1 Agent Release Control Panel System Capacity Annunciators: 8 Electrical Specifications RP-2002 (FLPS-7 Power Supply): 120 VAC, 60 Hz, 3.66 amps RP-2002E (FLPS-7 Power Supply): 240 VAC, 50 Hz, amps Wire size: minimum 14 AWG (2.0 mm²) with 600 V insulation, supervised, nonpower-limited Cabinet Specifications Door: (48.92 cm.) high x (42.73 cm.) wide x 0.72 (1.82 cm.) deep. Backbox: (48.26 cm.) high x (42.29 cm.) wide x 5.25 (13.34 cm.) deep. Trim Ring (TR- CE): (55.88 cm.) high x (49.91 cm.) wide. Shipping Specifications Dimensions: Height (50.80cm) Width (57.15cm) Depth 8.50 (21.59cm) Temperature and Humidity Ranges This system meets NFPA requirements for operation at 0 49 C/ F and at a relative humidity 93% ± 2% RH (noncondensing) at 32 C ± 2 C (90 F ± 3 F). However, the useful life of the system s standby batteries and the electronic components may be adversely affected by extreme temperature ranges and humidity. Therefore, it is recommended that this system and its peripherals be installed in an environment with a normal room temperature of C/60 80 F. NFPA Standards The RP-2002(E) complies with the following NFPA 72 Fire Alarm Systems requirements: NFPA 12 CO2 Extinguishing Systems NFPA 12A Halon 1301 Extinguishing Systems NFPA 12B Halon 1211 Extinguishing Systems NFPA 72 National Fire Alarm Code for Local Fire Alarm Systems and Remote Station Fire Alarm Systems (requires an optional Remote Station Output Module) NFPA 2001 Clean Agent Fire Extinguishing Systems Agency Listings and Approvals The listings and approvals below apply to the basic RP- 2002(E) control panels. In some cases, certain modules may not be listed by certain approval agencies, or listing may be in process. Consult factory for latest listing status. UL: S635 FM approved CSFM: :0245 MEA: E Seismic Listing: Reference certifi ciate of compliance VMA by the VMC Group NOTE: For ULC-listed model, see DN RP-2002(E) The RP-2002 is a six-zone FACP for single and dual hazard agent releasing applications. The RP-2002 provides reliable fire detection, signaling and protection for commercial, industrial and institutional buildings requiring agent-based releasing. The RP-2002 is compatible with System Sensor s i3 detectors which are conventional smoke detectors that can transmit a maintenance trouble signal to the FACP indicating the need for cleaning and a supervisory freeze signal when the ambient temperature falls below the detector rating of approximately 45 F (7.22 C). In addition, the control panel is compatible with conventional input devices such as two-wire smoke detectors, four-wire smoke detectors, pull stations, waterflow devices, tamper switches and other normally-open contact devices. Refer to the Notifier Device Compatibility Document for a complete listing of compatible devices. Four outputs are programmable as NACs (Notification Appliance Circuits) or releasing circuits. Three programmable Form-C relays (factory programmed for Alarm, Trouble and Supervisory) and 24 VDC special application resettable and non-resettable power outputs are also included on the main circuit board. The RP-2002 supervises all wiring, AC voltage, battery charger and battery level. Activation of a compatible smoke detector or any normallyopen fire alarm initiating device will activate audible and visual signaling devices, illuminate an indicator, display alarm information on the panel s LCD, sound the piezo sounder at the FACP, activate the FACP alarm relay and operate an optionalmmodule used to notify a remote station or initiate an auxiliarymcontrol function. The RP- 2002E offers the same features as the RP-2002 but allows connection to 220/240 VAC. Unless otherwise specified, the information in this data sheet applies to both the 110/120 VAC and 220/240 VAC versions of the panels.
2 Agent Release Control Panel RP-2002(E) Features Listed to UL Standard 864, 9th edition. FM Approved. Designed for agent releasing standards NFPA 12, 12A, 12B, and Meets International Building Code (IBC) seismic requirements. Disable/Enable control per input zone and output zone. Extensive transient protection. Dual hazard operation. Adjustable pre-discharge, discharge and waterfl ow delay timers. Cross-zone (double-interlock) capability. Six programmable Style B (Class B) IDCs (Initiating Device Circuit). System Sensor i3 series detector compatible. Four programmable Style Y (Class B) output circuits - (special application power). Strobe synchronization: System Sensor Wheelock Gentex Faraday Amseco Three programmable Form-C relays. 7.0 amps total 24 VDC output current. Resettable and non-resettable output power. Built-in Programmer. ANN-BUS connector for communication with optional devices (up to 8 total of any of the following): N-ANN-80 Remote LCD Annunciator N-ANN-I/O LED Driver N-ANN-S/PG Printer Module N-ANN-RLY Relay Module N-ANN-LED Annunciator Module 80-character LCD display (backlit). Real-time clock/calendar with daylight savings time control. History log with 256 event storage. Piezo sounder for alarm, trouble and supervisory. 24 volt operation. Low AC voltage sense. Outputs Programmable for: Releasing Circuits or NACS NACs programmable for: Silence Inhibit Auto-Silence Strobe Synchronization Selective Silence (horn-strobe mute) Temporal or Steady Signal Silenceable or Non-silenceable Release Stage Sounder Page 2 of 4 DN-60240:C1 06/14/2011 Automatic battery charger with charger supervision. Optional Dress Panel DP (red). Optional Trim Ring TR-CE (red) for semi-fl ush mounting the cabinet. Optional N-CAC-5X Class A Converter Module for Outputs and IDCs. Optional 4XTM Municipal Box Transmitter Module. Optional Digital Alarm Communicators (411, 411UD, 411UDAC). Optional ANN-SEC card for a secondary ANN-BUS. PROGRAMMING AND SOFTWARE: Custom English labels (per point) may be manually entered or selected from an internal library fi le. Programmable Abort operation. Three programmable Form-C relay outputs. Pre-programmed and custom application templates. Continuous fire protection during online programming at the front panel. Program Check automatically catches common errors not linked to any zone or input point. USER INTERFACE: Integral 80-character LCD display with backlighting. Real-time clock/calendar with automatic daylight savings adjustments. ANN-Bus for connection to remote annunciators. Audible or silent walk test capabilities. Piezo sounder for alarm, trouble, and supervisory.
