1 Taming the Health Care Building Codes NFPA vs. The International and Chicago Building Codes
2 Comparing the Codes: NFPA 101 Life Safety Code (2000) (NFPA) International Building Code (2012) (IBC) Chicago Building Code (2012) (CBC)
3 Comparing the Codes: NFPA 101 Life Safety Code (2000) (NFPA) International Building Code (2012) (IBC) Chicago Building Code (2012) (CBC) In addition, don t forget: The Hospital Licensing Act (HLA) Guidelines for Design and Construction of Health Care Facilities (FGI)
4 Why do we need to do this?
5 Challenge Question: What is the REQUIRED rating for a corridor wall in NEW construction in a Hospital in the State of Illinois?
6 ANSWER: It Depends
7 Factors: Where is the facility Chicago needs to follow BOTH the Chicago Building Code (CBC)for local AND the 2000 NFPA 101 Life Safety Code (LSC) for IDPH/CMS/JCAHO or DNV. Outside Chicago MOST municipalities follow the International Building Code (IBC), PLUS you must use the 2000 NFPA 101 Life Safety Code (LSC) for IDPH/CMS/JCAHO or DNV. Beware of other local ordinances requiring other editions of NFPA or even local supplemental codes. ALWAYS use the most stringent requirement.
8 2000 NFPA 101: Section * for new construction (and facilities built or remodeled after March 2003) requires Corridor walls shall form a barrier to limit the transfer of smoke. Such walls shall be permitted to terminate at the ceiling where the ceiling is constructed to limit the transfer of smoke. No fire resistance rating is required for corridor walls. Section Doors protecting corridor openings shall be constructed to resist the passage of smoke Door ratings for hazardous areas, stairs or other vertical openings must meet other required fire ratings.
9 2000 NFPA 101: For existing buildings, Section requires Corridor walls shall be continuous from the floor to the underside of the floor or roof deck above, through any concealed spaces, such as those above suspended ceilings, and through interstitial structural and mechanical spaces, and they shall have a fire resistance rating of not less than ½ hour. Exception: for smoke compartments which are fully sprinklered, NFPA allows the partitions to terminate at the ceiling, similar to chapter 18. Section requires that doors be substantial doors, such as those constructed of 1 ¾ (4.4-cm) thick, solid-bonded core wood or of construction that resists fire for not less than 20 minutes and shall be constructed to resist JENSEN the & HALSTEAD passage LTD. of smoke
10 International Building Code: Table Allows zero (0) fire rating of corridor walls in fully sprinklered buildings. Section requires Corridor walls shall be constructed as smoke partitions in accordance with section 710. Section 710 allows the partition to terminate at the underside of the ceiling above where the ceiling membrane is constructed to limit the passage of smoke. Section does not require the corridor doors to be rated except for those in a wall required to be rated by section
11 Chicago Building Code: Section ( ) (a) Requires that corridor walls be one (1) hour fire rated that the doors to only have a 20 Minute Fire Rating in a minimum 18 gage steel frame.
12 Chicago Building Code: Challenge Question: What is the exception for the one (1) hour fire rated corridor requirement in the Chicago Building code?
13 Chicago Building Code: The same section allows the partition to stop at the ceiling if the building is fully sprinklered INCLUDING THE CEILING SPACES.
14 Challenge Question: What is the difference between a SMOKE PARTITION and a SMOKE BARRIER?
15 Simple Answer: A Smoke Partition is an Assembly of Components that limits the passage of smoke. A Smoke Barrier is a rated partition that separates the building into compartments.
16 2000 NFPA 101: Smoke Partition NFPA uses the term barrier to limit the passage of smoke These types of partitions (such as corridor partitions) are allowed to stop at the ceiling. Section A An architectural, exposed, suspended-grid acoustical tile ceiling with penetrating items such as sprinkler piping and sprinklers; ducted HVAC supply and return-air diffusers; speakers; and recessed lighting fixtures is capable of limiting the transfer of smoke. Be careful which partitions that you stop at the ceilings. The HLA and FGI have requirements for sound transmission into patient rooms and other areas.
