2 WELCOME TO Flexible applications - Universal and easy to install in residential or commercial environments. Advanced features - Precision electronics provide premium comfort and temperature accuracy +/- 1 degree F. Simple to use - Set and Forget with an easy to use menus so straightforward no instruction manual is needed. 7 day Programmable with 4 events each day including fan. Technology that works for you - Easy to use, easy to see touchscreen ALL BACKED WITH A 2 YEAR WARRANTY OVER THE COUNTER.
3 MOUNTING THE THERMOSTAT TO THE WALL WIRING TABLE 1. Make sure to turn off the power supply located at the electrical service panel. All heating and cooling units should be OFF. 2. Remove the cover plate by pulling up the cover from the left or right side only. 3. Align the thermostat unit to the wall. 4. Mark the two locations for drilling the 3/16 holes required for the plastic screw anchors. 5. Remove the thermostat and drill the two 3/16 holes in these locations. 6. Insert the plastic gyproc screw anchors and tighten them securely. 7. Make the appropriate wire connections based on the specifications of the household HVAC unit(s). Please refer to Wiring Diagram to determine the appropriate wire connections. 8. Securely mount the thermostat unit to the wall with the two supplied screws. 9. Fit the cover plate back by clipping one side first (left or right) and than push down on the opposite side. 10. Turn on the electricity at the electrical service panel. CONFIGURATION Y1 Y2 W2 OB/W R/C R/H G Cooling Only Air Conditioner Furn. Off AC x x x 2 Air Conditioner Furn. Off AC1 AC2 x x x Heating Only No Compressor Electrical Furn. El.Furn El.Furn2* x x x No Compressor Emg. El. Furn. Emg. El. Furn. El.Furn El.Furn2* x x x No Compressor Gas Gas Gas2* x x x No Compressor Oil Oil Oil2* x x x No Compressor 2 Stage Gas Gas1 Gas2 x x x * if there is another furnace, then connect it to OB/W relay. 1 Stage Cooling, 1 Stage Heating Heat Pump Furn. Off HP OB x x x Air Conditioner Electrical Furn. AC El.Furn x x x Air Conditioner Emg. El. Furn. AC Emg. El. Furn. El.Furn x x x Air Conditioner Gas AC Gas x x x Air Conditioner Oil AC Oil x x x
4 WIRING TABLE WIRING LEGEND CONFIGURATION Y1 Y2 W2 OB/W R/C R/H G 1 Stage Cooling, 2 Stage Heating Air Conditioner 2 Stage Gas AC Gas1 Gas2 x x x Air Conditioner Electrical Furn. AC El.Furn1 El.Furn2 x x x Air Conditioner Emg. El. Furn. AC Emg. El. Furn. El.Furn1 El.Furn2 x x x Air Conditioner Gas AC Gas1 Gas2 x x x Air Conditioner Oil AC Oil1 Oil2 x x x Heat Pump Electrical Furn. HP El.Furn OB x x x Heat Pump Gas HP Gas OB x x x Heat Pump Oil HP Oil OB x x x TERMINAL EQUIPMENT STANDARD COLOR Y1 First Heat Pump & AC Yellow G Fan Green W2 First Stage Furnace White OBW Reverse Valve - Second Stage Furnace Orange RH 24v Red Y2 Second Heat Pump & AC Unknown C Common Blue H Humidity Control Unknown DH Dehumidity Control, Variable Fan Control Unknown RC 24v Unknown 11 & 12 Not Used NOTE: The above colors are standard in HVAC industry. The wiring should be confirmed before installation
5 WIRING DIAGRAM WIRING DIAGRAM ONE AC AC & ONE HEAT Heat (WHT) AC (YLW) AC (YLW) AC2 (YLW) TWO AC AC & TWO HEAT Heat2 Heat1 (WHT) AC1 (YLW) AC (YLW)
6 WIRING DIAGRAM WIRING DIAGRAM ONE HEAT PUMP Reverse Valves (ORG) ONE HEAT PUMP & TWO HEAT Heat 2 Reverse Valves (ORG) Heat 1 (WHT) HP (YLW) HP (YLW) ONE HEAT PUMP & ONE HEAT Reverse Valves (ORG) TWO HEAT PUMP HP 2 Reverse Valves (ORG) Heat (WHT) HP (YLW) HP 1 (YLW)
7 WIRING DIAGRAM WIRING DIAGRAM CUT AC & TWO STAGE FURNACE 2nd Stage Heat 1st Stage Heat (WHT) TWO TRANSFORMERS AC (YLW) COOL TRAN HEAT TRAN ONE TRANSFORMER HEAT TRAN