3 Agent Release Control Panel RP-2002(E) Controls and Indicators LED INDICATORS FIRE ALARM (red). SUPERVISORY (yellow). TROUBLE (yellow). AC POWER (green). ALARM SILENCED (yellow). DISCHARGED (red). PRE-DISCHARGE (red indicator). ABORT (yellow indicator). CONTROL BUTTONS ACKNOWLEDGE. ALARM SILENCE. SYSTEM RESET (lamp test). DRILL. AC Power TB1 RP-2002: 120 VAC, 60 Hz, 3.66 amps. RP-2002E: 240 VAC, 50 Hz, amps. Wire size: minimum #14 AWG (2.0 mm2) with 600V insulation. Supervised, nonpower-limited. Battery (sealed lead acid only) J12: Maximum Charging Circuit - Normal Flat Charge: amp. Supervised, nonpower-limited. Maximum Charger Capacity: 26 Amp Hour battery (two 18 Amp Hour batteries can be housed in the FACP cabinet. Larger batteries require separate battery box such as the BB-26 or NFS-LBBR). Minimum Battery Size: 7 Amp Hour. Initiating Device Circuits - TB4 and TB6 Zones 1-5 on TB4. Zone 6 on TB6. Supervised and power-limited circuitry. Style B (Class B) wiring with Style D (Class A) option. Normal Operating Voltage: Nominal 20 VDC. Alarm Current: 15 ma minimum. Short Circuit Current: 40 ma max. Maximum Loop Resistance: 100 Ohms. End-of-Line Resistor: 4.7K Ohms, 1/2 watt (PN 71252). Standby Current: 4 ma. Refer to the Notifi er Device Compatibility Document for listed compatible devices. Notifi cation Appliance and Releasing Circuit(s) - TB5 and TB7 Four Output Circuits. Style Y (Class B) or Style Z (Class A) with optional converter module. Special Application power. Supervised and power-limited circuitry. Normal Operating Voltage: Nominal 24 VDC. Maximum Signaling Current: 7.0 amps (3.0 amps maximum per NAC). End-of-Line Resistor: 4.7K Ohms, 1/2 watt (PN 71252). Max. Wiring Voltage Drop: 2 VDC. Refer to the Notifi er Device Compatibility Document for compatible listed devices. Form-C Relays - Programmable - TB8 Relay 1 (factory default programmed as Alarm Relay) Relay 2 (factory default programmed as fail-safe Trouble Relay) Relay 3 (factory default programmed as Supervisory Relay) Relay Contact Ratings: 2 30 VDC (resistive) VAC (resistive) Auxiliary Trouble Input J6 The Auxiliary Trouble Input is an open collector circuit which can be used to monitor external devices for trouble conditions. It can be connected to the trouble bus of a peripheral, such as a power supply, which is compatible with open collector circuits. Special Application Resettable Power - TB9 Operating Voltage: Nominal 24 VDC. Maximum Available Current: 500 ma - appropriate for powering 4-wire smoke detectors (see note). Power-limited Circuitry. Refer to the Notifi er Device Compatibility Document for compatible listed devices. NOTE: Total current for resettable power, nonresettable power and Output Circuits must not exceed 7.0 amps. Special Application Resettable or Nonresettable Power - TB9 Operating Voltage: Nominal 24 VDC. Maximum Available Current: 500 ma (see note 1). Power-limited Circuitry. Jumper selectable by JP31 for resettable or nonresettable power. Refer to the Notifi er Device Compatibility Document for compatible listed devices.
