1 SCR100 User Manual Version:1.1 Date:Dec 2009 Introduction: This document mainly introduces the installations and connections of SCR100 products, and the brief operations about attendance software.
2 Important Claim Firstly thank you for purchasing our products. Before use, please read this manual carefully to avoid the unnecessary damage! The company reminds you that the proper user will improve the use affect and authentication speed. No written consent by our company, any unit or individual isn t allowed to excerpt, copy the content of this manual in part or in full, also spread in any form. The product described in the manual maybe includes the software which copyrights are shared by the licensors including ZKSoftware Inc. Except for the permission of the relevant holder, any person can t copy, distribute, revise, modify, extract, decompile, disassemble, decrypt, reverse engineering, leasing, transfer, sub-license the software, other acts of copyright infringement, but the limitations applied to the law is excluded. Due to the constant renewal of products, the company can not undertake the actual product in consistence with the information in the document, also any dispute caused by the difference between the actual technical parameters and the information in this document. Please forgive any change without notice.
3 1. Must Know 1.1 Product Profile SCR100 released by our company is the World s first access controller and reader based on TCP/IP, professional access control machine with RF card but no screen and no press-key. These access control product series added with RF card provide a more product choices for system access control solutions. It can be used as a separate control locks, also can be used as an access controller connecting RF cards, to realized master-slave machine or anti-pass back function. Standard TCP/IP protocol can realize connection and networking crossover network and gateway. It can be embedded with Webserver to visit query records and so on via Internet. 1.2 Front View LED indicator 1. When the device is in verifying status, LED indicator light is blue and flashes once per 2 seconds. When the device is in enrollment and deletion status, LED indicator light is off. 2. If a successful verification, enrollment or deletion, LED indicator light is green and constant on for 1 second. If a failed verification, enrollment or deletion, LED indicator light is red and constant on for 1 second.
4 3. When the door is opened normally, if the device detects the door is not closed well after the time of door sensor delay time (which can be set by the suited access control software), the buzzer will long ring, if device detects the door is still not closed well after a minute long ring, the device will issue the alarm signal. Note:If the prompts of both device s LED indicator light and buzzer are different from the above, please contact the relevant technicians. 1.3 Installation Precautions Although our products are manufactured in accordance with the stringent manufacturing and inspection standards specified by China, USA and EU, we still recommend you to read the Installation Precautions carefully before installation. We recommend you to use this product properly so as to greatly improve the recognition performance and speed. Failure to read the Installation Precautions carefully before installation may result in serious accidental damage to the product due to improper installation. Therefore, to avoid unnecessary equipment damage, please do read the Installation precautions carefully before installation. 1. Ensure the power system is switched off prior to installation because live-line operation is quite hazardous and may result in the damage of the equipment and even core components due to power cable contact. 2. The stripped (naked) ends of all wiring terminals shall not be in excess of 5 mm to avoid equipment damage due to accidental contact with the naked ends. Furthermore, connection cables in
5 different colors must be adopted. 3. Connect the grounding cable first in places with large static electricity or in winter before connecting other cables to avoid equipment damage due to instant excessive static electricity. 4. Connect power cables only after connecting all the other cables. If the product cannot operate properly, please perform necessary inspection after cutting off the main power supply. Do keep in mind that all live-line operations may result in accidental equipment damage and our warranty does not cover any equipment damage arising out of such operations. 5. Only test the exit switch only when you have assigned other personnel outside of the door after the installation because you may be unable to exit the door due to accidental problems. 6. Our equipment provides a self-test function for you to perform self-test after installation to confirm whether the installation is complete. 7. It is recommended to adopt the 12V DC power supply with current larger than 3A. It is recommended to use 12V DC electronic locks with current less than 1.5A. Consult related technical personnel if the power parameters of the locks exceed the specified range. The current of the power supply shall be at least 1A larger than that of the electronic locks. Failure to meet the above power supply requirement may possibly lead to electronic lock drive failure or even equipment damage. 8. Before connecting cables for equipment, please read and follow the instructions in the Installation Guide. The burnout of core boards due to improper cable connection and equipment start failure due to fingerprint sensor burnout both fall beyond our warranty scope.
