1 ELECTRONIC ENGINEERING LTD. PowerWave zone Control panel Communicator Users Operating and Programming Guide Version 6.20 P/N Rev. B N.A July 2002
2 Contents Introduction...4 Meet the Crow Alarm Control System... 4 Typical Alarm System Configuration... 4 Keypad Description...5 Function Keys... 5 Alphanumeric Keys... 5 Audible Signals... 6 Indicators... 6 Zone and Status indicators LEDs Partitions indicators LEDs A, B,C... 6 Armed indicator, Memory indicator, Bypass indicator... 6 Program indicator, Aux indicator, Mains indicator... 6 Tamper indicator, Battery indicator, Line indicator, Control indicator... 6 Summary of Functions... 6 Operation...8 How to Arm the System before Exit... 8 How to Arm the System when Staying Home... 9 How to Arm Partitions... 9 How to Bypass Zones...10 How to use Chime (If enable by Installer)...11 Emergency Alerts...10 Generate Threat or Duress...11 How to Read System Messages...11 How to Read Trouble Messages
3 How to Display Events from Memory...12 How to Control Outputs and Devices...14 How to Get into to User Program/Client Mode...14 How to Change or Add Codes...15 How to Change Master Code...15 How to Add or Change User Code...15 How to Delete User Code...16 How to Add or Change Telephone Numbers...16 How to set Time and Date...16 How to operate the access control output...17 How to start Walk test Mode...17 Warranty
4 Introduction Meet the Crow Alarm Control System Thank you for choosing to protect your premises with a PowerWave-16 (PW16) of Crow Electronic Engineering Ltd. Power Wave of Crow Electronic Engineering Ltd. is a highly advanced, multifunction alarm control system, designed to flawlessly manage your security system at home or at business, protects you against burglary and supports the operation of electronic devices. The PW16 has many incredible program options and additional accessories that can enhance the standard features of the panel from simple Home Automation to Wireless control and Voice Prompted Telephone control. Please ask your installer to find out more about these powerful features. You can phone your home to check or change the status of any output using the keys on your phone. Arm or disarm the whole house or just one area, all with your own voice confirming your selections. Imagine turning on the spa before leaving work so it is hot when you get in the door. The under-floor heating has just automatically switched on using the on board timer and you have just opened the rollerdoor and disarmed the garage from your cell phone so the white ware repairman can work on your washer. The controller will support a 16 LED keypad or the more sophisticated LCD (liquid Crystal Display) keypad. It also has a comprehensive alarm event memory that stores all of the controller activity with the time and date. Typical Alarm System Configuration The protected premises can be divided up to 16 zones, as defined by the installation scheme. The protected area can be grouped into 3 separate partitions (A, B, C). The system can be grouped for User s convenience to separate, in a business environment, the offices from the warehouse area, or in a private residence, the different areas in the home, e.g., separate downstairs living area, detached garage, etc. Each zone can react differently to various events, to generate an alarm or activate a device. The system can be armed in two different modes: 1) Arm the protected areas are entirely vacated 2) Stay people and pets populate the protected areas. The User who has access to the keypad's control features, can change the settings. The system can be accessed via multiple keypads (each located at a different site). Up to 8 keypads can be integrated into the system. Access levels and Users access codes are detailed below. 4
5 Keypad Description The LED Keypad shows all the information required to operate the system. The User communicates with the alarm system via the keypad. The Keypad displays continuous information about the status of the alarm system, and enables the User to operate the system in different modes, change settings and program Users' access codes. The keypad also collects and records events to be displayed afterward on request, to overview system activities, and to analyze system performance for diagnostics. Function Keys These keys are used to arm the system, enter Telephones to alter system settings, or scroll through the history events. ARM, STAY, BYPASS, PROGRAM, CONTROL, MEMORY, PANIC, ENTER Alphanumeric Keys These keys are used to enter codes, Initiate Emergency or for programming. 5
6 Audible Signals The keypad emits signals (beeps) in response to User activities. These signals are listed in Table. Table: List of Audible Signals Sound Sequence Description Short beep Once only A key in the keypad has been pressed 3 short beeps Once only Operation carried out successfully Long beep Once only Illegal operation, or wrong key pressed Slow beeping Indicators Through the Exit or Entry delay time Exit or entry delay warning when arming the system indicates that you must exit the protected area, also Entry delay warning when entering via the entry zone, to disarm the system. There are 30 LEDs indicators show the status of the system. Zone and Status indicators LEDs 1-16 Partitions indicators LEDs A, B, C Armed indicator, Memory indicator, Bypass indicator Program indicator, Aux indicator, Mains indicator Tamper indicator, Battery indicator, Line indicator, Control indicator Summary of Functions The system's main functions are listed in table Function Keys Description Notes Full or Partition Arm C C O D E C ENTER Initiates full arm Full Arm C ARM Initiates full arm Only if enabled by installer Disarm during exit C ARM Disarms the system during exit delay Disarm C C O D E C ENTER Disarms the system Only when slow beeping is emitted Stopping Alarms 6