4 Agent Release Control Panel RP-2002(E) Product Line Information RP-2002: Six-zone, 24 volt Agent Release Control Panel (includes backbox, power supply, technical manual, and a frame & post operating instruction sheet) for single and dual hazard agent releasing applications. RP-2002E: Same as above but allows connection to 220/240 VAC. N-CAC-5X: Class A Converter Module can be used to convert the Style B (Class B) Initiating Device Circuits to Style D (Class A) and Style Y (Class B) Output Circuits to Style Z (Class A). NOTE: Two Class A Converter modules are required to convert all four Output Circuits and six Initiating Device Circuits. 4XTM: Transmitter Module provides a supervised output for local energy municipal box transmitter and alarm and trouble reverse polarity. It includes a disable switch and disable trouble LED. N-ANN-80(-W): LCD Annunciator is a remote LCD annunciator that mimics the information displayed on the FACP LCD display. Recommended wire type is un-shielded. (Basic model is black; order -W version for white; see DN-7114.) N-ANN-LED: Annunciator Module provides three LEDs for each zone: Alarm, Trouble and Supervisory. Ships with red or black enclosure (see DN-60242). N-ANN-RLED: Provides alarm (red) indicators for up to 30 input zones or addressable points. (See DN-60242). N-ANN-RLY (16911): Relay Module, which can be mounted inside or outside the cabinet, provides 10 programmable Form-C relays. (See DN-7107). N-ANN-S/PG: Serial/Parallel Printer Gateway module provides a connection for a serial or parallel printer. (See DN- 7103). N-ANN-I/O: LED Driver Module provides connections to a user supplied graphic annunciator. (See DN-7105). ANN-SEC: Optional card for a secondary ANN-BUS. See DP-51050: Dress panel (red) is available as an option. The dress panel restricts access to the system wiring while allowing access to the membrane switch panel. TR-CE: Trim-ring (red) is available as an option. The trim-ring allows semi-fl ushing mounting of the cabinet. BB-26: Battery box, holds up to two 26 Amp Hour batteries and CHG-75. NFS-LBBR: Battery box, houses two 55 Amp Hour batteries, red. SEISKIT-COMMENC: Seismic mounting kit; required for seismiccertifi ed installations. BAT Series Batteries: Refer to DN PRN-6: UL-listed compatible event printer. Dot-matrix, tractorfed paper, 120 VAC. PRT-PK-CABLE: Programming cable. Used to update the FACP s fl ash fi rmware. (Also requires an RS485 to RS232 converter).
5 Photoelectric Smoke Detector i 3 Series General System Sensor s i³ Series photoelectric and photoelectric/thermal smoke detectors represent a significant advancement in conventional detection, incorporating three key features: installation ease, intelligence, and instant inspection. Installation ease. The i³ Series redefines installation ease with its plug-in design. This allows an installer to pre-wire the bases included with the heads. The large wire-entry port and in-line terminals provide ample room for neatly routing the wiring inside the base. The base accommodates a variety of backbox mounting methods, as well as direct mounting with drywall anchors. To complete the installation, i³ Series heads plug into the base with a simple Stop-Drop N Lock action. Intelligence. i³ Series detectors offer a number of intelligent features to simplify testing and maintenance. Drift compensation and smoothing algorithms, to minimize nuisance alarms, are standard in the i³ Series. When connected to the 2W-MOD loop test/maintenance module, an SFP-2402/-2404 panel, SFP-5UD/10UD, or RP-2001/2002 two-wire i³ detectors are capable of generating a remote maintenance signal when they need cleaning. This signal is indicated by LEDs located at the module and at the panel. To read the sensitivity of i³ detectors, the SENS-RDR is a wireless device that displays sensitivity in terms of percent-per-foot obscuration. Instant inspection. The i³ Series provides wide-angle red and green LED indicators for instant inspection of detector condition. The LEDs indicate: normal standby, out-of-sensitivity, alarm, or freeze trouble conditions. The EZ Walk loop test feature is available on two-wire i³ Series detectors when connected to the 2W-MOD loop test/maintenance module. The EZ Walk feature verifies the initiating loop wiring by providing LED status indication at each detector. Features Plug-in detector line mounting base included. Large wire-entry port. In-line terminals with SEMS screws. Mounts to octagonal and single-gang backboxes, 4 (101.6 mm) square backboxes, or directly to ceiling. Stop-Drop N Lock attachment to base. Removable detector cover and chamber for easy cleaning. Built-in remote maintenance signaling. Drift compensation and smoothing algorithms. Simplifi ed sensitivity measurement. Wide-angle, dual-color LED indication. Loop testing via EZ Walk feature. Built-in test switch. Specifications PHYSICAL SPECIFICATIONS Operating Temperature Range: For models 2W-B and 4WB: 32 F to 120 F (0 C to 49 C); for thermal models 2WT-B and 4WT-B: 32 F to 100 F (0 C to 37.8 C). Operating Humidity Range: 0% 95% RH, non-condensing. Thermal Sensor: 135 F (57.2 C) fi xed (models 2WT-B, 4WT-B). Freeze Trouble: 41 F (5 C) (models 2WT-B and 4WT-B). Sensitivity: 2.5%/foot (0.762%/meter) nominal. Input Terminals: Utilize 14 to 22 AWG wire. Dimensions (including base): 5.3 ( mm) diameter,2.0 inches (50.8 mm) high. Weight: 6.3 oz. (178.6 grams). Mounting Options: 3.5 (88.9 mm) octagonal backbox; 4 (101.6 mm) octagonal backbox; single-gang backbox; 4 (101.6 mm) square backbox with a plaster ring; or direct mount to ceiling. ELECTRICAL SPECIFICATIONS Operating Voltage: 12/24 V non-polarized nominal; 8.5 V minimum; 35 V maximum. Maximum Alarm Current: For two-wire models: 130 ma limited by control panel; For four-wire models: V, V. Alarm Contact Ratings: For four-wire models: VAC/VDC; not applicable for two-wire models.