17 2000 NFPA 101: Smoke Barrier Where Required : To divide every story used by inpatients for sleeping or treatment into not less than two smoke compartments To divide every story having an occupant load of 50 or more persons, regardless of use, into not less than two smoke compartments. (Look at Exceptions for items specific to NFPA) To limit the size of each smoke compartment required above into an area not exceeding 22,500 square feet. Limit the travel distance from any point to reach a door in the required smoke barrier to a distance not exceeding 200 feet.
18 2000 NFPA 101: For Smoke Barriers: Section requires the smoke barrier to be constructed in accordance with section 8.3 and to have a fire resistance rating of not less than 1 hour. Section requires that the doors in the smoke barrier be of 1 ¾ thick, solid-bonded wood core doors, or shall be of construction that resists fire for not less than 20 minutes Section Smoke barriers required by this code shall be continuous from an outside wall to an outside wall, from a floor to a floor, or from a smoke barrier to a smoke barrier or a combination thereof. Such barriers shall be continuous through all concealed spaces, such as those found above a ceiling, including interstitial spaces.
20 IBC: Smoke Partition Essentially as discussed earlier for Corridor partitions Just limit the passage of smoke per section 710. Smoke Barrier The requirements in mirror those in NFPA, WITHOUT the exceptions.
21 Chicago Building Code: Every sleeping floor shall be divided into at least two smoke sections by a one (1) hour fire rated smoke stop partition. Doors shall be C Label (45 Minutes). IN ADDITION - every institutional unit over two stories in height, every floor over 12,000 square feet which contains bed rooms or wards shall be divided into two areas by a 3-hour fire-resistive separation
22 Challenge Questions: Are Smoke Dampers required in Smoke Barriers where ductwork penetrates the barrier? Are Fire dampers required in these partitions since they are also required to be fire rated?
23 ANSWER: It Depends
24 Factors: Where is the facility? Is the smoke barrier ALSO being used as a Fire Wall with a rating of two (2) hours or greater?
25 Chicago Building Code: The City has NO requirement for smoke dampers. FIRE DAMPERS are required at the required threehour barriers (or any other partition with a fire resistance rating of two (2) hours or more).
26 2000 NFPA 101: Section , Exception No. 2* Allows smoke dampers to be omitted in fully ducted HVAC systems. If the Barrier is also a rated building separation, horizontal exit or other type of partition requiring a fire rating of two (2) hours or greater, a FIRE DAMPER must be installed.
28 International Building Code: The International building code does NOT have an exception to delete smoke dampers except at Critical Exhaust Ducts. Therefore, smoke dampers must be used in most locations outside of Chicago. Combination Smoke/Fire dampers must be used at partitions with a fire rating of two (2) hours or greater.
29 Fire Barrier Locations: Mixed Use separations All codes Fire compartment size restrictions in IBC and CBC due to a factor of construction type and building height. Horizontal Exits
30 Challenge Question: What is a Horizontal Exit?
31 ANSWER: A horizontal exit is a fire barrier that is used when the distance to another legal exit (stair or access to the exterior) is too great to meet code.
32 Components of a Horizontal Exit: It is a minimum Two (2) hour fire rated partition that spans from outside wall to outside wall to separate the building into fire compartments. The adjacent horizontal separations (floors below and above) also need to maintain the Two (2) hour rating. For Healthcare, horizontal exits can account for up to 2/3 of the total exiting. It is important to read ALL of section for ALL requirements. VERY IMPORTANT A fire alarm pull station must be within five (5) feet of the horizontal exit doors.
33 Delayed Egress Locks: Used to help limit movement into or out of areas that must still be used as a means of egress. Obstetric Units Pediatric Units Secondary exits through restricted areas such as surgical suites ICU s Geriatric units Sometimes Psychiatric units
34 Delayed Egress Locks: Allows the door(s) to remain locked for 15 seconds after someone tries to exit the door. Outside of Chicago, the authority having Jurisdiction can allow an increase of up to 30 seconds. DON T FORGET to apply to ALL AHJ s involved. Section has all of the requirements for NFPA For IBC, see section For CBC, see ( ) All three Codes require that the building be fully sprinklered, and that the locks drop out upon activation of the fire alarm. Don t forget to make sure that you have emergency lighting at the door so that the signage can be read.
35 Challenge Question: How many Delayed Egress Locks can you have in the path of Egress?
36 ANSWER: NFPA and IBC allow only ONE (1) delayed egress lock in the path of travel to the public way.
37 Psychiatric Units: Can be locked down, and have multiple locks in the path of egress. Staff MUST have keys or keycards on them at all times! And be trained for fire situations.