8 HOME PAGE CONTROL PAGE TO RETURN TO THE HOME PAGE, SIMPLY TOUCH ICON AT ANY TIME! TO ACCESS THE CONTROL PAGE, SIMPLY TOUCH THE HOME PAGE SCREEN ANYWHERE! * 13 1 Room Temperature; to change ºF/ ºC, go to Thermostat Control Mode; to change, go to Temperature Control Mode; to change, go to Fan Operation Mode; to change, go to Fan Operation Indicator; to change, go to Vacation Mode Indicator; to change, go to Security On Indicator; to change, go to Heating set point; to change, go to Cooling set point; to change, go to Date (Month/Day/Year); to change, go to Time; to change, go to Current Room Temperature. 13 Heat and Cool temperature set points; to change, raise or lower set point as desired. In Auto mode touch * Heat/Cool button (Heat or Cool will flash once selected), then raise or lower set points as desired. 14 Temperature Control Mode; select between Heat / Cool / Auto / Emergency Heat. 15 Thermostat Operation Mode: Select between Run Program mode (for details, see 21 ) or Hold Temperature mode. 16 Fan Operation Mode: select between Fan Automaticwhere the fan will turn on only when there is a demand for heating or cooling. Fan Continuously On the fan runs continuously/ Fan Intermittent. In the fan intermittent mode the fan will run for 10 minutes per _ hour which is a convenient way to filter the air and conserve energy. 17 Displays Installer Message; to enter a message, go to Return to Home Page. 19 Access the Menu Page.
9 MENU PAGE MENU PAGE TO ACCESS THE MENU PAGE, SIMPLY TOUCH FROM THE CONTROL PAGE TO ACCESS THE MENU PAGE, SIMPLY TOUCH FROM THE CONTROL PAGE Set Date and Time. 21 Program temperature and fan events by: Select the Day of the week. Select the Event number Select the Start time of the Event Select the desired temperature setpoint Select the next Event number and repeat steps 3 and 4. Once you have set all the events for one day you may copy the same settings to other days of the week. First ensure that your program settings are correct. Then select the next day of the week that you would like to have the same program setting. The thermostat will then prompt you to copy the settings. To activate the program select run program from the control page. 22 Displays system energy consumption and cost: to enter system consumption parameters, go to 29; otherwise, displays fan and compressor runtime. 23 This function allows you to wipe and clean the screen with a dampened cloth with out accidentally changing any of the settings; it place the thermostat screen in a sleep mode for 15 seconds. 24 Vacation settings allows you to set the temperature to a fixed setpoint during the time you are on vacation. Please note that either Heat or Cool must be selected from the control page before entering the Vacation Settings page. To active the feature select Vacation Mode ON- Select the Start Date Select the End Date Adjust the Heat or Cool temperature setpoint. The Vacation Mode begins at 10 PM on the day of your departure and ends at Midnight on the day of your arrival. When the Vacation Mode is active the suitcase icon will appear on the main page. When you return from vacation, you will see a message Vacation Mode Ended displayed on the screen, simply touch the screen to acknowledge the message.
10 MENU PAGE ADVANCED SETTINGS PAGE 1 TO ACCESS THE MENU PAGE, SIMPLY TOUCH FROM THE CONTROL PAGE Displays filter usage in days and resets filter timer. 26 Set Screen Options: Daylight Time (ON/OFF): activate only if you are located in a Daylight Savings Time zone. Reverse: Select between dark background (ON) or light background (OFF) Night Reverse: Select between ON: Automatically reverses screen background for comfortable viewing at night (from 9PM to 6AM) OFF: screen background determined by Reverse function setting. Contrast: set screen contrast from To access Advanced Settings, hold finger 5 seconds on icon. A warning will appear: Caution: Incorrect configuration can damage your system, continue? YES NO 28 Turn Filter Monitor ON or OFF; if ON enter the filter replacement interval. 29 Enter HVAC system consumption parameters rounded off to kw; see 26 (Typically: Fan 1kW; Heat Pump 1kW/ton; Furnace 5-30 kw, 7-9 /kw) 30 Change thermostat temperature display units (ºF or ºC). 31 Turn Security ON or OFF (Default Security PIN = 1111) and select the security level: The security settings allow you to protect your thermostat thermostat from unauthorized use. Turn Security On or Off ( Default pin 1111) You will be prompted to: (first time user) Enter the default PIN Enter your new PIN Re-enter your new PIN There are two modes of password protection: Full Lock and Partial Lock The full lock Function does not allow any changes unless the user enters the PIN Partial Lock allows you to change only the temperature setpoint without entering a PIN. 32 Enter Installer Message (up to 42 characters) to appear at programmable intervals, see 17.