7 Function Keys Description Notes Arm Stay C STAY C C O D E C ENTER Initiates partial alarm when the user is home Only if enabled by installer Arm Stay C STAY Initiates partial alarm when the user is home Disarm Stay C C O D E C ENTER Disarms the system Disarm Stay C STAY Disarms the system Bypass C BYPASS C Zone # C ENTER Bypasses a zone(s) Repeats the procedure to un-bypass zones Initiate Panic C PANIC Activates panic alert Initiate Panic C Initiate Medical C Initiate Fire Alarm C Activates emergency alert Activates emergency alert Activates emergency alert Only if enabled by installer Only if enabled by installer Only if enabled by installer Memory C MEMORY Initiates display of events from memory. <ENTER> cancels memory readout Chime Enable/disable C CONTROL C PROGRAM Enable or disable chime function Displays events, and automatically scrolls to the next event every 2.5 sec. (Use <MEMORY> key to scroll up manually) Only if enabled by installer Control C CONTROL C Device# C ENTER Activates or deactivates outputs and devices Press <Control> for 2 seconds Change or Add Users' code C PROGRAM C M CODE C ENTER Activates program mode to add or change Users' codes For details see page 12 Note: If you started an operation incorrectly, press <ENTER> to exit and return to the previous mode. 7
8 Operation How to Arm the System before Exit Preparing the System for Arming Verify that all zone indicators are off, when all zones are closed (all doors, exits and windows are closed and motion in the protected area is restricted or bypassed), the system is ready to be armed. If one or more zone indicators are illuminated, it displays the open zones. Close open zones, or bypass them. Bypass any zone you cannot close, <Bypass> indicator flashes indicating bypassed zone(s). For details see page 9. Note: Bypassed zones are not protected. Arming the System Before leaving premises the system has to be armed. Arming the alarm system will turn on all detectors in the partition /s being armed. Enter user code and then <ENTER> to arm the system. There is a exit delay prior to the system being armed. During this delay time, a slow beeping is heard to indicate that the system is not armed yet and reminds you to leave the protected area. The A,B or C indicator lights up to indicate that the system is armed. (The indicators may go out few seconds after exit delay expired, depending on the installer's setting). If you must disarm the system during the exit delay, press <ARM>. Quick Arm (When enabled by the installer) Press <ARM> to arm the system. The A, B or C indicator lights up to indicate that the system is armed. During exit delay time, a slow beeping is heard reminds you to leave the protected area. Disarming the System Enter User s code and press <ENTER>. The A, B or C indicator goes off to indicate that the system is disarmed. Stopping Resetting Alarms In case of an alarm condition Enter User s code and press <ENTER> to stop alarm any time, and turn off any audible sirens. 8
9 How to Arm the System when Staying Home Arming the System in Stay Mode This type of arming is used when people are present within the protected area. At nighttime, when the family is about to retire, perimeter zones are protected, but not the interior zones. Consequently, interior movements will be ignored by the system. To arm Stay mode press <STAY>, enter user code, and then <ENTER>. The A, B or C indicator flashes to indicate that the system is armed in stay mode. Quick Stay When enabled by the installer, press <STAY> to arm the system. During exit delay you can leave the premises. If you wish to stay or that no one will enter the protected premises, you may cancel the Entry/exit delay by pressing the <ENTER> key. The slow beeping stops and the system is immediately armed. The A, B or C indicator flashes to indicate that the system is armed in stay mode. (The indicators may go out a few seconds after exit delay expired, depending on the installer's setting). Disarming the System Enter user s code and press <ENTER>, or press <STAY> if enabled by installer. The A, B or C indicator goes off to indicate that the system is disarmed. How to Arm Partitions The protected area can be grouped into 3 separate partitions (A, B, C). The system can be grouped for User s convenience to separate, in a business environment, the offices from the warehouse area, or in a private residence, the different areas in the home, e.g., separate downstairs living area, detached garage, etc. To arm partition A enter user code for partition A To arm partition B enter user code for partition B To arm partition C enter user code for partition C Note: to arming partition with code see page 8 How to arm the system before exit During exit delay you can leave premises. At the end of the procedure the A,B or C indicator lights up to indicate that the partition A or/and B or C is armed. (The indicators may go out after a few seconds, depending on the installer's setting). To disarm partition, see "Disarming the System". 9
10 How to Bypass Zones Bypass any zone that cannot be closed. You can bypass selected zones prior to arming. It is also used to temporarily exclude a faulty zone from service, which requires repair. To bypass a selected zone, press <BYPASS>, Bypass indicator lights up to indicate that the system is in bypass mode. Enter the zone number (e.g. 01, 05, 12) one or more zones, the zone LED indicators lights up to indicate that the zone is bypassed, following press <ENTER>, the Bypass LED flashes to indicate zone(s) bypassed. While in the Bypass mode it is possible to bypass more than one zone, press <BYPASS>, Bypass indicator lights up to indicate that the system is in bypass mode, Add the zone number (e.g. 03) one or more zones, the zone LED indicators lights up to indicate that the zone is bypassed, following press <ENTER>, the Bypass LED flashes to indicate zone(s) bypassed. To un-bypass zones, press <BYPASS>, enter zone number (e.g.07,13),the zone LED indicators goes off to indicate that the zone is un bypassed and <ENTER>. Note: Disarming automatically un-bypasses all zones. Emergency Alerts This three special key s function is best programmed by your installer to suit your individual situation. Most commonly it is used in a panic situation. These are a PANIC, FIRE, and MEDICAL alarm. When using the LED keypad the Panic alarm can be generated by either the single Panic button or by the simultaneous operation of two buttons. Pressing two buttons simultaneously generates the Fire and Medical alarms How to initiate Panic Press the <PANIC> or Press simultaneously <1>and <3>. How to initiate Medical Alarm Press simultaneously <7> and <9>. How to initiate Fire Alarm Press simultaneously<4> and <6>. 10