38 Electronic Locks: Be Careful with electric strikes on Fire Rated Doors, especially Stair Doors. It is acceptable to use FAIL SECURE on room doors (as long as ALL staff have keys) and occupants can gain access to the means of egress without a key or keycard. On stair doors, and rated cross corridor doors, use with caution. If you need access to all floors during an emergency situation, the strikes will be set for FAIL SAFE. This will DISABLE the latching function of the rated door creating a hazard. It is usually best to use magnetic locks or electric locksets in these locations.
39 Suites: Purpose: Allows for open areas, not every room is required to have a smoke tight, latching door, or even have a door. Can help alleviate a dead end condition. Can be used in an area where access to two exits is not desirable or feasible Can allow operations to store carts and items in the Passageway (BEWARE of what is being stored so that it is not considered open storage).
40 Suites: Requirements: All codes limit size of suites for patient sleeping rooms to 5,ooo square feet. NFPA and IBC allow non-patient sleeping areas to be 10,000 square feet. SEPARATION OF SUITES: NFPA Not specifically called out in the 2000 version. The interpretation from NFPA is to have a partition that limits the passage of smoke. IBC Smoke partition complying with 710 CBC One (1) hour construction with solid wood doors.
41 Suites: Question: Can a suite exit into another suite?
42 Suites: Answer: It Depends
43 Suites: IBC allows one of the exits in a two exit suite to pass through another complying suite. CBC does not address one way or the other. NFPA does not specifically allow it but it also doesn t prohibit it. The official interpretation from NFPA is to look at the 2006 code which they state Clarifies the intent of the 2000 Code BUT
44 Suites: Beware, IDPH and CMS do not officially accept this interpretation. IDPH interpretation: Any suite must comply with the travel distance rules for suites (50 or 100 ) to a corridor door, to a door directly to the outside at the level of exit discharge, and/or in some cases an exit from the most remote point in a suite. Once this item is met, a second path, where required may pass through an adjoining suite. Verify specific conditions with IDPH PRIOR to implementing.
46 Taming the Health Care Building Codes David Dastur AIA, NCARB, Senior Principal Jensen & Halstead, Ltd 358 west Ontario Street Chicago, Illinois
Page 1 of 92 ST - K0000 - INITIAL COMMENTS Title INITIAL COMMENTS Type Memo Tag These guidelines are meant solely to provide guidance to surveyors in the survey process. ST - K0100 - General Requirements
Changes to the 2018 Joint Commission Comprehensive Accreditation Manual for Hospitals (CAMH) The following represents a review of the Life Safety chapter of the new 2018 Joint Commission CAMH manual for
Page 1 of 94 ST - K0000 - Initial Comments Title Initial Comments Statute or Rule Type Memo Tag These guidelines are meant solely to provide guidance to surveyors in the survey process. ST - K0100 - General
FIRE PROTECTION KEY DESIGN CONCEPTS IN HEALTHCARE FACILITIES Scott Twele, Aman Shah Steven Dannaway AIA Healthcare Group Introductions Presenters Coffman Engineers Scott M. Twele, P.E. Operations Manager,
State of Alabama Department of Public Health Fax: 334-206-5890 Web Site: www.adph.org.facmgmt Mike Free Building Construction Specialist Technical Services Unit Office of Facilities Management 334-206-5221
Page 1 of 75 ST - K0000 - Initial Comments Title Initial Comments Statute or Rule Type Memo Tag These guidelines are meant solely to provide guidance to surveyors in the survey process. ST - K0001 - OTHER
Issued September 20, 2017 Changes to Environment of Care, Equipment Management, and Life Safety Chapters Related to Life Safety Code Updates Environment of Care (EC) Chapter Home Care (OME) Accreditation
Presented by: Brad Keyes, CHSP Senior Consultant Keyes Life Safety Compliance, LLC Changes to Life Safety Compliance Healthcare leaders will have to deal with many changes in Life Safety compliance when
JOINT COMMISSION PREPAREDNESS / STATEMENT OF CONDITIONS DRAWINGS WSSHE SOUTHWEST CHAPTER NOVEMBER 19, 2015 AGENDA INTRODUCTION OF PRESENTERS SOC VS. FIRE & LIFE SAFETY DRAWINGS HAZARDOUS AREAS VS. INCIDENTAL
CHAPTER 12 COMPLIANCE ALTERNATIVES SECTION 1201 GENERAL 1201.1 Scope. The provisions of this chapter are intended to maintain or increase the current degree of public safety, health, and general welfare
WHITE PLAINS SMOKE CONTROL CODE a. Application of Code. PART 1. GENERAL REQUIREMENTS The following uniform standards and procedures shall apply to the design, installation and testing of new smoke purge
CHAPTER 1 SCOPE AND ADMINISTRATION 102.7 Referenced codes and standards. The codes and standards referenced in this code shall be those that are listed in Chapter 45 47 and such codes and standards shall
RESIDENTIAL CARE USER GUIDE UPDATES TO MANITOBA BUILDING/FIRE CODE: Manitoba Regulation 221/2015 and Manitoba Regulation 222/2015 DATE: MARCH 17, 2016 1. INTRODUCTION On April 1, 2016, new building and
Copyright National Fire Protection Association 2013. All rights reserved. This copy is solely for your personal, noncommercial use in connection with participation in the NFPA Standards Development Process.