11 ADVANCED SETTINGS PAGE 2 ADVANCED SETTINGS PAGE PLEASE NOTE THAT INADVERTENTLY MODIFYING COMPRESSOR AND FURNACE SETTINGS, MAY SERIOUSLY DEGRADE SYSTEM PERFORMANCE Select system heating and/or cooling equipment: Heat Pump, 2-stage Heat Pump, Air Conditioning, No Compressor see Wiring Diagram. 34 Select the system Furnace Type: Furnace Off (No Furnace), Electric Furnace, Emergency Electrical Furnace (additional electric furnace which will come on in emergency mode in conjunction with electric furnace), Gas Furnace, Oil Furnace, and 2-stage Gas Furnace; see Wiring Diagram. 35 Set maximum compressor cycles per hour. 36 Set Minimum difference between auto mode heat and cool temperature set points. See Set temperature difference between temperature set point and actual temperature reading before 1st stage heating or cooling is initiated. 38 Set temperature difference between 1st stage initiation (37) and 2nd stage heating or cooling initiation. 39 Set temperature difference between 2nd stage initiation (38) and 3rd stage heating or cooling initiation. NOTE: Number of stages depends on your system; see 33 & Reverses the Heat Pump OB Valve contact; (manufacturer dependant)
12 ADVANCED SETTINGS PAGE 4 ADVANCED SETTINGS PAGE Specify X minutes for which stage 1 will function until stage 2 is activated to help raise (or cool) temperature (if the temperature set point is not reached). This function avoids excess compressor wear in the case where the necessary temperature set point is not met (see 37, 38 & 39). Set to 00 to disable. 42 HP ON when Furnace On: Heat Pump and Furnace can operate together when 2nd stage furnace is required. HP OFF when Furnace On: turns off the Heat Pump when the furnace is On (required on some gas or oil furnaces).
13 SIMPLE THERMOSTAT MODE TROUBLESHOOTING THERMOSTAT CAN ALSO FUNCTION AS A NON-PROGRAMABLE THERMOSTAT AFTER IT HAS BEEN CONFIGURED. To enable Simple Mode, press the reset button (take off the thermostat faceplate and press the reset button located in the bottom right-hand corner). The message Touch for Simple Thermostat will appear. Touch the screen, and the thermostat becomes a simplified non-programmable thermostat. * Please note that when changing to Simple Mode, you will not lose any of the settings you have previously entered in the Programmable Mode. Simple Mode has the following basic features: Temperature Control Modes: Fan Operation Modes: * To revert back to the Programmable Thermostat, simply press the reset button and touch the screen when the message Touch for Programmable Thermostat appears. Touch screen buttons do not function properly. Remove cover, press the reset button located in the bottom left corner then accurately touch 3 target centers on the screen when prompted. PARTIAL LOCK and FULL LOCK do not function. You must not touch the screen for 1 minute for the thermostat to automatically lock. I forgot my PIN and cannot unlock the thermostat. Remove the cover plate, press the reset button located in the bottom right corner, as soon as the message touch to reset password appears touch the screen, your PIN will be erased and the thermostat will unlock. Air conditioning turns on in HEAT mode and heating turns on in COOL mode. Reverse the OB valve (see Advanced Settings Page 3). Thermostat appears normal until the screen becomes blank when the compressor or heating system turn on. You need to connect the C wire. 4 wire system will not function unless the heat and compressor contactors can supply enough current to power the thermostat with only 4 wires, if you cannot hook up the C wire another possible solution is to connect two 250 ohm 10 watt resistors in the HVAC room, one between Y and C, and the second one between W2 and C.