6 Photoelectric Smoke Detector i 3 Series Agency Listings and Approvals In some cases, certain modules may not be listed by certain approval agencies, or listing may be in process. Consult factory for latest listing status. UL: S911 FM approved CSFM: :152 MEA: E Maryaldn State Fire Marshal: Permit # 2093 Architectural/EngineeringSpecifications Smoke detector shall be a System Sensor i³ Series model number, Listed to Underwriters Laboratories UL 268 Fire Protection Signaling Systems. The detector shall be a photoelectric type (models 2W- B, 4W-B) or a combination photoelectric/thermal (models 2WT-B, 4WT-B) with thermal sensor rated at 135 F (57.2 C). The detector shall include a mounting base for mounting to 3.5 (88.9 mm) and 4 (101.6 mm) octagonal, single-gang, and 4 (101.6 mm) square backboxes with a plaster ring, or directly mount to the ceiling using drywall anchors. Wiring connections shall be made by means of SEMS screws. The detector shall allow pre-wiring of the baseand the head shall be a plug-in type. The detector shall have a nominal sensitivity of 2.5%/foot (0.762%/meter) as measured in the UL smoke box. The detector shall be capable of automaticallyadjusting its sensitivity by means of drift compensation and smoothing algorithms. The detector shall provide dual-color LED indication which blinks to indicate power-up, normal standby, out-of-sensitivity, alarm, and freeze trouble (models 2WT-B, 4WT-B) conditions. When used in conjunction with the 2W-MOD module, two-wire moduels shall include a maintenance signal to indicate the need for maintenance at the alarm control panel, and shall provide a loop testing capability to verify the circuit without testing each detector individually. LED Modes Green LED Red LED Power Up Blink every 10 seconds Blink every 10 seconds Normal (Standby) Blink every 5 OFF seconds Out of Sensitivity OFF Blink every 5 seconds Freeze Trouble OFF Blink every 10 seconds Alarm OFF Solid ON Power up Sequence for LED Indication Condition Duration Initial LED Status Indication 80 Seconds Product Line Information 2W-B: Two-wire photoelectric smoke detector. C2W-BA: Same as 2W-B, ULC listing. 2WT-B: Two-wire photoelectric smoke detector with 135 F (57.2 C) fi xed thermal sensor. C2WT-BA: Same as 2WT-B, ULC listing. 4W-B: Four-wire photoelectric smoke detector. C4W-BA: Same as 4W-B, ULC listing. 4WT-B: Four-wire photoelectric smoke detector with 135 F (57.2 C) fi xed thermal sensor. C4WT-BA: Same as 4WT-B, ULC listing. ACCESSORIES: 2W-MOD2: Two-wire loop test/maintenance module. SENS-RDR: Sensitivity reader. A77-AB2: Retrofi t adapter bracket, 6.6 (167.7cm) diameter.
7 Dual Ac on Agent Release Sta on General The NBG-12LR is an Agent Release Station designed for use with Notifier Fire Alarm Control Panels with releasing capabilities and RP Series Releasing Systems. NBG-12LR Features Non-Coded, dual action operation Made with durable polycarbonate Optional surface backbox Applications The NBG-12LR is ideal for areas such as clean rooms and computer rooms where a chemical agent is used to extinguish a fire. Product Line Information NBG-12LRA: Agent Release station with abort swtich, release LED, Normal LED NBG-12LR: Dual action agent release station SBA-10: Surface backbox for NBG-12LRA SB-10: Surface backbox for NBG-12LR
8 Dual Ac on Agent Release Sta on NBG-12LR
9 Horns and Strobes General System Sensor SpectrAlert Advance selectable-output horns, strobes and horn/strobes are rich with features guaranteed to cut installation times and maximize profits. The SpectrAlert Advance series of notification appliances is designed to simplify your installations, with features such as: plug-in designs, instant feedback messages to ensure correct installation of individual devices, and eleven field-selectable candela settings for wall and ceiling strobes and horn/strobes. More specifically, when installing Advance products, first attach a universal mounting plate to a four-inch square, fourinch octagon, or double-gang junction box. The two-wire mounting plate attaches to a single-gang junction box. Then, connect the notification appliance circuit wiring to the SEMS terminals on the mounting plate. Finally, attach the horn, strobe, or horn/strobe to the mounting plate by inserting the product s tabs in the mounting plate s grooves. The device will rotate into position, locking the product s pins into the mounting plate s terminals. The device will temporarily hold in place with a catch until it is secured with a captured mounting screw. SpectrAlert Advance products allow you to choose: 12 or 24 volts. At 24 volts, 15, 15/75, 30, 75, 95, 110, 115, 135, 150, 177, or 185 candela by way of a rear-mounted slide switch and front viewing window. Horn tones and volume by way of a rotary switch. The SpectrAlert Advance series includes outdoor notification appliances. Outdoor strobes and horn/strobes (twowire and four-wire) are available for wall or ceiling. Outdoor horns are available for wall only. All System Sensor outdoor products are rated between 40 F and 151 F ( 40 C and 66 C) in wet or dry applications. Models available: Indoor wall-mount: horn, strobe, 2-wire horn/strobe, 4-wire horn/strobe. Indoor ceiling-mount: strobe, 2-wire horn/strobe, 4-wire horn/strobe. Outdoor wall-mount: horn, strobe, 2-wire horn/strobe, 4- wire horn/strobe. Outdoor ceiling-mount: strobe, 2-wire horn/strobe, 4-wire horn/strobe. Features Plug-in design. Same mounting plate for wall- and ceiling-mount units. Shorting spring on mounting plate for continuity check before installation. Captive mounting screw. Tamper-resistance capability. Field-selectable candela settings on wall and ceiling units: 15, 15/75, 30, 75, 95, 110, 115, 135, 150, 177, 185. Automatic selection of 12 or 24 volt operation at 15 and 15/ 75 candela. Outdoor wall and ceiling products. Outdoor products rated from 40 F and 151 F ( 40 C and 66 C). Outdoor products rainproof per UL50 (NEMA 3R) and weatherproof per NEMA 4X, IP56 Minimal intrusion into the backbox. Horn rated at 88+ dba at 16 volts. Rotary switch for tone selection. Three horn volume settings. Electrically compatible with existing SpectrAlert products. Agency Listings and Approvals The listings and approvals below apply to SpectrAlert Advance Selectable Output Notifi cation Devices. In some cases, certain modules may not be listed by certain approval agencies, or listing may be in process. Consult factory for latest listing status. UL Listed: S4011; S5512; S3593. ULC Listed: S4011; S5512 FM approved MEA: E CSFM: :0186; :0188; :0189; :0187.
