4AA D2TND024A4AA English Table of Contents Table of Contents 1 Introduction 2 1.1 About the unit... 2 1.2 About the documentation... 2 1.2.1 Meaning of warnings
Indirect Fired Water Heaters Installation and Operating Manual C US Models: SST150-40 SST250-65 SST300-80 SST450-119 CAUTION: The heat transfer medium must be water or other nontoxic fluid having a toxicity
WARNING: Improper installation, setup, modification, operation or maintenance of the heating system can cause personal injury and property damage. Follow each appliances' instructions precisely. For assistance
USER MANUAL AND INSTRUCTIONS Riva FP WALL HUNG GAS BOILER FOR CENTRAL HEATING SUPPLY Please Read Instructions Carefully Save for Future Reference WARNING: If the information in this manual is not followed
Aqua Balance AquaBalance TM CONTROL MODULE QUICK START GUIDE 10 1 Domestic Hot Water temperature setpoint decreasing button 2 Domestic Hot Water temperature setpoint increasing button 3 Central Heating
Operating Instructions Vitodens 200-W, B2HA Series and Vitodens 222-F B2TA Series Models 19 to 150 Wall-mounted, gas-fired condensing boiler For operation with natural gas and liquid propane gas Heating
2003 Lennox Industries Inc. Dallas, Texas, USA 504,809M 03/2009 Supersedes 06/2003 G61MPV SERIES GAS FURNACE Litho U.S.A. FIRE OR EXPLOSION HAZARD. Failure to follow safety warnings exactly could result
Operation Manual NPE Condensing Water Heaters Model NPE-180A NPE-210A NPE-240A NPE-150S NPE-180S NPE-210S NPE-240S Keep this manual near this water heater for future reference whenever maintenance or service
USERS GUIDE 24, 30 For installation guide see reverse of book When replacing any part on this appliance, use only spare parts that you can be assured conform to the safety and performance specification
2011 Lennox Industries Inc. Dallas, Texas, USA 506739 01 06/2011 EL195DFE SERIES GAS FURNACE Litho U.S.A. FIRE OR EXPLOSION HAZARD. Failure to follow safety warnings exactly could result in serious injury,
GB PLEASE LEAVE THIS INSTRUCTION WH THE USER ECOMFORT PLUS 25 HE User instructions All descriptions and illustrations provided in this manual have been carefully prepared but we reserve the right to make
PE MODEL ATER HEATERS SUPPLEMENT TO INSTRUCTION MANUAL P/N 238-44219-00 (Replaces pg. 2 in instruction manual.) CONGRATULATIONS! You have just purchased one of the finest water heaters on the market today!
Bosch Split-Type Ductless Air Conditioner / Heat Pump Climate 5000 AA Series User Manual 2 Bosch Split Type Ductless Air Conditioner / Heat Pump User Manual Data subject to change 01.2017 Bosch Thermotechnology
2010 Lennox Industries Inc. Dallas, Texas, USA 506597 01 11/2010 EL195UH SERIES GAS FURNACE Litho U.S.A. FIRE OR EXPLOSION HAZARD. Failure to follow safety warnings exactly could result in serious injury,
H 2 O Hot Water Storage/ Booster Tanks For Single Tank Installations INSTALLATION, OPERATION & MAINTENANCE MANUAL 30, 40, 60, 80, 115 Gallon L = Low Boy Profile C = Commercial Pipe Connections Conforms
722 7900-0/2004 GB/IR(EN) For trade use Installation and servicing instructions Wall-mounted condensing gas boiler 600-28C Please read thoroughly before installing or servicing The boiler meets the basic
2017 Lennox Industries Inc. Dallas, Texas, USA 506525-01 04/2017 Supersedes 10/2015 ML180UH SERIES GAS FURNACE Improper installation, adjustment, alteration, service or maintenance can cause property damage,
Great Britain EN High-efficiency wall-hung boilers Avanta 24c - 28c - 35c - 39c 18s - 24s - 30s User s Operation Instructions & Important Warranty Information Please keep these instructions in a safe place.
Prestige _TriMaxUser Manual_Qrk8_9225:Prestige User Manual 9/2/ :6 AM Page prestige User s Information Manual WARNING To maintain the safety & longevity of your appliance read and follow the maintenance
GB PLEASE LEAVE THIS INSTRUCTION WITH THE USER Ecomfort 30 HE User instructions CONTENTS OPERATING INSTRUCTIONS FOR THE USER 1.1 INTRODUCTION.................................................................................