6 9. If the distance between the power supply and equipment is large, do not replace power cables with network cables or other types of cables. When selecting power cables, take into account the voltage attenuation caused by long transmission distance. 10. When adopting the RS485 networking mode, use dedicated RS485 cables and active RS232/485 converter, and distribute cables by adopting the bus structure. If the RS485 communication distance is over 100m, the RS485 bus must be terminated using termination resistors with impedance of about 120Ω at both ends of the network. For matters not mentioned herein, see User Manual, Software Instructions and Appendix.
7 1.4 Schematic Diagram for System Installation
8 1.5 Schematic Diagram for Communication Connections 1. The device directly connects with the computer. PC TCP/IP or RS232 SCR The device connects to the computer over an RS485 network. RS485 bus PC RS232 RS485 converter 3. The device connects to the computer over an Ethernet. Switch PC TCP/IP TCP/IP TCP/IP
9 2. Installation 2.1 Fix the plate 1) Post the mounting template on 2) Take off the water-proof cushion the wall. Drill holes according to the marks on the template.(holes for screw and wiring) 3) Take away the screw on the 4) Release the mounting plate bottom of device 5) Fix the cushion and plate on the wall
10 2.2 Connecting Peripherals Ensure the power supply is cut off before cable connection. Live-line cable connection may result in serious damage to the equipment. Connect the following peripherals in the sequence presented below: 1) Door sensor cables (Sensor, GND) 2) Exit switch cables (Button, GND) 3) Alarm cables (Alarm+, Alarm-) 4) Electronic lock cables (NC, COM, NO) 5) Ethernet cables (RJ45-1, RJ45-2, RJ45-3, RJ45-4) 6) RS232 cables (232RX, 232TX, GND) 7) RS485 cables (485A, 485B) 8) Wiegand output cables (WD0, WD1, GND) 9) Wired door bell (Bell+, Bell-) 10) Power cables (GND, +12V)
11 2.2.1 Door Sensor Cables The door sensor is used to sense the door open/close status. The device generates an alarm when sensing that there is an unauthorized entry or the door is not closed within the specified time through the door sensor.
12 2.2.2 Exit Switch Cables The exit switch is a door access device installed inside the room. To open the door, press the pushbutton exit switch. The exit switch is installed about 1400 mm above the floor. Ensure the exit switch is well aligned without skew and cables are properly connected and fastened. (Cut the naked ends of unused cables and wrap them with insulating tape) Take measures against the electromagnetic interference (EMI). (For example, lighting switches and computers) Alarm Cables The alarm output of access control machine is a switch signal,it can be connected to the circuit of simple alarm in serial, it can also be used as a signal to trigger the advanced alarm/monitor system. (This alarm output can only support 12VDC alarm)
13 2.2.4 Electronic Lock Cables The installations of the door locks are subject to the types of locks used. When selecting the power cables of an electronic lock, you need to take into account the internal resistance on the transmission lines. Ensure the electronic lock is securely fastened and cables are properly connected. For electric bolt locks and electromagnetic locks, do not reverse the positive (+) and negative (-) terminals. Cut the naked ends of unused cables on locks and wrap them separately with insulating tape. The operation latency of an electric bolt lock can be adjusted as required. The device supports the NO and NC electronic locks concurrently as long as they are connected to different terminals. NC: The circuit-breaker is closed in normal conditions. When the device is opened by force, the circuit is opened, thus resulting in the status change. NO: The circuit-breaker is opened in normal conditions. When the device is closed by force, the circuit is closed, thus resulting in the status change. Power Ground (GND): Power loop grounding wire connector. In practice, various types of electronic locks are in use, and therefore the proper cable connection methods must be subject to the lock specifications. Note: The door lock is controlled by a lock relay. When installing a lock, you need to take into account two factors: safety and security, that is, what do you expect from a door during a power outage? To keep Safety During Power Outage or Security During Power Outage? Safety During Power Outage : In the event of a power outage (possibly because of the cutting-off of the power supply or the controller