11 How to use Chime (If enable by Installer) A Chime (Day zone) is a detector that can be part armed while you are at home but working in another part of the building. It can be programmed to operate a buzzer or light to let you know you have a visitor. To disable the Day (chime) zone, press <CONTROL> and <PROGRAM>, Control LED indicator lights up to indicate that Chime is disabled. To enable Chime mode press <CONTROL> and <PROGRAM> Control LED goes off to indicate that Chime is active. Generate Threat or Duress If you are compelled to disarm the system under threat, you must enter the duress digit before the user s code to activate the automatic dialer. The duress digit shifts up your usual code by one digit. If your code is 345 and 8 is your duress digit, than entering 8345 will modify your code. The modified duress code will disarm the system in a normal way, but at the same time will activate the dialer silently to report a duress event without arousing suspicion. (For details ask installer.) How to Read System Messages When viewing the memory events at the keypad by pressing the <MEMORY>,the first thing that will always be displayed is the system messages. LED # 1 Battery Low LED # 5 Wireless Keyfob Battery Low LED # 2 Mains Failure LED # 6 Supervised Detector Failure LED # 3 Telephone Line Failure LED # 7 Zone Inactivity Timeout LED # 4 Wireless Detector Battery Low LED # 8 Dialer Kiss-off Failure If the system led turns ON but no other Zone LED s are ON at the same time, this means that there are no current system alarms. If a zone LED and LED s are ON then this indicates system alarms that have not yet cleared. The LED s 1-8 are pre-defined as to what system alarm they will display. These system alarm indications are shown in the table below. Following the display of current system alarms the panel will then sequence through the 255 historical memory events starting at the most recent event. The second table shows the alarm events that can be displayed in memory mode and what indicators are used to show them. 11
12 How to Read Trouble Messages Any failure or abnormal events that may occur are indicated by trouble messages, and the Trouble indicator is lit. Press <MEMORY> to read out messages and other events stored in memory. How to Display Events from Memory The system memory stores the last events. Press <MEMORY> to display list of events. Following the display of current system alarms the panel will then sequence through the 255 historical memory events starting at the most recent event. The second table shows the alarm events that can be displayed in memory mode and what indicators are used to show them. The system will display the last event and automatically scroll to the next one every 2.5 seconds, and a beep is emitted. Use the arrow keys to scroll up manually. Wait until all messages are displayed, or press <ENTER> to cancel memory readout. EVENT TYPE DEVICE INDICATOR STATUS ACTIVATION Zones 1-16 LED's 1-16 BYPASS Zones 1-16 Bypass DETECTOR TAMPER (SHORT CIRCUIT) DETECTOR TAMPER (OPEN CIRCUIT) Zones 1-8 Zones 9-16 LED's 1-16 TAMPER LED's 1-8 TAMPER LED's 9-16 WRONG CODE ALARM Code at Keypad # TAMPER LED's 1-8 CABINET TAMPER Cabinet or Siren TAMPER KEYPAD TAMPER SWITCH Tamper alarm at keypad TAMPER LED's 1-8 LOW BATTERY Controller Battery BATTERY MAINS FAILURE Controller Mains Supply MAINS FUSE FAILURE F1 or F2 Controller on-board MAINS Fuses 12
13 WIRELESS ZONE LOW BATTERY Wireless Zone 1-16 BATTERY LED's 1-16 KEYFOB LOW BATTERY Wireless Keyfob User 1-20 BATTERY LED's 1-16 PANIC BUTTON (or BUTTONS 1&3 PRESSED TOGETHER) Keypad Panic At keypad # LINE LED's 1-8 FIRE ALARM (BUTTONS 4&6 PRESSED TOGETHER) Keypad Fire LINE CONTROL MEDICAL ALARM (BUTTONS 7&9 PRESSED TOGETHER) Keypad Medical LINE BYPASS ARMED A Area A is Armed AREA A ARMED B Area B is Armed AREA B ARMED C Area C is Armed AREA C STAY MODE A STAY MODE B STAY MODE C DURESS ALARM SUPERVISED WIRELESS ALARM Area A STAY Mode ON Area B STAY Mode ON Area C STAY Mode ON Duress Alarm At keypad # Supervised Wireless Passive Infra-Red AREA A AREA B AREA C TAMPER LINE LED s 1-8 Bypass TAMPER LED s 1-16 ZONE INACTIVITY ALARM Zones 1-16 LED s 1-16 TAMPER CONTROL TELEPHONE LINE FAILURE Phone Line Failure LINE EXCESSIVE RE-TRIES Panel Dialler LINE 13 LED1
14 FAILURE TO GET A KISSOFF Panel Dialler LINE LED2 WALKTEST MODE Manual walk-test mode MAINS BATTERY LINE LED s 1-16 How to Control Outputs and Devices The keypad enables control of external devices, such as an air-conditioner or heater. To activate or halt a device, press <CONTROL>, Control LED lights up steady, press the number of the device, up to 8 different devices can be controlled via the keypad,then press <ENTER> to activate or deactivate the selected device. To check what outputs are ON simply press the <CONTROL> key, LED s corresponding to device ON lights up.press <ENTER> to return to normal mode. How to Get into to User Program/Client Mode There are 2 levels of program mode, CLIENT mode and INSTALLER mode. Normally the installer will give you access to the CLIENT mode so you can add, delete, or change the user codes. If you request it your installer can provide you with access to the INSTALLER mode as well. To get into CLIENT mode provided the system is NOT armed Press <PROGRAM> enter Master code and <ENTER>. The Program indicator lights up to indicate that the system is in User programming mode. If you get a single long beep at this point and the Program LED doesn t turn on, it means your code cannot access Program mode. How to exit program mode To exit out of program mode press <PROGRAM> and <ENTER>. The Program indicator goes off to indicate that the system is not in User programming mode. 14
15 How to Change or Add Codes About Master code and User code The factory default master code (123) is intended as a preliminary control of the alarm system. After PowerWave is installed and put into service, the code can be changed to any code known to the Master user. The Master user can define up to 49 user codes. To limit access rights, the holder of the Master code can ask the installer to define several User profiles. Access rights are listed below: - User code has Area A and/or B or C access - User code can arm and/or disarm arm an area - User code can arm and/or disarm arm an area in Stay mode - User code can change its code - User code can change user s code - User code can Operate control Functions - User code can change dialler telephone numbers - User code can alter the real time clock - User can answer an incoming call and start up/down load - User can allow access to installer program mode from client mode. - Initiate Walk-test mode. How to Change Master Code While in CLIENT mode, Press <PROGRAM> and 1 to change Master code press <ENTER>, the code digit will be flashed back to you. Use the numeric keyboard to enter your new Master code. The code can hold any combination of 1 to 6 digits. It is recommended using a multi-digit code.. Press <ENTER> to save your new code, the new code will be flashed to you and 3 short beeps to indicate correct entry or 1 long beep if not accepted. Press <PROG> and <ENTER> exit user Code Program mode. How to Add or Change User Code While in CLIENT mode, press <PROGRAM> and the User number (2 to 50) to add or change the code, press <ENTER>. If there is an existing code already, it will be flashed back to you. Use the numeric keyboard to enter the new code. The code can hold any combination of 1 to 6 digits. Entering the new code will delete the old code. Press <ENTER> to save your new code, the new code will be flashed to you and 3 short beeps. Repeat the procedure for all users. Press <PROG> and <ENTER> to exit Local Program mode. 15