10 Hornes and Strobes Engineering Specifications SpectrAlert Advance horns, strobes, and horn/strobes shall mount to a standard 4.0 x 4.0 x 1.5 (10.16 x x 3.81 cm) backbox, 4.0 (10.16 cm) octagonal backbox, or a doublegang backbox. Two-wire products shall also mount to a singlegang 2.0 x 4.0 x (5.08 x x cm) backbox. A universal mounting plate shall be used for mounting ceiling and wall products. The notification appliance circuit wiring shall terminate at the universal mounting plate. Also, SpectrAlert Advance products, when used with the Sync Circuit Module accessory, shall be powered from a non-coded notification appliance circuit output and shall operate on a nominal 12 or 24 volts. When used with the Sync Circuit Module, 12- volt rated notification appliance circuit outputs shall operate between 9 and 17.5 volts; 24-volt rated notification appliance circuit outputs shall operate between 17 and 33 volts. Indoor SpectrAlert Advance products shall operate between 32 F and 120 F (0 C and 49 C) from a regulated DC, or full-wave-rectified, unfiltered power supply. Strobes and horn/strobes shall have field-selectable candela settings including 15, 15/75, 30, 75, 95, 110, 115, 135, 150, 177, 185. STROBE The strobe shall be a System Sensor SpectrAlert Advance Model listed to UL 1971 and shall be approved for fi re protective service. The strobe shall be wired as a primary-signaling notifi cation appliance and comply with the Americans with Disabilities Act requirements for visible signaling appliances, fl ashing at 1 Hz over the strobe s entire operating voltage range. The strobe light shall consist of a xenon fl ash tube and associated lens/refl ector system. HORN/STROBE COMBINATION The horn/strobe shall be a System Sensor SpectrAlert Advance Model listed to UL 1971 and UL 464 and shall be approved for fire protective service. The horn/strobe shall be wired as a primary-signaling notifi cation appliance and comply with the Americans with Disabilities Act requirements for visible signaling appliances, fl ashing at 1 Hz over the strobe s entire operating voltage range. The strobe light shall consist of a xenon fl ash tube and associated lens/refl ector system. The horn shall have three audibility options and an option to switch between a Temporal 3 pattern and a Non-Temporal (continuous) pattern. These options are set by a multiple position switch. On four-wire products, the strobe shall be powered independently of the sounder. The horn on horn/strobe models shall operate on a coded or non-coded power supply. OUTDOOR PRODUCTS SpectrAlert Advance outdoor horns, strobes and horn/strobes shall be listed for outdoor use by UL and shall operate between 40 F and 151 F ( 40 C and 66 C). The products shall be listed for use with a System Sensor outdoor/weatherproof backbox with half-inch and three-fourths-inch conduit entries. SYNCHRONIZATION MODULE The module shall be a System Sensor Sync Circuit MDL3R or MDL3W listed to UL 464 and shall be approved for fire protective service. The module shall synchronize SpectrAlert strobes at 1 Hz and horns at Temporal 3. Also, while operating the strobes, the module shall silence the horns on horn/strobe models over a single pair of wires. The module shall mount to a x x ( x x cm) backbox. The module shall also control two Style Y (class B) circuits or one Style Z (Class A) circuit. The module shall synchronize multiple zones. Daisy-chaining two or more synchronization modules together will synchronize all the zones they control. The module shall not operate on a coded power supply. Operating Specifications Standard operating temperature: 32 F to 120 F (0 C to 49 C). K Series operating temperature: 40 F to 151 F ( 40 C to 66 C). Humidity range: 10% to 93% non-condensing (indoor products). Strobe fl ash rate: 1 fl ash per second. Nominal voltage: regulated 12 VDC/FWR or regulated 24 VDC/FWR. NOTE: Full Wave Rectifi ed (FWR) voltage is a non-regulated, time-varying power source that is used on some power supply and panel outputs. Operating voltage range: 8 V to 17.5 V (12 V nominal); or 16 V to 33 V (24 V nominal). NOTE: P, S, PC, and SC products will operate at 12 V nominal only for 15 cd and 15/75 cd. Input terminal wire gauge: 12 to 18 AWG (3.31 to mm²). Ceiling-mount dimensions (including lens): 6.8 diameter x 2.5 deep (17.3 cm diameter x 6.4 cm deep). Wall-mount dimensions (including lens): 5.6 H x 4.7 W x 2.5 D (14.2 cm H x 11.9 cm W x 6.4 cm D). Horn dimensions: 5.6 H x 4.7 W x 1.3 D (14.2 cm H x 11.9 cm W x 3.3 cm D).