14 IMPORTANT NOTICE LIMITED WARRANTY When using this thermostat with a gas furnace a common wire (C) must be connected. When working without a common wire: A confirm in heat mode the cooling does not switch on or B confirm in cooling mode the hear does not switch on If test A or B fail or the thermostat shuts down in either heat or cool mode then it is necessary to connect a common wire, (C), alternatively it may be possible to solve this issue by simply connecting the 250 ohm 10 watt resistor between C and W (in the case of a cooling problem see B) or between C and Y1 (in the case of a heating problem - see A) at the HVAC equipment. When working without a common wire, A confirm that when there is a call for heat, cooling does not also activate, and when there is a call for cool, heating does not also activate. If using the configuration of Heat Pump and Furnace with no Common Wire confirm that when Heat Pump and Furnace are working together (both stages are operating at the same time) that the display does not go blank, if so you must use a Common Wire. This thermostat is equipped to run with two separated power transformers if required RC and RH. Terminals RC and RH are internally connected together however you should wish to use two transformers simply cut with a blade the copper trace on the printed circuit board located between the C and Y2 screw terminals. Hardware Fast Parts Division - International Comfort Products, LLC warrants the original end user ( Customer ) that new FAST HVACR Parts thermostat branded products will be free from defects in workmanship and materials, under normal use, for two (2) years from the original purchase date. Software Fast Parts Division - International Comfort Products, LLC warrants to Customer that the thermostat software will perform in substantial conformance to its program specifications for a period of two (2) years from the date of the original purchase. Exclusions This warranty excludes (1) physical damage to the surface of the product, including cracks or scratches on the touch-screen or outside casing; (2) damage caused by misuse, neglect, improper installation, unauthorized attempts to open, repair, or modify the product, or any other cause beyond the range of intended use; (3) damage caused by accident, fire, power changes, other hazard, or Acts of God; or (4) use of the product with any device if such device causes the problem. Exclusive Remedies Should a covered defect occur during the warranty period and Customer notifies Fast Parts Division - International Comfort Products, LLC, Customer s sole and exclusive remedy will be, at Fast Parts Division - International Comfort Products, LLC s sole option and expense, to repair or replace the product. Replacement products or parts may be new or reconditioned or a comparable version of the defective item. Fast Parts Division - International Comfort Products, LLC warrants any replaced product or part for a period of ninety (90) days from shipment, or through the end of the original warranty, whichever is longer. Obtaining Warranty Service Customer must contact and return product to a local Fast Parts Division - International Comfort Products, LLC product dealer or installer within the applicable warranty period to obtain warranty service. Dated proof of original purchase will be required. Fast Parts Division - International Comfort Products, LLC will not be responsible for Customer s memory data contained in, stored on, or integrated with any products returned to Fast Parts Division - International Comfort Products, LLC for repair, whether under warranty or not. Warranty Exclusive THE FORGOING WARRANTIES AND REMEDIES ARE EXCLUSIVE AND IN LIEU OF ALL OTHER WARRANTIES, EXPRESS OR IMPLIED, INCLUDING WARRANTIES OF MERCHANTABILITY, FITNESS FOR A PARTICULAR PURPOSE, CORRESPONDENCE WITH DESCRIPTION, AND NON-INFRINGEMENT, ALL OF WHICH ARE EXPRESSLY DISCLAIMED BY FAST PARTS DIVISION - INTERNATIONAL COMFORT PRODUCTS, LLC AND ITS SUPPLIERS. Disclaimer NEITHER FAST PARTS DIVISION - INTERNATIONAL COMFORT PRODUCTS, LLC NOR ITS SUPPLIERS SHALL BE LIABLE FOR INCI- DENTAL, CONSEQUENTIAL, INDIRECT, SPECIAL, OR PUNITIVE DAMAGES OF ANY KIND, OR FINANCIAL LOSS ARISING OUT OF OR IN CONNECTION WITH THE SALE OR USE OF THIS PRODUCT, WHETHER BASED IN CONTRACT, TORT (INCLUDING NEGLIGENCE) OR ANY OTHER THEORY, EVEN IF FAST PARTS DIVISION - INTERNATIONAL COMFORT PRODUCTS, LLC HAS BEEN ADVISED OF THE POSSIBILITY OF SUCH DAMAGES. FAST PARTS DIVISION - INTERNATIONAL COMFORT PRODUCTS, LLC S ENTIRE LIABILITY SHALL BE LIMITED TO REPLACEMENT OR REPAIR OF THE PRODUCT.