14 failure), the door is automatically opened for free entry and exit and only locked after the power returns. Such a type of door ensures access to the protected areas in the event of emergencies. A typical application of this mechanism is the use of electromagnetic locks. The locks can only be opened when the power supply is normal. Security During Power Outage : Doors adopting this mechanism ensure the protected areas are still under protection at all events. A typical application of this mechanism is the use of electronic locks which can only be opened from within in the event of a power outage. You can decide the power supply mode when installing locks based on the following calculation: The operating voltage of the device is 12V. In the following expressions, I is defined as the current input by the power supply; ULock is defined as the operating voltage of the lock; ILock is defined as the operating current of the lock. 1. The device shares power supply with the electronic lock, as shown in Figure 1 and Figure 2: 1) ULock=12V, I-ILock>1A; 2) The distance between the electronic lock and the device is short. 2. The device and the electronic lock adopt separate power supply, as shown in Figure 3 and Figure 4: 1) ULock=12V, I-ILock 1A; 2) ULock 12V; 3) The distance between the electronic lock and the device is long.
15 Figure 1 NC electronic lock (sharing power supply with the device) Figure 2 NO electronic lock (sharing power supply with the device)
16 Figure 3 NC electronic lock (adopting an independent power supply) Figure 4 NO electronic lock (adopting an independent power supply) Note: To prevent the self-induced Electromotive Force (EMF) generated when an electronic lock is opened/closed from impacting the access control system, connect in parallel a diode FR107 (do not reverse the
17 positive (+) and negative (-) terminals) on the electronic lock to discharge the self-induced EMF when connecting cables for the access control system on site Ethernet Cables The background PC software can communicate with the device, upload and download data and perform remote management of the terminal over TCP/IP. The device can connect with Ethernet in the following two ways: 1) The device connects with a computer through a crossover cable. IP: Subnet mask: PC 2) The device and computers form a Local Area Network (LAN) through network cables and a hub. PC Switch
18 2.2.6 RS232 Cables The background software can communicate with the device through RS232 to upload and download data. Definition for connections between PC and device PC Serial Port RXD TXD GND Device Serial Port TXD RXD GND Schematic diagram of cable connection PC Serial port
19 2.2.7 RS485 Cables Cables must be distributed by adopting the bus structure in RS485 networking mode. The RS485 communication cable consists of a shielded twisted pair. The RS485 transfers signals through the voltage difference between two communication cables. The differential-mode interference will be generated between two signal cables during signal transfer. A bias resistor (termination resistor) can be added in the circuit to eliminate the differential-mode interference. Generally the termination resistor is not required. The RS485 bus must be terminated using termination resistors with impedance of about 120Ω at both ends of the network only when the RS485 communication distance is over 100m. Definition of terminal connection Number of Terminals Function 485+ RS-485 communication RS-485 communication - RS485Bus PC PC RS232 RS485 Converter
20 2.2.8 Wiegand Output Cables The device provides standard Wiegand26 output. It can connect to a majority of access controllers, just like connecting an IC card reader or an encryption keyboard. It is recommended that the cable between the device and controller is not over 90m in length. (The wiegand signal extender can be adopted in cases where long transmission distance is required or the interference nearby is quite strong.) Note: 1) The device and the access controller or card reader must share a common ground regardless of whether they share the power supply or not, so as to ensure Wiegand signal stability. 2) If Wiegand output or RS485 communication distance is over 90m, it is recommended to adopt shielded cables and connect them to the SGND terminal to avoid interference caused by long-distance transmission.