MS-9600 Rev. 2/DACT-UD: Intelligent Addressable FACP with Optional 2nd Loop DF-52395:A A1-90 Addressable General The Fire Lite MS-9600 is a compact, cost-effective, intelligent addressable fire alarm control
Specification/ Data Sheet TRITON RP Agent Release Control Panel FEATURES Agent Release Control Panel designed specifically for suppression release operation with: Four initiating device circuits (IDCs)
SECTION 16721 FIRE ALARM SYSTEMS PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. The general provisions of the contract including General and Special Conditions and General Requirements shall apply to all work
Document 53192 3/2/2011 Rev: D1 P/N 53192:D1 ECN 11-159 Fire Alarm System Limitations While a fire alarm system may lower insurance rates, it is not a substitute for fire insurance! An automatic fire alarm
CONVENTIONAL FIRE ALARM CONTROL UNITS MR-2300 SERIES Fire Alarm Control Units Description Secutron s MR-2300 Series fire alarm control panels consist of six and twelve zone models which are equipped with
Notification Appliances L-Series, Indoor Strobes and Horn Strobes Indoor Selectable-Output Horns, Strobes and Horn Strobes for Wall Applications General The L-Series audible visible notification products
PRODUCT SPECIFICATION XR2400F Addressable FACP Addressable Fire Alarm Control Panel Description The DMP XR2400F Addressable Fire Alarm Control Panel is an expandable Fire Alarm Control with built-in DACT
Fire Alarm Control Panels MS-5UD Series MS-10UD Series Manual Document 52626 1/24/2012 Rev: C2 P/N 52626:C2 ECN 12-056 Fire Alarm System Limitations While a fire alarm system may lower insurance rates,
ECC-50/100(E) Emergency Command Center DF-60734:A9 C-200 General Fire Lite s ECC-50/100 and ECC-50/100E are multipurpose emergency voice evacuation panels for fire applications, mass notification applications,
s Data Sheet Fire Safety & Security Products SXL-EX Fire Alarm Control Panel Conventional Zone Fire Alarm Control Panel ARCHITECT AND ENGINEER SPECIFICATIONS Four (4) zones expandable to eight (8) zones
PN: 52626:A1 ECN 07-248 Fire Alarm Control Panels MS-5UD & MS-10UD Series Document #52626 5/11/07 Revision: A1 Fire Alarm System Limitations While a fire alarm system may lower insurance rates, it is not
R 12 Clintonville Road, Northford, CT 06472 Phone: (203) 484-7161 FAX: (203) 484-7118 Instruction Manual for the MS-4012/4024 and CMS-4012/4024 Fire Alarm Control Panels Document 15586 5/11/93 Revision:
ACC-25/50ZST Zoned System Voice with Telephone Evacuation Control Panel General The AUDIO COMMAND CENTER 25/50 Zone System with FireFighters Telephone (ACC-25/50ZST) is a state-of-the-art Emergency Voice
CHEETAH XI INTELLIGENT SUPPRESSION CONTROL SYSTEM DESCRIPTION Fike s Cheetah Xi (P/N 10-068) is a state-of-the-art true intelligent digital peer-topeer modular suppression control system. It is ideal for
TrueAlert Notification Appliances UL Listed; FM, CSFM and MEA (NYC) Approved* Non-Addressable Audible/Visible Notification Appliances with SmartSync Operation of Strobes and Horns Features Wall mount audible/visible
SpectrAlert Advance Description System Sensor SpectrAlert Advance offers a variety of devices designed for mass notification, including plain devices for non-fire applications, amber lens strobes and speaker
NBG-12LR and NBG-12LRA Dual-Action Agent Release Stations DN-6840:B F-710 Releasing Panels General The NBG-12LR and NBG-12LRA are Agent Release Stations designed for use with NOTIFIER Fire Alarm Control
March 30, 2000 Section: Audio/Visual Devices G-250 SpectrAlert Series Horns, Strobes, and Horn/Strobes GENERAL System Sensor SpectrAlert Series strobes, horns, and combination horn/strobes are UL listed
Fire Alarm Control Panels MS-2 & MS-4 MS-2E & MS-4E Instruction Manual Document 51512 8/6/2014 Rev: G3 P/N 51512:G3 ECN 14-523 Fire Alarm & Emergency Communication System Limitations While a life safety
AL600ULADA NAC Power Extender Installation Guide Rev. 122000 AL600ULADA - NAC Power Extender Overview: The Altronix AL600ULADA is an extremely cost effective 6.5 amp voltage regulated remote power supply/battery
Fire Alarm Control Panels MS-5UD Series MS-10UD Series Manual Document 52626 6/30/2009 Rev: B1 P/N 52626:B1 ECN 09-432 Fire Alarm System Limitations While a fire alarm system may lower insurance rates,
UL, ULC Approved* LifeAlarm Fire Alarm Controls 4009 IDNet NAC Extender for Control with IDNet Communications or Conventional NACs Features Provides additional notification appliance circuit (NAC) capacity