16 How to Delete User Code In client mode, press <PROGRAM> and the User number (2 to 50) you intend to delete, press <ENTER>. The code will be flashed back to you. Press <BYPASS> to delete User code. Press <ENTER> to save the change. Press <PROG> and <ENTER> exit program mode. How to Add or Change Telephone Numbers Your panel will accept up to 6 phone numbers with a total of 16 digits. Your panel can be can be programmed to dial all or any of these depending on the event which has occurred.(the six phone numbers are at program address 331 through to 336). While in CLIENT mode, key in the following sequence <PROGRAM> <331> <ENTER> (The address for telephone number 1), The existing number will be flashed out at the Keypad then enter <NEW TELEPHONE #> <ENTER> The new numbers will be flashed back to confirm acceptance. At any time you can enter in the address for the telephone number just to view the currently programmed value then press the <PROGRAM> button to move on to another address. Note: Address 331 = PH # 1, 332 = PH# 2 to 336 = PH# 6. (Note: on the LED keypad 0 is indicated by LED A and 9 by LED B ) How to set Time and Date The alarm system has an internal clock that may be used to automatically Arm or Disarm the alarm or turn Outputs On or off. It is also used to identify when events occurred in memory via the LCD keypad. Should you need to change the Time & Date it must be done from CLIENT mode. To change the Time & Date press Press <PROGRAM> <823> <ENTER> <1-7> <ENTER> Where 1-7 = the current day (1=Sun, 2 = Mon to 7 = Sat) Press <PROGRAM> <824> <ENTER> <HHMM> <ENTER> Where HH = Hour in 24 Hour Format and MM = Minutes Press <PROGRAM> <825> <ENTER> <1-31> <ENTER> Where 1-31 = the current date Press <PROGRAM> <826> <ENTER> <1-12> <ENTER> Where 1-12 = the current month Press <PROGRAM> <827> <ENTER> <YY> <ENTER> Where YY = current year, e.g. 02=
17 How to operate the access control output If the alarm system has been set up to allow control of an electric door lock, you can activate the door release function as follows; Press <CONTROL> or Press <CONTROL> enter CODE then <ENTER> The Control LED will lights up while the lock is active and turn off as soon as power is removed from the lock. The Access Control function can either be a single button operation or restricted to requiring a valid User code entry. Both options are shown above. Please consult your installer as to what option may be programmed. How to start Walk test Mode While in CLIENT mode a User with the proper authority can start walk-test mode. This special mode latches the alarm signals from detectors at the keypad initiating the test so that one person can trigger every detector connected to the alarm then return to the keypad to verify operation. On terminating Walk-test mode the test results are put into the memory buffer so they can be viewed at a later time. To start Walk-test mode while in CLIENT mode press <PROGRAM> <836> <ENTER> The keypad buzzer will beep at 1-second intervals Next trigger every detector connected to the panel then return to the keypad and all of the zones that were triggered will be displayed at the keypad. To terminate Walk-test mode press <ENTER> The keypad will stop beeping and automatically exit CLIENT mode. How to Answer an in-coming call From time to time your installer may need to access the alarm from a remote PC to make changes to your programming and for security reasons they may have configured the alarm so that an authorized person on-site is required to make the alarm system answer the in-coming call. This option is only available in CLIENT mode. To answer an In-coming Call press <PROGRAM> <835> <ENTER> Provided the line connected to the alarm was ringing at the time the panel will now answer the call and allow a remote PC connection. 17
18 How Remote Telephone control works Another powerful feature available from your alarm is Telephone Control. This feature is a remote control facility which allows valid users to access the panel via a standard touch tone telephone and check or change the Arm/Disarm status of each of the areas, operate each of the eight outputs or turn on an optional Microphone. The Telephone Control feature is only available on panels fitted with a Voice or DTMF board. The Voice board provides voice prompts to guide you through Telephone control operations whereas the DTMF board provides tones (one Long Tone for ON or three short beeps for OFF). Please talk to your installer to find out if all or any of these options are available on your alarm. To perform any of the Telephone Control features you must first ring the phone number, which the panel is connected to. The panel may be set up to answer after a specific number of rings of it may be set-up to use a fax defeat option (ring once, hang up and call back within 30sec). Either way, when you ring the phone number and the panel answers the call, the first thing you will hear over the phone is a burst of modem tone for two seconds. After this tone has stopped you must enter the access code, which is associated with the Telephone menu option you wish to access. Remember, the code you enter will determine which menu option you access. If you miss the pause, the panel will repeat the modem tone and then again pause for 5 seconds looking for your access code. This process will be repeated 4 times before hanging up if no valid code is received. When entering codes or other information in Telephone Control the "#" key acts as a "Clear" button. When you have entered the required 4-digit access code the panel will reply with the status message associated with the Telephone Control function you have accessed. For example, lets say we have a code of 2045 to allow Arming & Disarming of Area A. Once the code 2045 has been received the panel checks the current status of Area A and replies with the pre-programmed voice message relating to that status e.g. if Area A is Armed then the Armed message will be sent, if Disarmed then the Disarmed message will be sent. If only the DTMF board is fitted, the voice message is substituted with a long beep if Area A is Armed, and three short beeps if it is disarmed. Once the status message has informed you of the actual state, you can use the "*" key to toggle the option on & off or Arm and Disarm, e.g. in our example above, code 2045 accesses Area "A" arming or disarming. Assuming the status message we received was "Area A alarm is Armed" If we press the "*" key, Area "A" will be Disarmed and we would receive a status message "Area A alarm is Disarmed" (or whatever message is programmed by the installer) While you are on-line with the panel you can move between menu options by entering the code of the option you want to control. Assuming there was a code of 4321 programmed to control outputs. After having used code 2045 to control the Arm/Disarm status of Area A we first press the # button to reset all previous entries. Then we can enter the digits (that is 4321 as the code to control outputs and 5 to select output #5). The current status of output #5 will be given either by the voice message or the appropriate tone and then the status can be changed with the * button on the 18
19 remote telephone (Note; For output control you must enter in the 4 digit code e.g followed by the output number you wish to control, in this case 5). At any stage, if you enter in an incorrect code you can press the # button on the remote telephone to clear all code entries and then start again. To turn on the optional Microphone (only available if the Voice Board is fitted) you must enter in the appropriate code followed by the * button. To turn the Microphone off you simply press the * button again. To end a Telephone Control session simply hangs up the phone. The panel is monitoring the line at all times and 15 seconds after the last key press it will automatically hang up the line. This 15-second timer is active during the whole Telephone control process so a period of 15 seconds without a key press will cause the panel to hang-up. How Local control works If a Telephone control code for outputs is programmed and the output/s are allowed to be locally controlled from the keypad, then entering the 4 digit code at a keypad will blank the display and the zone LED s will now indicate the output status e.g. if output 1 is on zone 1 LED will be on. By now pressing the 1 button at the panel keypad, output 1 can be turned off provided it is allowed to be locally controlled. To leave local Telephone control mode simply press the <ENTER> button and the keypad will return to normal operation. This feature works the same way that Directly Controlling an Output works (see page 14) only it requires a code to access the function. 19
20 Warranty CROW LIMITED WARRANTY (Crow) warrants this product to be free from defects in materials and workmanship under normal use and service for a period of three years from the last day of the week and year whose numbers are printed on the printed circuit board inside his product. Crow s obligation is limited to repairing or replacing this product, at its option, free of charge for materials or labour, if it is proved to be defective in materials or workmanship under normal use and service. Crow shall have no obligation under this Limited Warranty or otherwise if the product is altered or improperly repaired or serviced by anyone other then Crow. There are no warranties, expressed or implied, of merchantability or fitness for a particular purpose or otherwise, which extend beyond the description on the face hereof. In no case shall Crow be liable to anyone for any consequential or incidental damages for breach of this or any other warranty, expressed or implied, or upon any other basis of liability whatsoever, even if the loss or damage is caused by Crow s own negligence or fault. Crow does not represent that this product can not be compromised or circumvented; that this product will prevent any person injury or property loss or damage by burglary, robbery, fire or otherwise; or that this product will in all cases provide adequate warning or protection. Purchaser understands that a properly installed and maintained product can only reduce the risk of burglary, robbery or other events occurring without providing an alarm, but it is not insurance or a guarantee that such will not occur or that there will be no personal injury or property loss or damage as a result. Consequently, Crow shall have no liability for any personal injury, property damage or any other loss based on claim that this product failed to give any warning. However, if Crow is held liable, whether directly or indirectly, for any loss or damage arising under this limited warranty or otherwise, regardless of cause or origin, Crow s maximum liability shall not in any case exceed the purchase price of this product, which shall be the complete and exclusive remedy against Crow. 20
21 Use the following form to record your changes and customisations. User Name Output Device Designation Zone Zone Name
22 COMMUNICATION OPTIONS: Monitored o Domestic o Speech o SERVICING: Can your system be serviced by another technician? Yes o No o If yes, Installer Code INSTALLATION COMPANY DETAILS: Company Technician Phone Installation Date SERVICING NOTES: 22
Power Wave LCD Keypads CR-16S CR-16M Users Operating and Programming Guide Version 2.00 P/N 7102265 Rev. C N.A May 2003 Contents Introduction...4 Meet the PowerWave Alarm Control System... 4 Typical Alarm
1 Contents Glossary-------------------------------------------------------------------------------------------------------------------6 1. Introduction to the IDS 816---------------------------------------------------------------------------7
Version 1.03 January-2002 1 USER S MANUAL 2 Version 1.03 January-2002 System Details CUSTOMER:...... PHONE:... FAX:... INSTALLED BY:...... PHONE:... FAX:... MAINTENANCE & SERVICE:...... PHONE:... FAX:...
