2 Outline Before you start Critical building information drives requirements Access Requirements Access, aerial access, road design, remoteness, fire lanes, residential development Water Supply Requirements Hydrant placement, fire flow, fire department connections General Requirements Access during construction, clearance to landscaping Performance Alternatives Types of construction, level of sprinkler protection Odds & Ends Address identification, Lock box, undeveloped areas
3 Before you start Critical Building Information Occupancy Type (or proposed occupancy type) Construction Type Sprinklers Provided? NFPA 13 NFPA 13R NFPA 13D (one and two family dwellings) Total Building Square Footage Total Building Height
4 Access Requirements
5 Fire Department Access 150 feet within ALL portions of the building Measured as the hose lays on the ground Can be extended to 250 if the building is fully sprinklered Fire apparatus access roads shall be designed and maintained to support the imposed loads of fire apparatus and shall be of a continuous hard surface such as concrete, asphalt, rock, or other continuous hard surface material so as to provide all weather maintenance and driving capabilities. Grass pavers or similar type products that are not readily distinguishable as a road surface shall not be used.
7 Fire Department Access Roads City of Des Moines Fire Prevention Code Section Fire apparatus access roads shall have a minimum unobstructed width of 20 feet 26 feet where a hydrant is located on the access road.
8 Fire Apparatus Access Roads Vertical Clearance Delete Code Section: IFC Replace with the following language: Dimensions. Fire apparatus access roads shall have a minimum unobstructed width of not less than 20 feet (6096 mm), exclusive of shoulders, except for approved security gates in accordance with Section 503.6, and an unobstructed vertical clearance of not less than 14 feet (4268 mm).
9 Fire Department Access Roads - Loading D102.1 Access and loading. Facilities, buildings or portions of buildings hereafter constructed shall be accessible to fire department apparatus by way of an approved fire apparatus access road with an asphalt, concrete or other approved driving surface capable of supporting the imposed load of fire apparatus weighing at least 75,000 pounds ( kg).
10 Fire Department Access Roads Grade and Angles Grade. The grade of the fire apparatus access road shall be within the limits established by the fire code official based on the fire department s apparatus. D103.2 Grade. Fire apparatus access roads shall not exceed 10 percent in grade Angles of approach and departure. The angles of approach and departure for fire apparatus access roads shall be within the limits established by the fire code official based on the fire department s apparatus.
11 Access Road vs. Fire Lane Not every road is a fire lane, nor does it have to be Not every fire lane needs to be marked: D Roads 20 to 26 feet in width. Fire lane signs as specified in Section D103.6 shall be posted on both sides of fire apparatus access roads that are 20 to 26 feet wide. D Roads more than 26 feet in width. Fire lane signs as specified in Section D103.6 shall be posted on one side of fire apparatus access roads more than 26 feet wide and less than 32 feet wide.
12 Fire & Emergency Vehicle Lanes Add Code Section: IFC 511 Language: Section 511 Fire and Emergency Vehicle Lanes. Section General. Fire and emergency vehicle lanes shall be provided and maintained in accordance with section through 511.6, and referred to as fire lanes in this ordinance. Section Purpose. The requirement that Fire Lanes be established in certain parking areas and the enforcement of restrictions on parking in such Fire Lanes established in this Chapter are designed to ensure adequate access to commercial, office, multifamily, and other high density use facilities by fire-fighting and other emergency vehicles. Section Designation. The Fire Code Official may designate fire lanes on private and public property as deemed necessary for the protection of life and property.
13 Fire & Emergency Vehicle Lanes Section Obstruction. No person shall park or place a vehicle or other obstruction in a designated fire lane that would prevent such fire lane from being immediately accessible to emergency vehicles, or deter or hinder emergency vehicles from gaining immediate access to the fire lane. A written request to the jurisdictional Fire Code Official for temporary obstruction of a fire lane shall be submitted for approval. Section Signs and markings. Wherever a fire lane has been designated, the Code Official shall cause appropriate signs and markings to be placed identifying such fire lanes. Signs or markings shall be maintained in a clean and legible condition at all times and shall be replaced or repaired when necessary to provide adequate visibility. Fire lanes may be established or relocated at the time of plan review, preconstruction site inspection, and/or post construction site inspection, as well as any time during the life of the occupancy as needed to provide and maintain emergency vehicle access. All designated fire lanes shall be clearly marked in the following manner:
14 Fire & Emergency Vehicle Lanes (signs and markings) 1. Vertical curbs shall be painted red on the top and side, extending the length of the designated fire lane. Rolled curbs or surfaces without curbs shall have a red (6) inch wide stripe painted the length of the designated fire lane. One of the following identification lettering methods shall be utilized: A. The words NO PARKING FIRE LANE (Except for Emergency Vehicles) shall be stenciled with three (3) inch white letters and a minimum three quarter (¾) inch stroke on the face of the curbing, or in the absence of vertical curbing, on the red stripe, and spaced at fifty (50) foot intervals or portions thereof, or B. The pavement adjacent to the painted curbs shall be marked with minimum eighteen (18) inch in height block lettering with a minimum three (3) inch brush stroke reading: NO PARKING - FIRE LANE. Lettering shall be red and spaced at fifty (50) foot intervals or portions thereof
15 Fire & Emergency Vehicle Lanes (signs and markings) 2. Signage identifying fire lanes shall conform to the following: Fire lane signs shall be 18 inches tall x 12 inches wide with red letters on a white reflective background to read Fire Lane No Parking Except For Emergency Vehicles or similar verbiage as approved by the code official. Fire lane signs shall be placed 2-4 feet from the edge of the Fire Lane. The bottom of fire lane signs shall be between five (5) and seven (7) feet from the ground. Intermediate fire lane signs shall be set every one hundred (100) feet in a continuous fire lane. The BEGINS sign shall mark the beginning of a fire lane and shall be mounted below the first fire lane sign. The ENDS sign shall mark the ending of a fire lane and shall be mounted below the last fire lane sign. The BEGINS and ENDS signage may be omitted by the Code Official due to the location of the fire lane. Signs may be placed on a building when approved by the Fire Code Official.