15 FAST PARTS DIVISION - INTERNATIONAL COMFORT PRODUCTS, LLC Technical Support: Physical Dimensions Case: 5.75 x 4.75 x 1.25 (145mm x 120mm x 30mm) Display: x (95mm x 55mm) Electrical Rating 24 volt AC/DC Class 2 maximum 4 amps Temperature Accuracy +/-1 F degree Power failure protection safeguards clock and memory. FCC Statement THIS DEVICE COMPLIES WITH PART 15 OF THE FCC RULES. OPERATION IS SUBJECT TO THE FOLLOWING TWO CONDITIONS: (1) THIS DEVICE MAY NOT CAUSE HARMFUL INTERFERENCE, AND (2) THIS DEVICE MUST ACCEPT ANY INTERFERENCE RECEIVED, INCLUDING INTERFERENCE THAT MAY CAUSE UNDESIRED OPERATION. US PATENT 6,786,421 OTHER PATENTS PENDING
2-YEAR WARRANTY Climatouch CT0-7TC-32H 3 Heating and 2 Cooling with Humidistat www.climatouch.com OUTDOOR WIRELESS TEMPERATURE TRANSMITTER AND RECEIVER KIT Climatouch Part No. 90064 Accurately Displays
MODEL Premier Series 3000 USER MANUAL Non-Programmable Single Stage Heat/Cool Digital Thermostat Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single
1 Specifications Premier Series Non-Programmable Thermostats MODEL 3000 MODEL 3200 1 2 3 4 5 Specifications Installation Testing Your New Thermostat Programming User Settings Temperature Adjustment WARNING
Model 8800 Universal Communicating Thermostat Owner s Manual Includes Operating Instructions and Warranty Information READ AND SAVE THESE INSTRUCTIONS 61000762A 8800 Tstat Owners.indd 1 3/28/11 4:19:57
3100 Premier Series Non-Programmable 2 Heat / 2Cool & Heat / Cool Digital Thermostat OWNERS MANUAL Compatible with low voltage multi-stage heat / cool systems with up to two stages of heating and two stages
1 Specifications cont. Premier Series Universal Auto Changeover Up to 3 Heat / 2 Cool Heat Pump or 2 Heat / 2 Cool Conventional Thermostat Installer Guide Before Installing, Programming or Operating, PLEASE
3000 Premier Series Non-Programmable Single Stage /Cool Digital Thermostat OWNERS MANUAL Compatible with low voltage single stage gas, oil or electric heating or cooling systems, including single stage
www.klimaireintl.com Small Digital Thermostat Controller Temperature Control Small-Fiac IOM Manual KLIMAIRE International +1.647. 477. 3333 +1.646. 808. 0240 firstname.lastname@example.org Digital Thermostat
INSTALLER S & OWNER S MANUAL HVAC INSTALLER: PLEASE LEAVE MANUAL FOR HOMEOWNER Part No. 4028539 Dehumidifier & Ventilation System Controller 4201 Lien Rd Madison, WI 53704 TOLL-FREE 1-800-533-7533 www.thermastor.com
OWNER'S MANUAL P/N P374-1100FM 1 For All Programmable Digital Thermostat 72 74 Am I2:00 AUTO 70 unts Flush to the Wall 7 Day Programmable 4 Time Periods per Day Auto Changeover Large, Easy To Read Display
INSTALLER S & OWNER S MANUAL HVAC INSTALLER: PLEASE LEAVE MANUAL FOR HOMEOWNER DEH 3000R Part No. 4028407 Dehumidifier & Ventilation System Controller 4201 Lien Road, Madison, WI 53704 TOLL-FREE (800)-533-7533
Installation Manual 000 Version.0 EXP-000 HBX Control s Inc. Control s Inc. HBX EXP 000 Version.0 HBX EXP-000 EXPANSION MODULE INTRODUCTION The EXP-000 is designed to be integrated with the HBX CPU-000