User s Guide SUB-MA7240O-0001.OG.Solution40-111.doc Created: 6/05/03 Last Updated: 23/09/03 MA7240AO-0001 Version 1.0 2 Table Of Contents User List...6 Quick Reference..7 Features...7 Keypad User's Guide...8
INTRODUCTION The BLUGUARD Control Panel is designed for simple operation yet provides the maximum protection for you. Please read this manual carefully and follow the instructions contained in this book.
DESTINY OWNER S MANUAL DESTINY You have made a wise decision to protect your family and property with the DESTINY Security System. The DESTINY has been designed to provide you with a maximum level of security
SCORPION Z16040C, Z8040C and Z5120C Alarm Controller User Instructions Thank you for choosing to purchase this micron security alarm controller. Micron product is manufactured to exacting quality standards.
Destiny 4100 Destiny 4100 Owners Manual TABLE OF CONTENTS INTRODUCTION Control Panel...3 Detection Devices...3 Telephone Keypads...3 GLOSSARY... 4-5 LOCAL PHONE ACCESS Using Your Telephones As Keypads...6
DESTINY 6100 SERIES SECURITY SYSTEM OWNER S MANUAL 800-6006V1 12/01 System Overview General Information Control Panel Detection Devices You have made a wise decision to protect your family and property
TABLE OF CONTENTS...Glossary of terms...2...code Pad Diagram...3 Understanding the Code Pad lights...4 Code Pad tones...5 Fully arming the system On MODE...6 Fully arming the system - Quick Arm MODE...6
Protégé Eclipse LED Keypad User Manual PRT-KLES The specifications and descriptions of products and services contained in this manual were correct at the time of printing. Integrated Control Technology
RANGER 7600 DOWNLOADABLE CONTROL COMMUNICATOR INSTALLATION MANUAL TABLE OF CONTENTS 1. TABLE OF CONTENTS... P.1 2. GENERAL DESCRIPTION... P.2... 3. STANDARD AND OPTIONAL PARTS LIST... P.2... 4. FEATURE
KLEDEU03.fm Page -1 Friday, May 4, 2001 11:25 AM Digiplex LED Keypads User s Manual KLEDEU03.fm Page 0 Friday, May 4, 2001 11:25 AM KLEDEU03.fm Page 1 Friday, May 4, 2001 11:25 AM TABLE OF CONTENTS 1.0
ICP-CC488 EN User s Guide ICP-CC488 Control Panel ICP-CC488 User's Guide Notices EN 2 Copyright Notice Unless otherwise indicated, this publication is the copyright of Bosch Security Systems, Inc. ( Bosch
Solution 844 Operators Manual ISSUE 1.10 Solution 844 Operators Manual Copyright 2001 by, SYDNEY, AUSTRALIA Document Part Number MA406O DOCUMENT ISSUE 1.10 Printed 24 April 2001 This documentation is provided
ICP-CC408 EN User s Guide ICP-CC408 Control Panel ICP-CC408 User's Guide Notices EN 2 Copyright Notice Unless otherwise indicated, this publication is the copyright of Bosch Security Systems, Inc, ( Bosch
LYNX Touch Security System User Guide 1:35 2 PM October 26, 2011 72 Mostly Sunny 68 F F Feels Like 71 Security Messages Automation 5-Day Forecast News Traffic 800-10615 1/12 Rev. A LYNX Touch L5100 Series
VISTA-32FBPT Commercial Fire and Burglary Partitioned Security Systems with Scheduling User Guide 800-11045 2/12 Rev. B 2 TABLE OF CONTENTS SYSTEM OVERVIEW...5 General...5 A Partitioned System...5 Zones...6
RANGER 8600 DOWNLOADABLE CONTROL COMMUNICATOR INSTALLATION MANUAL TABLE OF CONTENTS GENERAL DESCRIPTION... 2 STANDARD AND OPTIONAL PARTS LIST... 2 PARTS DIAGRAM... 3 TERMINAL DRAWING AND SPECIAL NOTES...