21 2.2.9 Power Cables The operating voltage of the device is 12V DC, the operating current is about 500mA, and the standby current is about 50mA. Connect the device to the power supply through the power wiring terminals. You can also adopt the standard delivery-attached power adapter, with connection methods shown in the following two figures. 1. Connect the positive (+) and negative (-) terminals of power supply directly to +12V and GND. (Do not reverse the positive (+) and negative (-) terminals) 2. Insert the plug of the 12V power adapter into the power socket. 2PIN Power Socket
22 2.3 Fastening the Device 1) Ensure all cables are properly connected. 2) Attach the device to the rear wall-mount plate (From the top down) to place it flat against the wall-mount plate, as shown in Figure 1. 3) Fasten the device to the rear wall-mount plate by using a screw, as shown in Figure 2. 4) Ensure the device is securely fastened after installation. Figure 1 Figure Inspection after Installation After the whole system installation is complete, check whether the system is properly installed prior to power-on. Check whether the lock drive and other devices operate properly. The green indicator will start blinking upon power-on.
23 4. Others 4.1 Reset Button If the device cannot operate properly due to misoperation or other faults, you can reset it by pressing the Reset button. 1 Find a tool with a sharp end and with diameter less than 2 mm. 2 Locate the Reset sign beside a small hole at one side of the device. 3 Insert the tool into the small hole and press it in the direction as shown in the following figure to reset the device. RESET button Bottom View
24 4.2 Tamper Switch A tamper switch is located in the middle of the rear of the device and covered with the rear cover plate to prevent tampering. When dismantled, the device will generate an alarm through the terminal. Tamper Switch Back View
Installation Guide & User Manual Standalone Metal RFID Series Version: 2.1 Date: January, 2015 Important Note Document Privacy Note: Firstly thank you for purchasing the product. Before use, please read
InBio X60 Series Access Control Panel User Manual Version: 1.4 Date: Nov., 2015 About This Manual This manual introduces the installation connection and user manual of the InBio X60 Series Access Control
UNC100 Integra Manual New Generation Building Security July 30, 2014 V1.2 Copyright Notice Copyright 1995-2014 by All rights reserved Worldwide. Printed in Canada. This publication has been provided pursuant
Controllers Centralization of Access Control Devices Made Easy Installer Guide CONTENTS 1 INTRODUCTION 3 The Overview of Hardware 5 The Overview of Installation & Communications 7 Installations with door
HRX 5000 Technical Manual Version 1.2 Contents: Specification...2 Connectors...5 RS-485 Network Connectors (J6 and J7)...5 RS-232 to Printer (J19)...6 RS-232 to PC (J8)...7 TCP/IP...8 Power (J21)...9 Fire
User Manual X8s Access Control System Version: 1.0 I 1. Equipment Installation (1) Remove the screw from the bottom of the device. (2) Remove the back cover of the device. (3) Fix the back cover on the
Grandstream Networks, Inc. Table of Contents INTRODUCTION... 4 GDS3710 WIRING CONNECTION... 5 Powering and Connecting the GDS3710... 5 Power and Data PINs... 5 Alarm In and Alarm Out PINs... 6 DETECT AND
GSM RFID VOICE Alarm System User s Manual For a better understanding of this product, please read this user manual thoroughly before using it. CONTENTS [Function Instruction] [Control Panel] Control Panel
Grandstream Networks, Inc. Table of Contents INTRODUCTION... 4 GDS3710 WIRING CONNECTION... 5 Powering GDS3710... 5 Power and Data PINs... 5 Connecting Alarm IN and Alarm OUT PINs... 6 Alarm IN Connection
RC801/803/805-480B 16E1 Fiber-Optic Multiplexer (Rev. M) User Manual Raisecom Technology Co., Ltd. (04/2005) 1. Cautions Please read the following notices carefully before installing and using the device,
XP2M Networked Access Control Panel V1.0X Installation Guide X P 2 M A C C E S S C O N T R O L S Y S T E M Installation Guide Document Ref: PLAN XP2M Installation Guide V4(G)2010 Access Control Services