CHAPTER 13 PERFORMANCE COMPLIANCE METHODS SECTION 1301 GENERAL 1301.1 Scope. The provisions of this chapter shall apply to the alteration, repair, addition and change of occupancy of existing structures,
TIPS FOR BETTER JOINT COMMISSION SURVEYS Washington Society for Healthcare Engineering September 21, 2011 Yakima, Washington The BASICS Most Failed Standards. Scoring. Electronic S. O. C. I.L.S.M. Building
2. The Group F occupancy has have an a combined occupant load of 500 or more above or below the lowest level of exit discharge. Exception: Manual fire alarm boxes are not required where the building is
DEPARTMENT OF HEALTH AND HUMAN SERVICES CENTERS FOR MEDICARE & MEDICA SERVICES FIRE SAFETY SURVEY REPORT - HEALTH CARE Medicare Medicaid 2. NAME OF FACILITY 2. (A) MULTIPLE CONSTRUCTION (BLDGS) 3. SURVEY
Compliance w/ the 2012 Life Safety Code Implications of the 2012 NFPA Code Set for Existing & New ASCs William E. Lindeman, AIA http://www.weldesigns.com Financial Interest Disclosure The presenter provides
2017 The Healthcare Environment Update John Maurer, SASHE, CHFM, CHSP Engineering Department The Joint Commission Engineering Department 2017-1 Most Cited Standards Standard 2015 % Noncompliance 2016 %
Developing a Healthcare Facility Fire Door Inspection Program WELCOME Moderator: Richard Schieferdecker support.webinato.com Audio QUESTIONS How To Ask a Question: 1 POLLING There will be occasional interactive
SPACE TYPE: LIBRARY Construction Criteria The unit costs for Library space types are based on the construction quality and design features in the following table. This information has been generally organized
Issued June 28, 207 Changes to Environment of Care and Life Safety Chapters Related to Life Safety Code Updates Environment of Care (EC) Chapter Nursing Care Center (NCC) Accreditation Program Standard
DEPARTMENT OF HEALTH AND HUMAN SERVICES CENTERS FOR MEDICARE & MEDICAID SERVICES FIRE SAFETY SURVEY REPORT - 2000 LIFE SAFETY CODE Intermediate Care Facilities for the Mentally Retarded LARGE PART I Figure
Module 7 Control of Smoke & Highlights of Code Requirements 1 Module 7 Overview This module will cover: 1. The requirements of smoke control in the Ohio Building Code Section 909 2. The differences between
AHC Meeting #7 July 12-13, 2012 A. 2012 Cycle Approved Code Changes The following are the APPROVED Group A code changes created by the AHC Fire Safety Work Group that were considered at the 2012 Code Development
Page 1 of 34 ST - K0000 - INITIAL COMMENTS Title INITIAL COMMENTS Statute or Rule Type Memo Tag These guidelines are meant solely to provide guidance to surveyors in the survey process. ST - K0001 - OTHER
Short Term Accommodations Fire Code Requirements 1 Foreward The following is a comprehensive reference to Retrofit 9.3 of Division B of the Ontario Fire Code (OFC). Retrofit provisions were developed to
SECTION 909 SMOKE CONTROL SYSTEMS 909.1 Scope and purpose. This section applies to mechanical or passive smoke control systems when they are required for new buildings or portions thereof by provisions
2012 Life Safety and Health Care Facility Codes - Door Inspections and Other Critical Inspection, Testing and Maintenance Will begin at 1 pm Housekeeping Announcements Problems during the call? Press *0
Moreno Valley Fire Department Fire Prevention Bureau Residential Based Care Facility Guidelines Approved and Authorized By: Randall Metz, Fire Marshal Issued: January 1, 2011 Residential Based Care Facilities