INSTALLATION & SERVICE MANUAL ELECTRIC WATER HEATER THE WARRANTY ON THIS WATER HEATER IS IN EFFECT ONLY WHEN THE WATER HEATER IS INSTALLED AND OPERATED IN ACCORDANCE WITH LOCAL CODES AND THESE INSTRUCTIONS.
prestige User s Information Manual WARNING To maintain the safety & longevity of your appliance read and follow the maintenance schedule information throughout this manual. WARNING If the information in
OWNER S MANUAL 14 SEER Single -Package Air Conditioner and Gas Furnace System with R -410A Refrigerant Single Phase 2 to 5 Nominal Tons Three Phase 3 to 5 Nominal Tons PGD4andPGS4SeriesE,WPG4SeriesB Fig.
User s Information Manual CHALLENGER COMBI CC105, CC125, CC125H If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury, or death.
Models: 80-500 Starting Serial #H05H10003637 If the information in this manual is not followed exactly, a fire or explosion may result causing property damage, personal injury or loss of life. This appliance
INSTALLATION, OPERATION AND SERVICE MANUAL GAS COOKER MODEL CPG Page 1 / 18 CHAP 1 - INSTRUCTIONS TO PREVENT ACCIDENTS Keep this manual carefully to be able to refer to it in every case of need. Keep appliance
Applications Manual Gas condensing boiler WARNING! Improper installation, adjustment, alteration, service or maintenance can cause injury, loss of life or property damage. Refer to the installation and
cod. 6272262A GENERAL DATA Heating Data Heat Output Input (Adjustable) (Adjustable) Format 34i 11.2 34KW 45 145MJ/hr Format 34e 11.2 34KW 45 145MJ/hr General Specifications FORMAT 34i 34e Main burner injectors
TROVIS 5600 Automation System TROVIS 5610 Heating and District Heating Controller Mounting and Operating Instructions Electronics from SAMSON EB 5610 EN Firmware version 1.40 Edition December 2014 Controller
MODELS LFP4218/LFP6018 TOP VENT GAS FIREPLACE PFS APPROVED FOR NATURAL GAS OR PROPANE GAS Z21.50-2014 If your plans do not allow for the venting system as outlined previously in the installing chimney/vent
Use & Care Manual With Installation Instructions for the Installer Electric Tankless Water Heaters The purpose of this manual is twofold: one, to provide the installer with the basic directions and recommendations
2015 Lennox Industries Inc. Dallas, Texas, USA 506443-01 01/2015 Supersedes 08/2012 SLP98UH SERIES VARIABLE CAPACITY GAS FURNACE Improper installation, adjustment, alteration, service or maintenance can
Gas-Fired Condensing Boilers A Green Start To Space & Water Heating Residential space and water heating boiler solutions with up to 98.7% efficiency and 57.2 to 151.6 MBH inputs. 1 New! Bosch residential
40MB*D Ducted Style Ductless System Sizes 09 to 48 Owner's Manual TABLE OF CONTENTS PAGE A NOTE ABOUT SAFETY... 2 GENERAL... 2 PARTS LIST... 3 DISPLAY PANELS... 4 FUNCTION BUTTONS... 5 REMOTE CONTROL...
INSTALLATION INSTRUCTIONS Energy Manager Keep these instructions with the boiler at all times for future reference BOYERTOWN FURNACE CO. PO Box 100 BOYERTOWN, PA 19512 1-610-369-1450 www.boyertownfurnace.com
MODULEX EXT GF-143 User Manual OMM-0087_0F USER MANUAL Installation, Operation and Maintenance Natural Gas Modulating & Condensing Modular Hot Water Boiler MODULEX EXT Light Commercial Series Modular Condensing
prestige Control Application Supplement - ACVMax L I S T E D WARNING This document is intended to be used by a factory trained and qualified heating contractor or service technician only. Read all instructions
USER S INFORMATION MANUAL MODELS: All Residential Multi-position Gas Furnaces (33 Models) EFFICIENCY RATING CERTIFIED ISO 9001 Certified Quality Management System CONTACT INFORMATION...............................