OWNER'S MANUAL MODEL P474-0140 Non-Programmable Digital Thermostat HEAT PUMP THERMOSTAT 2 HEAT, 1 COOL emergency aux. heat normal energy save Fan On Fan Auto Millivolt Compatible Battery or System Powered
Digital Thermostat residential THERMOSTAT T1050 5+2 Day PROGRAMMABLE up to 2-heat & 2-cool PUMP Control up to 2 heat & 2 Cool Stages 4 Settings Per Day Self-prompting programming Auto changeover Separate
GG-2 2-CHANNEL GAS DETECTION CONTROL PANEL Installation and Operation Manual 2 GG-2 Warning Use this product only in the manner described in this manual. If the equipment is used in a manner not specified
OWNER'S MANUAL P/N P474-2150 1 For All Programmable Digital Thermostat Mo TOTALINE 72 74 COOL AUTO HEAT 70 Optional Locking Cover Meets California Title 24 Dual Setpoint 5+1+1 Day Programmable 3 Occupied,
Programmable 5-2 Day Digital Thermostat 1 STAGE HEAT COOL THERMOSTAT TOTALINE 72 72 prog run off set Tu Heat I2:00 next SINGLE STAGE HEAT PUMP COMPATIBLE (Does not control auxiliary heat) Separate programs
Model 8476 Thermostat with Event-Based Air Cleaning Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS Table of contents Installation Installation location recommendations... 3 Outdoor
5100 Premier Series 7-Day Programmable 2-Heat / 2-Cool Heat /Cool Digital Thermostat OWNERS MANUAL Compatible with low voltage multi-stage heat / cool systems with up to two stages of heating and two stages
ENTOUCH ONE USER GUIDE v4.0 MEASURE. MANAGE. SAVE. Contents Getting Started 3 Installation 7 Using the Setup Wizard 11 Using the Home Screen 12 Using the Main Menu 16 The Setup Menu 19 Using the Web Management
OWNER'S MANUAL P/N P374-2300FM 1 For All Programmable Digital Thermostat Am OFF OVERRIDE Meets California Title 24 unts flush to the wall 7 Day Programmable 3 Occupied, 1 Unoccupied Auto-Changeover Large,
Optima ZigBee Thermostat Quick Start Guide For other language versions, please visit: www.salusinc.com LET S GET STARTED Make sure you have the following items: Thermostat with Mounting Plate Trim Plate
Owner s Manual Model CX-MPC IMPORTANT SAFETY INFORMATION: Always read this manual first before attempting to install or use this device. For your safety, always comply with all warnings and safety instructions
VENSTAR FAN COIL THERMOSTAT FAN COIL THERMOSTAT T1070 NON- PROGRAMMABLE 2 OR 4 PIPE SYSTEMS Remote sensor ready 3 speed fan control Self-prompting adjustment Auto 2-pipe changeover when used with ACC-SENFC
SC 3006 Auto Changeover 7-Day Programmable Hardwired Programmable Electronic Thermostat 7-Day Programmable Single Stage Heat Pump/Non-Heat Pump Systems Backlit Display Single Stage Heat/Cool Systems Field
Owner s Manual PIR-1 IR Learner PIR-1 Owner s Manual 2010-2013 Universal Remote Control, Inc. The information in this owner s manual is copyright protected. No part of this manual may be copied or reproduced
Model 8800 Universal Communicating Thermostat Safety & Installation Instructions READ AND SAVE THESE INSTRUCTIONS Table of contents Installation Installation location recommendations... 2 Thermostat mounting...