Title: Effective Date: 01/01/14 Revised Date: 1/1/14 Code References: Title 16, Chapter 16.16 of the Roseville Municipal Code, NFPA 72 Note: This standard is a summary of Fire Department clarifications
M.S. Montgomery Fire Marshal September 1, 2010 This document describes rules changes affecting the operation and fire safety in foster homes licensed and regulated by the Texas Department of Family and
Code Reference NFPA 101 126.96.36.199 (2009 188.8.131.52 (2012 1.1.7 (New) 184.108.40.206 Florida Specific Amendment Anytime a reference is made to NFPA 1 or NFPA 101 within this Code, it shall be the Florida specific version
2017 Accreditation Updates Tennessee Healthcare Engineers Association 2017 Spring Conference Pickwick Landing State Park Counce, Tennessee 38326 Presented May 17, 2017 By Ken Gregory Vice President, Accreditation
Life Safety - Means of Egress/Exits NFPA 101 Properly designed exits provide a safe path of escape from a fire or other emergency environment. The means of egress (exits) should be arranged to permit all
Managing the Interim Life Safety Measures (ILSM) Process 1 A Program for The Texas Association of Healthcare Facility Management Monday, April 30, 2012 Robert H. Bartels, CHFM CHSP CHEP SASHE President,
FIRE SAFETY INSPECTION REPORT AMITY DESIGNS LTD. HOUSE#7&9, ROAD#9 BLOCK D, SECTION #11MIRPUR DHAKA OTHER FACTORIES: NONE April 21, 2014 Page 2 SUMMARY was surveyed for fire safety on 4/21/2014 by Hughes
Page 1 of 98 ST - Y0000 - INITIAL COMMENTS Title INITIAL COMMENTS Type Memo Tag These guidelines are meant solely to provide guidance to surveyors in the survey process. Based on the LSC surveyor's determination
Healthcare Interpretations Task Force MEMORANDUM TO: FROM: Heathcare Interpretations Task Force Robert Solomon DATE: May 30, 2014 SUBJ: HITF Meeting Agenda and Meeting Room Location Information Attached
Department of Health Life Safety Code Update Presented by: Charlie Schlegel, Director Division of Safety Inspection Overview CMS Adoption of the 2012 Life Safety Code (LSC) and 2012 Health Care Facilities
ICC Committee on Health Care Hospitals and Nursing Homes Group A Draft Proposals Revised 11-16-2017 Copyright 2017 International Code Council, Inc. Work groups are: G/MOE - General/Means of egress Chair:
TOPICS IN CODE ENFORCEMENT CAHED SE DISTRICT MEETING FEBRUARY 17, 2017 Mark Jelinske Cator, Ruma, and Associates email@example.com 303-462-8475 TALKING POINTS Conducting Surveys on NFPA 2012 as of
Table of Contents CHAPTER 10 ADMINISTRATIVE RULES FOR CERTIFICATION OF CHILD CARE FACILITIES FIRE STANDARDS FOR FAMILY CHILD CARE HOME Section No. Subject Page No. 1 Authority and Purpose 10-1 2 Definitions
Ch. 54 GROUP B EDUCATIONAL 34 CHAPTER 54. GROUP B EDUCATIONAL OCCUPANCY GROUP Sec. 54.1. Group B occupancies. 54.2. Classification. 54.3. Nursery schools, day care centers and the like. 54.4. Separation
DATE: 04/11/02 APPROVED: NUMBER: FP0-010 REVISED: FIRE PREVENTION STANDARDS TITLE: Large Family Day Cares (9-14 kids) PURPOSE: The purpose of this standard is to acquaint the applicant with the applicable
Life Safety Checklist For Assisted Living and Specialty Care Assisted Living Facilities in Alabama prepared by: TIM BARRON, ARCHITECT, INC. 212 EDEN VIEW DRIVE HOOVER, AL 35244 205.444.1443 Tim@TimBarron.com
FIRE SAFETY WORK GROUP REPORT TO AHC MEETING #4 CHICAGO, IL - OCTOBER 5-6, 2011 PART I ROUND 1 ISSUES CODE CHANGES Issue 1: DECORATIONS ON WALLS Gary Lewis/Eugene Jaques 8-12-11 IBC [F] 806.1 (IFC 807.1)