MOBILE CALL GSM Alarm System User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. Contents Function Introduction (3) Alarm Host Diagram
Centaur TM II Cube Slave Alarm Signalling Equipment INSTALLATION GUIDE General Description This guide provides a summary for installing and configuring the Centaur TM Cube Slave Alarm Signalling Equipment
RMS/RPX Reader User Manual Copyright Disclaimer Trademarks and patents Intended use FCC compliance Copyright 2005, GE Security Inc. All rights reserved. This document may not be copied or otherwise reproduced,
Operating & Maintenance Manual Alert-4 Ethernet LCD Master Alarm w w w. a m i c o. c o m Contents User Responsibility 4 Introduction 4 Features 5 Description of the Alarm 5 Shipment Details 5 The Alarm
R A D I O N I C S READYKEY K2015A Alarm Event Manager Installation Data Sheet READER CONTROLLER INPUTS INPUTS RLY 8 RLY 7 RLY 6 RLY 5 RLY 4 RLY 3 RLY 2 RLY 1 8 Supervised Inputs (Normally Open or Normally
Intelligent GSM Auto-Dial Alarm System User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. Contents Function Introduction (3) Alarm
BS-316 Gas detection control panel up to 16 inputs Installation operation manual Page 1 from 21 Contents 1 Operation instructions--------------------------------------------------------------------------------------------------------------------3
A SAFE ENVIRONMENT THROUGH SECURED ACCESS TAKE TOTAL CONTROL OF - WITH HIKVISION When you re installing Access Control systems, there s a lot on your mind and there s a lot riding on your product decisions.
RFID Card Access Control Unit Operating Instructions 1 1. Product Specification Item Index Operating Voltage 12VDC+10%; Current 1.2A Lock Relay 12VDC/2A Environmental temperature working:0 C~45 C; storage:-10
FEC400 Series Conventional microprocessor controlled fire detection and alarm panels with extinguishing control Installation Manual Version 2.3 / August 2004 Aritech is a GE Interlogix brand. http://www.geindustrial.com/ge-interlogix/emea
Although PROTECH provides high security indoor intrusion sensors for the military and government markets, our specialty is outdoor protection. Since we first introduced our PIRAMID outdoor dual technology
Intelligent Wireless GSM Alarm System 00M2K User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. Contents [Function Instruction] [Alarm
IndigoVision Alarm Panel User Guide THIS MANUAL WAS CREATED ON 2/21/2017. DOCUMENT ID: IU-AP-MAN002-4 Legal considerations LAWS THAT CAN VARY FROM COUNTRY TO COUNTRY MAY PROHIBIT CAMERA SURVEILLANCE. PLEASE
Flair 500 Series s Basics Flair Multi-Zone s (MZAs) are fully functional, flexible, programmable micro controller based alarm control panels. They can be used independently d or in conjunction with other
Remote Terminals Product Data Sheet Features: Based around two core products, the Mx- 4010 Remote Display Terminal (RDT) and the fully functional Mx-4020 Remote Control Terminal (RCT). Both remote terminals
HRX3000 Technical Manual Contents: Specification...2 Connectors...3 Power (J21)...3 RS-485 Network Connectors (J6 and J7)...4 RS-232 to PC (J8)...5 Printer and Fire Alarm Panel (J19)...6 TCP/IP...8 Modem
Universal fault annunciator for panel mounting Communication over Ethernet USM - Universal-fault annunciator for panel mounting Low depth housing for panel mounting Versions with 8, 16, 32 or 48 inputs
Available online at www.sciencedirect.com Procedia Engineering 11 (2011) 308 313 The 5 th Conference on Performance-based Fire and Fire Protection Engineering Construction of Wireless Fire Alarm System
ASCO 5350 The ASCO 5350 ATS Remote Annunciator is listed under the Underwriter s Laboratories Standard UL-1008 for Automatic Transfer Switch accessories. This stand-alone device provides individual status
Roger Access Control System User manual for CPR32-NET network controller Firmware version: 1.0.14 or newer Hardware version: 1.0 Document version: Rev. E 2016 ROGER sp. z o.o. sp.k. All rights reserved.