Comfort System T-21-P Touchscreen Thermostat Installation Manual Version 1.40 INTRODUCTION The Comfort System T-21-P is a feature-rich touchscreen thermostat that can be battery powered or hardwired to
USERS INFORMATION MANUAL Heating & Cooling Systems L TSTATBBPB101 PROGRAMMABLE DIGITAL THERMOSTAT NOTE TO INSTALLER: This manual must be left with the equipment user. AUTO Heat Pump & Heat Cool Dual Setpoint
Installation Instructions TSTATCCPQ501 TSTATBBPQ501 P474-1035 Digital Thermostat NOTE: Read the entire instruciton manual before starting the installation. Tu AM SET I2:00 HEAT & COOL 5+2 DAY PROGRAMMABLE
Digital Thermostat residential THERMOSTAT T1 900 7-DAY MABLE up to 3-heat & 2-cool HEAT COOL HEAT PUMP with HUMIDITY CONTROL Control up to 3 Heat & 2 Cool Stages 3 Configurable Outputs Adjustable 2nd &
Operation 8085C MENU PROGRAM RESET ENGLISH MENU PROGRAM RESET Customer Support: 888-515-2585 or Visit our webiste www.ritetemp-thermostats.com Printed in China 1-402-006 Operation 8085C PG 1 Day Indoor
M3375 Home and Building Control Home and Building Control Helping You Control Your World Honeywell Inc. Honeywell Limited/Honeywell Limitée 1985 Douglas Drive No. 740 Ellesmere Road Golden Valley, MN 55422
Projection Alarm Clock USER GUIDE Jazwares, Inc. 2012 CONTENTS Please read the instructions along with the Alarm Clock carefully before you use it, so that you can operate it conveniently. WELCOME, Warnings
PRACTICAL USER S GUIDE FOR THE DIMPLEX PURIFIRE ELECTRIC STOVE Serial Number Quality checked by: Model Number CAT Number Valued Customer, We are pleased that you have chosen to purchase an electric fireplace
Protégé Eclipse LED Keypad User Manual PRT-KLES The specifications and descriptions of products and services contained in this manual were correct at the time of printing. Integrated Control Technology
OWNER'S MANUAL P/N P374-2200 Installation Instructions 70 AUTO TOTALINE 72 COOL o HEAT o 69 Meets California Title 24 Use with most Air Conditioning & Heating Systems including: 1 or 2 Stage * Electric
Carrier Heating & Cooling TSTATCCNB00 NON-PROGRAMMABLE DIGITAL THERMOSTAT USER INFORMATION MANUAL FOR THE OPERATION AND MAINTENANCE OF YOUR NEW THERMOSTAT NON-PROGRAMMABLE DIGITAL THERMOSTAT AUTO 74 Dual
MagicStat CT3300 Programmable Thermostat Installation and Programming Instructions Weekday/Weekend (5-day/2-day) Programmable Heat and/or Cool Low Voltage (20 to 30 Vac) Thermostat and Mounting Plate Model
9720 DELUXE PROGRAMMABLE THERMOSTAT INTEGRATED COMFORT SOLUTIONS H HEAT PUMP 7 Day Programmable 3 Heat / 2 Cool User s Manual Quick Start Installation and Programming 110-662 W A R R T A N Y PRODUCT FEATURES
Master Catalog 125 Temperature Controls Section A Product/Technical Bulletin Issue Date 1098 MR4PMUHV Electronic Temperature/Defrost Control with Relay Pack The MR series temperature controls are designed
PRACTICAL USER S GUIDE FOR THE ELECTRIC STOVE MODEL NUMBERS: 23 Electric Stove Quality checked by: Valued Customer, We are pleased that you have chosen to purchase an electric stove manufactured by Dimplex
OPTIMA ZigBee Thermostat For other language versions, please visit: www.salusinc.com ii Salus SAFETY INSTRUCTIONS Please read these instructions carefully before installing and using the OPTIMA thermostat,
INSTALLATION MANUAL This manual covers TopTech models: TT-S-755H Thermostat Applications Guide Description Gas or Oil Heat Electric Furnace Heat Pump (No Aux. or Emergency Heat) Heat Pump (with Aux. or
Heating/Cooling Thermostat and Subbase Package T8196A/Q682A OWNER'S MANUAL M3375 Congratulations on your purchase of a Honeywell energy saving thermostat. The Honeywell name is your assurance of accurate
Digital Thermostat residential THERMOSTAT T0140 NON- PROGRAMMABLE up to 2-heat & 1-cool PUMP Stages: 2-Heat, 1-Cool Battery or System Powered Auxiliary Heat Indicator Fahrenheit or Celsius Bi-Color LED
Facilities Planning & Management ComfortNet CTK03 Thermostat Instructions Millbrook Apartments #4 Application These residential units are furnished with new high efficiency HVAC units. These are designed
Automatic Phone-Out Home Monitoring Systems Power Outage, Freeze and Flood Alarm Product Description Model Number: THP201 These monitoring systems are intended to monitor homes, cabins, and other premises
Proliphix Thermostat Installation Guide Release 2.0 July 2006 Beta Draft Confidential Technical Support When contacting Proliphix for technical assistance, please have the following information available:
PSP721U SMART TEMP UNIVERSAL PROGRAMMABLE THERMOSTAT FOR BOTH CONVENTIONAL AND HEAT PUMP SYSTEMS INSTALLATION AND OPERATING INSTRUCTIONS 52033 IMPORTANT! Please read all instructions carefully before beginning
ADC-T2000 ADC-T2000 Smart Thermostat User Product Guide Manual 170308 v1.5 Smart Thermostat Product Manual 1 Before installing or servicing the thermostat, turn off power to the system at the circuit breaker.