The City of Long Beach City of Long Beach Medical Marijuana Facilities Permit Requirements Information Bulletin BU-051 Eff: 01-30-2017 Rev: 11-1-2017 The purpose of this Information Bulletin is to assist
2015 MECHANICAL CODE REQUIREMENTS ANTRIM COUNTY BUILDING DEPARTMENT PO BOX 188 205 CAYUGA STREET BELLAIRE, MI 49615 (231) 533-8373 FAX (231) 533-6041 Mechanical requirements for residential buildings per
Prepublication New Text Jan 2018 Changes to Environment of Care and Life Safety Chapters EC.01.01.01 EP3 Related to Life Safety Code Updates Hospital (HAP) Accreditation Program The hospital has a library
Sam Docknevich, PSP, Security Service Portfolio Manager Are You Prepared? The impending impact of Code on Servicing Security Systems Siemens AG 2015 All rights reserved. usa.siemens.com/infrastructure-cities
Secondary Suites Guidelines for the construction of Accessory Secondary Suites in the City of Abbotsford August 2015 PLANNING & DEVELOPMENT SERVICES Building Permits & Licences 1st Floor, 32315 South Fraser
Open to Below: A Discussion of Allowed Floor Openings Kevin S. Hastings, P.E., LEED AP Jay A. Ierardi, Ph.D., P.E., LEED AP R.W. Sullivan Engineering (617) 523-8227, Fax (617) 523-8016 http://www.rwsullivan.com
Ezekiel Enterprises, LLC Fire Protection System Design Course# FP201 EZ-pdh.com Ezekiel Enterprises, LLC 301 Mission Dr. Unit 571 New Smyrna Beach, FL 32128 800-433-1487 firstname.lastname@example.org FIRE PROTECTION
NFPA-101 Life Safety Code (2012), ADA & CMS Requirements for Healthcare Facilities: Compliance Made Easy with Low-Profile Fire Extinguishers Webinar Presentation Kevin M. Kozlowski, President / CEO September
MSL Healthcare Partners, Inc. Wild Card EPs Paraphrase K-tag # EC.02.04.03 EP 14 All other electrical K-920 equipment in patient care vicinity NFPA 992012, Chapter 10 K-924 K-928 K-931 K-tag Description
TRI-LAKES MONUMENT FIRE PROTECTION DISTRICT LOCAL AMENDMENTS INTERNATIONAL FIRE CODE 2009 December 5, 2012 1 Chapter 1 Administration Chapter 5 Fire Service Features Chapter 9 Fire Protection Systems Chapter
SPACE TYPE: JUDICIAL CHAMBER Construction Criteria The unit costs for Judicial Chamber space types are based on the construction quality and design features in the following table. This information has
APPENDIX A 2012 International Building Code Amendments The following sections, paragraphs, and sentences of the 2012 International Building Code are hereby amended as follows: Standard type is text from
CHAPTER 9 FIRE PROTECTION SYSTEMS > SECTION 901 GENERAL 901.1 Scope. The provisions of this chapter shall specify where fire protection systems are required and shall apply to the design, installation,
Fire Safety, Risks, & Response at Jackson Health System 2016 JHS Annual Mandatory Education Objectives of this module Become familiar with applicable administrative policies related to Fire Safety, Risks,
Nursing Facility Life Safety Code Today and Tomorrow Kenneth Daily, LNHA email@example.com April 2014 Life Safety Code Life Safety Code 101 (2000 Ed.) Promulgated by the National Fire Protection Association
M E M O R A N D U M TO: FROM: NFPA Technical Committee on Alternative Approaches to Life Safety Linda MacKay DATE: December 28, 2010 SUBJECT: NFPA 101A ROP TC Letter Ballot (A2012 Cycle) The ROP letter
Informational Bulletin Date Issued: July 11, 2010 Bulletin No: 2010-11N Topic: Code Reference For Use By: Inspection Guide - General Sonoma County Code California Fire Code California Health and Safety