FireSeeker Fire Alarm Control Panel Model FS-250 Installation, Operation and Maintenance Manual P/N 315-049353-1 Siemens Building Technologies Fire Safety TABLE OF CONTENTS INTRODUCTION... 1 CONTROL PANEL
Genesis Low Frequency (520 Hz) Horn-Strobe Installation Sheet Table 1: Models Description Low frequency (520 Hz) horn, white housing, no FIRE marking, standard output clear strobe light Low frequency (520
Fire Safety FireSeeker Fire Alarm Control Panel Model FS-100 Installation, Operation, and Maintenance Manual Siemens Building Technologies, Inc. Siemens Building Technologies, Ltd. 8 Fernwood Road 2 Kenview
Intelligent Analog/ Fire Alarm/Voice Integration Systems IntelliKnight TM Series CONVENTIONAL FIRE ALARM CONTROL PANELS SK-Conventional Series 2- to 30-Zone Fire Alarm Control Panels (FACPs) Whether your
12 Clintonville Road Northford, CT 06472 (203) 484-7161 FAX: (203) 484-7118 LDM Series Lamp Driver Modules For Graphic Annunciation and Control Used with the System 500, System 5000, AM2020/AFP1010 and
AEGIS Conventional Fire Alarm-Suppression Control Unit FEATURES Agency Approvals FM Approved FM Approved to ANSI/UL 864, 9th edition FM Approved to ULC-S527-99 Other domestic U.S. approvals/listings pending/
UL, ULC, CSFM Listed; FM, NYC Fire Dept Approved* 4007ES Fire Control Panels 4007ES Hybrid, Fire Detection and Control Panel with Addressable and/or Conventional Initiation Features Satisfies a variety
Data/ Specification Sheet AUTOPULSE IQ-318 INTELLIGENT ADDRESSABLE FIRE ALARM SYSTEM GENERAL The AUTOPULSE IQ-318 intelligent Fire Alarm Control Panel is part of the AUTOPULSE Series of Fire Alarm Controls
GE Security EST Life Safety & ommunications onventional Small Building Solutions Overview The FireShield Plus fire alarm family consists of 3, 5 and 10 zone conventional fire alarm s, an integrated DAT/Dialer,
Installation Instructions Notice Addressable NAC Output Module D327A These instructions cover the installation of the D327A Addressable NAC Output Module in an analog system controlled by a Bosch D8024,
CFP-105 Fire Alarm Control Panel Installation Manual Version 1.0 WARNING: This manual contains information on limitations regarding product use and function and information on the limitations as to liability
Conventional Fire Alarm Control Panel CFP-2410B Programming, Installation, Maintenance and Operating Manual Document 50974 2/18/04 Rev: B P/N 50974:B ECN 02-253 Fire Alarm System Limitations While a fire
ORENA BRAND CONVENTIONAL (ORENA Brand) CE ODH02E 2 Zone Conventional Control Panel Zone Capacity: can be connected with 20 fire detectors and infinite manual call points Using environment: Temperature:
s Data Sheet Fire Safety & Security Products Cerberus TM PRO Fire Safety System A comprehensive fire-protection system Standard 50-point, 252-point and 504-point-capacity systems Remote viewing for the
OSU PROJECT NO. 30-04-15 PAGE 1 PART 1 GENERAL 1.1 WORK INCLUDED A. Provide all labor, materials, and equipment required to provide a complete and operating system of manual and automatic detection devices,
R IPS CARBO STEEL PIPE FIRE PROTECTIO PRODUCTS Electric Release Panel Wiring Tips 30.4 VICTAULIC IS A ISO 900 CERTIFIED COMPAY Model PDRP-00 Releasing Panels are compact single enclosure units containing
Edwards Signaling atalog u Fire Alarm ontrol Panels E-FS onventional Fire Alarm ontrol Panels Overview The E-FS fire alarm family consists of 3, 5 and 10 zone conventional fire alarm s, an integrated DAT/Dialer,
Technical Service Note Detection Systems, Inc. Fairport, New York 14450-9199 Technical Service (800) 374-7454 Sales: (800) 289-0096 and (585) 223-4060 Fax: (585) 223-9180 Concerns: Affects: Dated: June
January 16, 2014 Release Control Panel 290a 1. Description The Viking VFR400 is a microprocessor based releasing control panel for use on preaction, deluge, Surefire, Firecycle multicycle sprinkler systems,
Fire Alarm Control Panel & Fire Alarm Annunciator Panel Notify all building occupants that testing will be conducted. Fire alarm contractor shall have personnel with 2-way radios at the fire alarm control
One Fire-Lite Place Northford, CT 06472 Phone: (203) 484-7161 FAX: (203) 484-7118 FCPS-24F FIRE ALARM FIELD CHARGER/POWER SUPPLY FOR FIRE PROTECTION/SIGNALING SERVICE FCPS-24F/FCPS-24FE Field Charger/Power
INTELLIGENT FIRE ALARM CONTROL UNITS MMX-2003-12NDS Intelligent Network Fire Alarm Control Unit Description Secutron s MMX-2003-12NDS Network Fire Alarm Control Unit offers modular components to meet a
RANGER 8600 DOWNLOADABLE CONTROL COMMUNICATOR INSTALLATION MANUAL TABLE OF CONTENTS GENERAL DESCRIPTION... 2 STANDARD AND OPTIONAL PARTS LIST... 2 PARTS DIAGRAM... 3 TERMINAL DRAWING AND SPECIAL NOTES...