CT2700 An Electronic Round Programmable Thermostat USER S GUIDE MERCURY SWITCH TYPICAL LOCATION OF A MERCURY SWITCH IN A THERMOSTAT M064 RECYCLING THERMOSTAT If this thermostat is replacing a control that
IT801 Thermostat User s Manual The complete guide to the set up and operation of your new smart Wi-Fi thermostat. The smart Wi-Fi thermostat system learns your comfort preferences, then finds opportunities
Users Manual LAURUS Systems, Inc. - Ph: 410-465-5558 - Fax: 410-465-5257 - www.laurussystems.com Introduction The rad-d is a security and inspection system that detects emissions from radioactive material.
OWNERS MANUAL CARBON MONOXIDE DETECTOR MODELS Panel Mount & Remote Detectors (R) (353-101 and 353-201) 353 FAMILY MODEL OWNERS/INSTALLATION MANUAL Page 1 of 22 LOG OF REVISIONS REV NO. PAGE NO. DATE DESCRIPTION
User Manual Touchscreen Programmable Touchscreen Thermostats 6100 6300 6400 For 1 Heat / 1 Cool Systems For Systems Up to 4 Heat / 2 Cool For Systems Up to 4 Heat / 2 Cool with Humidification Control Read
519_D Radiant Thermostat 519 03/13 Zoning Replaces: New Installation & Operation Manual Introduction The Radiant Thermostat 519 accurately controls the room and/or floor temperature for a hydronic heating
Model: SFE-ST BUILDER BOX INSTALLER/CONSUMER SAFETY INFORMATION PLEASE READ THIS MANUAL BEFORE INSTALLING AND USING APPLIANCE. WARNING! IF THE INFORMATION IN THIS MANUAL IS NOT FOLLOWED EXACTLY, AN ELECTRICAL
Peak Partners Web-Programmable Thermostat Homeowner s Manual Look inside for a complete guide to the setup and operation of your new thermostat. Table of Contents Step 1: Getting Started...4-6 A. Thermostat
LIMITED WARRANTY Limited Warranty: Subject to the limitations set forth below, THYSSENKRUPP ACCESS, 4001 East 138th Street, Grandview, Missouri 64030, warrants to the ORIGINAL PURCHASER ONLY that the Volant
PRACTICAL USER S GUIDE FOR THE CORNER WALL MOUNTED ELECTRIC FIREPLACE MODEL NUMBER: EWMC-CC-SS Quality checked by: Valued Customer, We are pleased that you have chosen to purchase an electric fireplace
ACONT600AF11MA/ACONT602AF22MA Programmable Comfort Control OWNER S GUIDE M28617 Pub. No. 12-5039-03 69-1831-04 Quick Reference Card Grasp and pull to see basic operating instructions at a glance. Battery
Weekday, Saturday and Sunday Programmable Heat and/or Cool Low Voltage (20 to 30 Vac) Thermostat and Wallplate Model CT3550 Honeywell CT3550 PROGRAMMABLE THERMOSTAT OWNER S GUIDE Para pedir estas instrucciones
Single-Stage Thermostat Set-Up Guidelines for All-Electric Heat Pumps: Supplement to ecobee 3 Installation Materials from the North Carolina Electric Cooperatives The following Advanced Energy recommendations
INSTALLATION AND USER INSTRUCTION GUIDE Electric Fire With Remote Control Model: WM-3522CF Please read all instructions carefully and retain for future reference IMPORTANT: THESE INSTRUCTIONS SHOULD BE