Construction Warehouse FPE 596 Culminating Experience In Fire Protection Engineering Final Project (Spring 2014) By Ben Johnson 1 Statement of Disclaimer This project report is a result of a class assignment;
First Revision No. 6-NFPA 90A-2012 [ Chapter NFPA ] 220.127.116.11.5 Materials within a raised floor plenum exposed to the airflow shall be (a) noncombustible or (b) exhibit a maximum flame spread index of 25
TITLE 77: PUBLIC HEALTH CHAPTER I: DEPARTMENT OF PUBLIC HEALTH SUBCHAPTER c: LONG-TERM CARE FACILITIES PART 300 SKILLED NURSING AND INTERMEDIATE CARE FACILITIES CODE SECTION 300.3010 APPLICABILITY Section
Health Chapter 420-5-22 ALABAMA STATE BOARD OF HEALTH ALABAMA DEPARTMENT OF PUBLIC HEALTH ADMINISTRATIVE CODE CHAPTER 420-5-22 SUBMISSION OF PLANS AND SPECIFICATIONS FOR HEALTH CARE FACILITIES TABLE OF
2012 B.C. Building Code Checklist (Division B Part 3) This checklist is provided as a reference only. The submission of this checklist with a Building Permit application should not be considered as a substitute
2018 Joint Commission Standards What s New in the EC/LS/UM GASHE Annual March Meeting Lake Blackshear Resort Presented March 9, 2018 By Ken Gregory, CHSP President Ken Gregory Consulting 1 2018 Joint Commission
St. Number Dir Street Name Street Type Inspected Time of Day to be Re-inspected Zip Code Occupancy Type Emergency Contact Phone (Inc. Area Code) Building Owner Building Owner Mailing Address Bldg. Owner
Chapter 21, Emergency Control Functions and Interfaces Summary. Chapter 21 is new. These requirements were formerly found in Chapter 6, Protected Premises Fire Alarm Systems. The term fire safety function
Introduction Florida Building Code 2010 Chapter 9 Fire Protection Systems This course will cover specific sections of Chapter 9 that relate to fire alarm systems. While many contractors are familiar with
This information is intended to assist you in preparation for the annual high-rise inspection. This is not a complete list and the Inspector may identify other conditions or issues in the building that
PASS / RESUBMIT Rancho Santa Fe Fire Protection District P.O. Box 410 18027 Calle Ambiente Rancho Santa Fe California 92067-0410 Tel. (858) 756-5971 Fax (858) 756-4799 FIRE PLAN CHECK CORRECTION List for
EL DORADO COUNTY REGIONAL FIRE PROTECTION STANDARD Installation of Residential Fire Sprinkler Systems STANDARD #C-002 EFFECTIVE 03-19-2009 PURPOSE: To ensure that sprinkler plans submitted for review contain
780 CMR: STATE BOARD OF BUILDING REGULATIONS AND STANDARDS 780 CMR: MASSACHUSETTS AMENDMENTS TO AND THE INTERNATIONAL BUILDING CODE 2009 CHAPTER 9: FIRE PROTECTION SYSTEMS SECTION 901 GENERAL 901.1 Scope.
CREIGHTON ENGINEERING INC. FIRE PROTECTION CONSULTING ENGINEERS 210 N. University Road, Suite 100 Spokane Valley, WA 99206 TEL: 509.921.9755 FAX: 509.921.9806 WEB: www.creightoneng.com SCOTT R. CREIGHTON,
The following are the Proposed Amendments to 2015 edition of the Life Safety Code (NFPA 101): 1.1.1 Title. NFPA 101, Life Safety Code, shall be known as the Life Safety Code, is cited as such, and shall
Energy Conservation Code Commercial Electric CHAPTER 5 WORKSHEET 1. When using the COMcheck software, the compliance report submitted by the permit holder shall indicate that the applicable code is. a.
Recommended Amendments to the 2015 International Building Code North Central Texas Council of Governments Region The following sections, paragraphs, and sentences of the 2015 International Building Code