The Icon Series User Guide CDV25 Version 1.0 Iconopm1.pm6 200198 The Icon Series The Icon Series The Icon Series Contents Contents 2 Terms you need to Know 3 Keypad Indicators 4 Keypad Keys 5 User Functions
User s Guide for the Text Command Center MY ALARM COMPANY IS: CALL BEFORE TEST: THIS SECURITY SYSTEM IS CONNECTED TO TELEPHONE NUMBER: THE SECURITY CONTROL PANEL IS CONNECTED TO THE PHONE JACK LOCATED:
Proudly Designed and Manufactured in New Zealand By Arrowhead Alarm Products Ltd ARMED = Indicates the System is Armed in Away Mode. STAY = Indicates the System is Armed in Stay Mode. BYPASS = When Flashing,
FA700KP-ADS TouchCenter Keypad User Guide ARMED READY MESSAGE HOME FUNC PANIC BACK TN LIC#: C-0183 C-0180 C-0685 AL LIC#: 001 072 073 080 094 151 403 GA LIC#: LVA205166 K0976-6 1/05 Conventions Used in
INSTRUCTION MANUAL PC255O Canadian Department of Communications Notice NOTICE: The Canadian Department of Communications label identifies certified equipment. This certification means that the equipment
User's Guide PC6010 Quick Reference Guide This manual is for Basic and Advanced users. Each of these types of user can access a different set of functions. The and symbols next to the title of each procedure
S e c u r i t y S y s t e m User's Manual VISTA-40 N7003V1 6/97 SYSTEM OVERVIEW...3 General...3 A Partitioned System...3 Zones...3 Burglary Protection...4 Fire Protection...4 Alarms...5 Emergency (Panic)
Solution-6 Operators Manual Page 1 Preface Congratulations on selecting the Solution-6 security control system for your installation. So that you can obtain the most from your unit, we suggest that you
LYNX Touch L5210 Series Security System User Guide 800-19975 12/14 Rev. B LYNX Touch L5210 Series Your Honeywell security system is designed for use with devices manufactured or approved by Honeywell for
ADVISOR CD 3403 User Manual Software from version: V6.0 142715999-1 COPYRIGHT SLC BV 1996. All rights reserved. No part of this publication may be reproduced, transmitted, stored in a retrieval system,
$'(0&29,67$ 3DUWLWLRQHG6HFXULW\6\VWHP 8VHU*XLGH N7003V3 5/04 Rev A 2 TABLE OF CONTENTS SYSTEM OVERVIEW...5 General...5 A Partitioned System...5 Zones...5 Fire Protection...6 Burglary Protection...6 Alarms...6
Master Code The 4 digit Master Code is used for arming and disarming the system, for programming additional access codes, and for changing other features. The Master Code will be supplied to you by your
CC408 EN Quick Reference Guide Solution 880 CC408 Quick Reference Guide Notices EN 2 Copyright Notice Unless otherwise indicated, this publication is the copyright of Bosch Security Systems Pty Ltd ( Bosch
The most user friendly Contents Section 1 Overview of System 1.1 Kit Contents 1.2 Tools Required 1.3 System Features Security Alarm System L S 4 0 0 Section 2 Planning your Installation 2.1 Location of
N6484V3 3/96 5827BD and 5827BDE WIRELESS BI-DIRECTIONAL KEYPADS Used with 5800TM Transmitter Module INSTALLATION INSTRUCTIONS and OPERATING GUIDE Unless otherwise indicated, all information in this manual
Fire and Burglary System User's Manual 5120XM N8031 6/96 SYSTEM OVERVIEW...3 General...3 Zones...3 Fire & Emergency Protection...3 Burglary Protection...4 Alarms...4 Memory of Alarm...4 ABOUT THE KEYPADS...5
LED Keypads D720 Series User s Guide D720 D720W D720B Table of Contents Fire Safety 3 The D720/D720W/D720B Keypad 4 Security System Basics 5 Turning the System On and Off 7 Silencing and Reporting Alarms
NetworX NX-8V2 LED Keypad User Manual POWER Light is on when AC power is present; flashes to indicate a low battery condition. ARMED Light is on when armed; off when disarmed; flashes to indicate a previous
User Access Codes The CONDOPLEX series panels can be programmed with nine (9) different user codes and one (1) duress code. User codes are normally used for arming and disarming the panel. The duress code
8 plus and16 plus User s Guide GALAXY 16+ V2.XX 06.22 TUE 30 JUN 1 2 3 4 5 6 7 8 9 0 * # A u B u ent esc IU1-0018 ZST 962 Issue 2 Contents INTRODUCTION... 1 Glossary of Terms... 3 KEYPAD INFORMATION...
PROGRAMMING GUIDE SPECTRA CONTROL PANELS V1.2 1725, 1725EX, 1728 AND 1728EX 1755, 1755EX, 1758, AND 1758EX TABLE OF CONTENTS HOW DO I PROGRAM THE SYSTEM?... 4 Single Digit Data Entry Method (Hexadecimal
MG5000 MG5050 SP5500 SP6000 SP7000 User Guide We hope this product performs to your complete satisfaction. Should you have any questions or comments, please visit www.paradox.com and send us your comments.
BENTEL SECURITY srl reserves the right to modify the technical specifications of this product without prior notice. via Florida - Z.I. Valtesino - 63013 GROTTAMMARE (AP) - ITALY USER MANUAL: Digital communicator
PC4020 v3.5 Instruction Manual WARNING: This manual contains information on limitations regarding product use and function and information on the limitations as to liability of the manufacturer. The entire
Challenger10 Users Manual P/N MAUSER-TS1016 REV 01 ISS 18FEB13 Copyright Trademarks and patents Manufacturer Agency compliance Contact information 2013 UTC Fire & Security. All rights reserved. The Challenger
User Manual Summary of Keypad Main User Commands Full Set Code > Part Set Code > System Unset Silence an Alarm Partition Full Set Partition Part Set Code> Code> Code > > Partition No. > Code > > Partition
Advisor Advanced User Guide P/N 1068996 (EN) REV G ISS 28AUG15 Copyright Trademarks and patents Manufacturer Version Certification 2015 UTC Fire & Security Americas Corporation, Inc. All rights reserved.
VISTA-128BP/VISTA-250BP/ VISTA-128SIA Enhanced Commercial Burglary Partitioned Security System With Scheduling User Guide K5895V5 4/09 Rev C Your Honeywell security system is designed for use with devices
VISTA-15PMT VISTA-20PMT Security Systems User s Guide Monitronics R I N T E R N A T I O N A L, I N C. K5309-1MTV2 7/04 Rev. A Reference: MTV15P, MTV20P IMPORTANT! PROPER INTRUSION PROTECTION For proper
NETWORX TM User manual NX-4 POWER Light is on when AC power is present; flashes to indicate a low battery condition. ARMED Light is on when armed; off when disarmed; flashes to indicate a previous alarm.