WARNING: This manual contains information on limitations regarding product use and function and information on the limitations as to liability of the manufacturer. The entire manual should be carefully
Installation and Operating Manual SR868C6 System Regulator for Solar Thermal Systems Display Panel Illustration Pos. Button on display panel Button description 1 Green lamp Power indication lamp 2 On/Off
ViewMatrix Software for Online Monitoring & Control of Matrix2000 Conventional Fire Alarm Panels Version: 2.0 Revision: 0.1 CONTENTS 1. Introduction...3 2. Keyboard...5 2.1 POWER indication - Normal Operation...5
CV-350 TCP/IP Access Control System System Overview July 2015 Open Product Access Camden delivers the power of advanced IP access control differently than our competitors! - All product sales exclusively
LED Driver Module Installation Guide 1.0 Notice These instructions are for installing Radionics LED Driver Module in a fire alarm system controlled by Radionics D8024 or D10024 Fire Alarm Control Panels
MOBILE CALL GSM Alarm System GSM Alarm System System disarmed 11/26/2013 User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. CONTENTS
This instruction document consists of 2 parts : one part about the assembly of the components and one part about configuration and starting-up of the system. The assembly is done by the qualified installer
Operation Instructions for T300 Thank you for choosing the ViewX human-machine interface. For more efficient use of the ViewX human- machine interface, please read the included quick startup guide before
COMMUNICATOR ET08 User Manual v1.0 Safety instructions Please read and follow these safety guidelines in order to maintain safety of operators and people around: GSM communicator (gateway) ET08 (further
0BThe System The Security Management System should be capable of Controlling and Monitoring Access through the doors, Monitor and control Inputs and Outputs, include an Integrated Video Badging, Integrate
Replaceable LED modules 11 Alarm Sequences as per ISA-18.1 standard Each channel/window fully field programmable RS232 or RS485 MODBUS-RTU communication Repeat relay for each window and multifunction relays
Version 1.4 15/04/2013 Manufactured for Thank you for choosing our product. This manual will help you with proper support and proper operation of the device. The information contained in this manual have
The future of security, secured IP by security professionals, for the professional security industry Installation and Service Engineer Support Telephone: +44 871 977 1133 (Calls are charged at 10p a minute
Access Control Solutions ZKAccess is a division of ZKTeco, which engages in access control products and solutions. The product line includes IP-based standalone access control, networked access control
RC802/804-240B 8E1 Modular Fiber-Optic Multiplexer (Rev. M) User Manual Raisecom Technology Co., Ltd. (04/2005) 1. Cautions Please read the following notices carefully before installing and using the device,
G LMS 188 4P BMS August, 2018 LMS-188-4P-BMS 4 POINT DIGITAL MONITOR/ALARM WITH PROTOCOL CONVERTER OPERATING INSTRUCTIONS! WARNING: This product can expose you to chemicals including lead, which is known
Rev 2.0 (May 2013) Installer Manual 1 Current Part Numbers: Fratech Multipath-IP E-Link STU PCB & Accessory Kit only In Metal Enclosure with Power Supply 998325-PK 998325-XS Installer Manual This document
DGPROX PIN Code and/or Badge STAND-ALONE PROXIMITY SYSTEM Wiring diagram PCB front view 8 WIRING DIAGRAM AND INSTRUCTIONS ST2 1 3 1 3 Warning Do not use a switching power supply because of the interference