FA-1000 SERIES Microprocessor-Based Fire Alarm Control Panel Installation and Operation Manual LT-600 Rev. 19 May 2017 Table of Contents 1.0 Introduction 8 1.1 About this Manual... 8 1.2 About the FA-1000...
HP101U Conventional Fire Alarm Control Panel Installation And Operation Manual NOTICE All information, documentation, and specifications contained in this manual are subject to change without prior notice
s Desigo Fire Safety System A comprehensive fire-protection system Standard 50-point, 252-point and 504-point-capacity systems Remote viewing for the 252- point and 504-point systems One (1) or (2) two-heightunit
MANUAL RELEASE - IDNET IN + +IDNET IN - RED NA C+ N A C - COIL SUPERVISION MODULE ( 2 AMP) 28-946 INSTALLATION INSTRUCTIONS 574-437 REV YEL MA IN T A IN /4 "S E P A R A T IO N BETW EEN POW ER LIMITED (
PN: 52646:B ECN 08-188 Fire Alarm Control Panel MS-9600LS/MS-9600LSE MS-9600UDLS/MS-9600UDLSE MS-9600LSC IMPORTANT! The SLC Wiring Manual Document #51309 must be referenced in addition to this manual when
Installation Guide for AL600ULM Multi-Output Access Control Power Supply Charger Rev. 091800 1 AL600ULM - Multi-Output Access Control Power Supply/Charger Overview: The AL600ULM multi-output access control
Cerberus PRO Marine Fire and Detection Equipment s FH-2071-UM, BP-62 and USCG-HPLATE Cerberus PRO Fire Safety Products ARCHITECT AND ENGINEER SPECIFICATIONS Marine equipment is used with Cerberus PRO 252-point
PN: 52750:A ECN 05-680 Fire Alarm Control Panel MS-9200UDLS MS-9200UDLSE IMPORTANT! The SLC Manual Document #51309 must be referenced in addition to this manual when installing or servicing the Fire Alarm
UL, ULC, CSFM Listed; FM, NYC Fire Dept Approved* Features Flexible standard combination of addressable initiation and addressable notification 4.3 (109 mm) Diagonal color touchscreen display: Convenient
Cautions and Warnings DO NOT INSTALL ANY SIMPLEX PRODUCT THAT APPEARS DAMAGED. Upon unpacking your Simplex product, inspect the contents of the carton for shipping damage. If damage is apparent, immediately
IFP-2000 Farenhyt PHD Power Supplies Module 4 Course Objectives At the end of this course you will be able to: Explain the advantages of Conventional Distributed power supplies Explain the advantages of
Installation Guide for AL400ULM Multi-Output Access Control Power Supply Charger R AL400ULM - Multi-Output Access Control Power Supply/Charger Rev. 072500 Overview: The AL400ULM multi-output access control
Voice Evacuation E3 Series Broadband System Intelligent, Networked, Multi-Channel Fire Alarm Control and Emergency Voice Evacuation System General The, E3 Series Broadband System is a modular design and
HARRINGTON SIGNAL INC. FIRE ALARM Harrington Signal HS-3100/3200 Fire Alarm Control Unit Installation Manual Revision 2 January 2009 Document # LT-2000HAR Table of Contents 1.0 Technical Information...
System Sensor 3825 Ohio Avenue St. Charles, IL 60174 1-800-SENSOR2 Fax: 630-377-6495 PDRP1002.CD The PDRP-1002/PDRP-1002E Agent Release Control System Manual Document 51135 A 03/11/99 Revision: I56-1358-00
LiftMaster 300 Windsor Drive Oak Brook, IL 60523 LiftMaster.com O W N E R S M A N U A L MODELS LM21AFCB LM21AFCBVB B ADVANCE FIRE CONTROL RELEASE DEVICE FM APPROVED TABLE OF CONTENTS INTRODUCTION General
HCA Series Conventional Fire Alarm System (HCA-2, HCA-2D, HCA-4, HCA-4D, HCA-8, HCA-8D) Installation and Operation Manual Hochiki America Corporation 7051 Village Drive, Suite 100 Buena Park, CA90621-2268
RP-1002M AGENT RELEASE CONTROL PANEL AC POWER SYSTEM ALARM RELEASE SUPERVISORY SYSTEM TROUBLE CIRCUIT TROUBLE ALARM SILENCED POWER TROUBLE ZONE 1 ZONE 2 ABORT MANUAUL RELEASE TONE SILENCE ALARM SILENCE
Oxygen (O) Single-Point Gas Detection System DESCRIPTION Wall-mounted gas monitor with built-in oxygen (O) sensor, accepts one analog remote device such as a secondary gas sensor, temperature or humidity
FX-3500 Fire Alarm Control Panel Installation and Operation Manual Table of Contents 1.0 Industry Canada and FCC Notice 7 1.1 Notice for all FX-3500 Series Built-In UDACTs Sold in Canada... 7 1.2 Industry
Vigilant Catalog Small Building Fire Alarm Solutions VS1 Intelligent Life Safety System Overview The Vigilant VS1 intelligent life safety system offers the speed of high-end intelligent processing in a
VALOUR COMMUNITY CENTRE FIRE ALARM SYSTEM Section 28 00 00 GYMNASIUM ADDITION & RENOVATION Page 1 of 3 28 00 00 FIRE ALARM SYSTEM 1.1 GENERAL REQUIREMENTS 1.2 SCOPE 1. The specification covering the General