POWERMAX PRO USER GUIDE Quick Guide To Primary Alarm Control Operations...2 Contact list form...2 Luminous Indicator Signals...2 Siren Signals...3 Useful Hints For PowerMax Pro Users...3 1. Introduction...4
MG5000 MG5050 SP5500 SP6000 SP7000 User Guide We hope this product performs to your complete satisfaction. Should you have any questions or comments, please visit www.paradox.com and send us your comments.
XRSuper6 User s Guide Silencing an Alarm When the alarm bell or siren is sounding, enter your user code or present your card to a keypad or reader during the Status List display. All/Perimeter or Home/Sleep/Away
Instruction Manual PC56O Software Version 1.OA W A R N I N G This manual contains information on limitations regarding product use and function and information on the limitations as to liability of the
NESS 5000 SERIES DIALLER INSTALLATION MANUAL This manual is designed to provide the installation instructions on the NESS SECURITY PRODUCT'S 5000 SERIES Dialler. For complete details on the warranty or
Owner's Manual Includes the SIA CP-01 Control Panel Standard Features for False Alarm Reduction Document Number 21R00-1 Rev. 2.14 February, 2007 Document Number 21R00-1 Rev. 2.14 February, 2007 Copyright
MAX INSTANT READY R BYPASS AWAY STAY PAGE ARMED READY 1 OFF MAX INSTANT READY R 2 AWAY 3 STAY BYPASS 9 CHIME FA168CPS / FA168CPSSIA FA148CP / FA148CPSIA Security Systems ARMED READY A B C D 7 4 1 2 3 OFF
Intelligent GSM Auto-Dial Alarm System User s Manual Profile For a better understanding of this product, please read this user manual thoroughly before using it. Contents Function Introduction (3) Alarm
Solution 6+6 Wireless On/Off Installation Manual ISSUE 1.20 MA670I This page has been included for you to cut out and insert into the spine of the folder Solution 6+6 Wireless On/Off Installation Manual
Silencing an Alarm When the alarm siren is sounding, enter your user code or present your card to a keypad during the Status List display. All/Perimeter or Home/Sleep/Away System CANCEL VERIFY displays.
970213-0001 ESPRIT 727 U LISTED User Manual VERSION 3.3 P R D O X S E C U R I T Y S Y S T E M S Paradox Security System Graphic Dept - PRINTED IN CANADA READY The green LED must be " on", indicating all
XL-20 Security System Owner s Manual N9824 11/97 TABLE OF CONTENTS QUICK REFERENCE...1 Turn System On...1 Turn System Off...1 Turn System On and Stay Inside...1 Turn System On: Perimeter Sensors Instant
16 and 16 plus User s Guide GALAXY 16+ V2.XX 06.22 TUE 30 JUN 1 2 3 4 5 6 7 8 9 * 0 # A u B u ent esc Contents INTRODUCTION... v QUICK OPERATION GUIDE...vii GLOSSARY OF TERMS... ix KEYPAD INFORMATION...
System Introduction S E C T I O N 1 1.1 Specifications Downloading Software Support PC585 uses DLS-1 v6.5 and up. Flexible Zone Configuration Four fully programmable zones; system expandable to eight zones
ELECTRONIC ENGINEERING LTD. Serenity CONTROL PANEL Technician s Handbook P\N 7107960 SERENITY technician Guide IMPORTANT NOTICE All information and data contained in this document is proprietary and confidential.
Veritas User Guide Quick Reference Guide THANK YOU FOR VOTING TEXECOM THANK YOU FOR VOTING TEXECOM USER GUIDE Security Control Panels 1 INS167 Overview Premier Series User Guide 1. Overview Introduction
MG5000 V2.4 MG5050 V2.4 SP5500 V2.4 SP6000 V2.4 SP7000 V2.4 Programming Guide We hope this product performs to your complete satisfaction. Should you have any questions or comments, please visit www.paradox.com
Contact ID as of 2/2/2015 100 Medical Zone A non-specific medical exists 101 Personal Emergency Zone Emergency Assistance request 102 Fail to report in Zone A user has failed to activate a monitoring device
VISTA-128BPT/ VISTA-250BPT/ VISTA-128BPTSIA Commercial Burglary Partitioned Security System With Scheduling User Guide 800-06905 6/10 Rev. E IMPORTANT! RECOMMENDATIONS FOR PROPER INTRUSION PROTECTION For
Protégé EliteSuite Eclipse LED Keypad Installation Manual ELT-KLES The specifications and descriptions of products and services contained in this manual were correct at the time of printing. Integrated
Installation Manual Premier // Issue 0 Premier // Installation Manual 5. Operating the System Introduction Before attempting to operate the alarm system ensure you have familiarised yourself with all the
NX148-E LCD KEYPAD TABLE OF CONTENTS GLOSSARY OF TERMS... 3 UNDERSTANDING THE LIGHTS... 4 KEYPAD FUNCTIONS... 5 ARMING YOUR SYSTEM IN THE AWAY MODE... 5 MAKING YOUR SYSTEM READY TO ARM... 5 ARMING YOUR
HOME AUTOMATION, INC. Control & Security System Owner's Manual Document Number 20R00-2 Rev A February, 2002 Copyright 2001-2002 Home Automation, Inc. All Rights Reserved Contents INTRODUCTION... 1 Underwriter's