Pioneer-R16 Gas Monitor Operator s Manual Edition 7/2/97 RKI INSTRUMENTS, INC RKI Instruments, Inc. 33248 Central Ave, Union City, CA 94587 (510) 441-5656 Chapter 1: Description About the Pioneer-R16 Gas
AUTODIALER SYSTEM FOR LIFTS MANUAL HELPY 2W-V 05/06/2018 DESCRIPTION Autodialer to be fitted behind the cop or on top of the car / retrofit. A Connector for Esse-ti power supply (12 Vdc) B Micro SD Card
NGC-40 PANEL MOUNTED ADVANCED MODULAR HEAT-TRACING CONTROL SYSTEM Local configuration and monitoring with Raychem Touch 1500 touch screen display PRODUCT OVERVIEW The nvent RAYCHEM NGC-40 is a multipoint
Tables of Contents Page Application 1 Features 1 Important Safety Information! 2 Note to this Guide 2 Further Information 2 Device Variants 2 General Functions 3 Annunciator Sequences - ISA 18.1 3 Plan
Panel Mounted Fault Annunciator Series BSM / USM Panel-mounted fault annunciator Annunciators for panel mounting with,,,, 0 and signal inputs Storage of the last state of inputs and sequence in the case
GSD WIN USER MANUAL Application Version: 2.0 and above Date Written: 03/09/2010 Copyrights - 2010-2012, Global Security Devices, All Rights Reserved TABLE OF CONTENTS TABLE OF CONTENTS...2 SETTING UP A
ABOUT THIS DOCUMENT AND THE DOCUMENT STRUCTURE WE USE isocket Smart Relay is a complex Smart House system which is installed in the fuse cabinet (electric cabinet) in the house. We therefore assume that
Door Activation Devices CM-RQE70A PIR REQUEST TO EXIT DETECTOR THIS PACKAGE INCLUDES (2) #6 x 3/4" Screws (2) 3/16" Wall Plugs (2) MOV's BP7175 1. GENERAL DESCRIPTION Camden CM-RQE70A Request-to-Exit Sensor
KP-100A BACKLIT DIGITAL KEYPAD FOR ELECTRIC LOCK AND SECURITY SYSTEM INSTALLATIONS Alarm Controls ASSA ABLOY, the global leader in door opening solutions 10027 S. 51st Street, Ste. 102 Phoenix, AZ 85044
Product Overview: The Pertronic F4 Remote LED Mimic / Aux Relay Module F4-RMAX is an optional extra for the Pertronic F4 conventional 4-zone fire alarm panel. This board enables the fire alarm panel to
E21.X.01.6C-05 Operating Manual EB2000 MC page 1 Operating manual EB2000 MC EASYBUS-display with MIN-/MAX-alarm for up to 9 sensor modules Version 3.0 Pursuant to EN 50 081-1 and EN 50 082-2 for unlimited
Refrigeration Controller Operator s Manual (HRC) PO Box 6183 Kennewick, WA 99336 www.jmcvr.com 1-509-586-9893 Table of Contents TABLE OF FIGURES...1 OVERVIEW OF THE HRC CAPABILITIES...2 INSTALLATION AND
VANDAL RESISTANT BACK-LIT WEATHERPROOF ACCESS CONTROL KEYPAD WITH WIEGAND OUTPUT & DATA I/O DOLKPS1KB Programming & Installation Manual FOR ELECTRIC LOCK, INTER-LOCK AND SECURITY SYSTEM INSTALLATIONS DOLKPS1KB
Two Door Access Controller Panel Board TCP/IP Wiegand with Software and Power Supply Included 100,000 Users VS-AXESS-4DLX Installation Manual 1 User Manual COPYRIGHT Visionis Technology. ALL RIGHTS RESERVED.
Introduction The CO Transmitter uses an electrochemical sensor to monitor the carbon monoxide level and outputs a field-selectable 4-20 ma or voltage signal. The voltage signal may also be set to 0-5 or
CAN OBD READER REFERENCE DESIGN KIT USER GUIDE 1. Standard ToolStick Handling Recommendations The ToolStick Base Adapter and daughter cards are distributed without any protective plastics. To prevent damage
NZ 400 AUTOMATIC FIRE ALARM SYSTEM OPERATORS MANUAL Document No...G108WO1.DOC Serial No... Issue Date...17 th SEPTEMBER 1999 Software Version...1.4 APPROVED TO: NZS 4512:1997 AS/NZS 3548:1992 Fire Alarm