16 Fire & Emergency Vehicle Lanes (example)
17 Fire Access Roads - Dead Ends Dead ends. Dead-end fire apparatus access roads in excess of 150 feet in length shall be provided with an approved area for turning around fire apparatus.
18 Fire Access Roads - Dead Ends
19 Secondary Access Requirements 3 Triggers for secondary access Single-Family Multi-family Commercial Remoteness: Where two fire apparatus access roads are required, they shall be placed a distance apart equal to not less than ½ the length of the maximum overall diagonal dimension of the lot or area to be served, measured in a straight line between accesses.
20 Residential Developments Single-Family >30 homes, unless sprinklered, then up to 60 Delete Code Section: IFC D107.1 Exception #2 Replace with the following language: 2. The number of dwelling units on a single fire apparatus access road shall not be increased unless alternative fire and life safety measures have been provided, as determined by the fire code official. When alternative fire and life safety measures have been implemented, at no time shall the number of dwelling units on a single fire apparatus access road exceed 60 units.
21 Residential Developments (example)
22 Multi-Family Multiple-family residential projects having more than 100 dwelling units shall be equipped throughout with two separate and approved fire apparatus access roads. Exception: Projects having up to 200 dwelling units may have a single approved fire apparatus access road when all buildings, including nonresidential occupancies, are equipped throughout with approved automatic sprinkler systems installed in accordance with Section or Multiple-family residential projects having more than 200 dwelling units shall be provided with two separate and approved fire apparatus access roads regardless of whether they are equipped with an approved automatic sprinkler system.
24 Commercial Secondary Access Buildings exceeding 62,000 sqft in area. Buildings or facilities having a gross building area of more than sqft shall be provided with 2 separate and approved apparatus access roads. Exception: Projects having a gross building area up to 124,000 sqft that have a single approved fire apparatus access road when all buildings are equipped throughout with approved automatic sprinkler systems. Remoteness: Where two fire apparatus access roads are required, they shall be placed a distance apart equal to not less than ½ the length of the maximum overall diagonal dimension of the lot or area to be served, measured in a straight line between accesses.
26 Aerial Access Roads Where the vertical distance between the grade plane and the highest roof surface exceeds 30 feet (9144 mm), approved aerial fire apparatus access roads shall be provided. For purposes of this section, the highest roof surface shall be determined by measurement to the eave of a pitched roof, the intersection of the roof to the exterior wall, or the top of parapet walls, whichever is greater. Aerial fire apparatus access roads shall have a minimum unobstructed width of 26 feet (7925 mm), exclusive of shoulders, in the immediate vicinity of the building or portion thereof. At least one of the required access routes meeting this condition shall be located within a minimum of 15 feet (4572 mm) and a maximum of 30 feet (9144 mm) from the building, and shall be positioned parallel to ¼ of the perimeter of the building. D105.1 (Modified by CICC to accommodate reasonable development.)
27 Aerial Access Roads Delete Code Section: IFC D105.3 Replace with the following language: D105.3 Proximity to building. At least one of the required access routes meeting this condition shall be positioned along a total of ¼ of the building perimeter and located within the minimum and a maximum dictated by the table below, Table D The arrangement of the aerial fire apparatus access road shall be approved by the fire code official and may be discontinuous with approval. Building Height (ft) Distance from Building (ft) Minimum Maximum Minimum Maximum N/A 15 30
28 Water Supply Requirements
29 Hydrant Layout IFC Section ; where a portion of the facility or building hereafter constructed or moved into or within the jurisdiction is more than 400 feet from a hydrant on a fire apparatus access road, as measured by an approved route around the exterior of the facility or building, on-site fire hydrants and mains shall be provided (Exception: R-3, U & sprinklered buildings shall be 600 ft).
30 Fire Hydrants Near FDCs Delete Code Section: IFC Replace with the following language: Hydrant for fire department connections. Buildings equipped with a fire department connection installed in accordance with Section 912 shall have a fire hydrant located on a fire access road within 100 feet (30 m) of the fire department connection as measured by an approved route around the exterior of the building. Exception: The distance shall be permitted to exceed 100 feet (30 m) where approved by the fire code official.
31 Clear Space Around Fire Hydrants Delete Code Section: IFC Replace with the following language: Clear space around hydrants. A 5-foot (1524 mm) horizontal clear space shall be maintained around the circumference of fire hydrants, as measured from the center-point of the hydrant, except as otherwise required or approved.
32 Fire Hydrant Installation Insert New Code Section: IFC Insert the following language: Fire Hydrant Installation. Fire hydrants shall be installed with the grade mark on the fire hydrant at the level of finished grade. The large diameter connection shall be installed such that the connection is oriented facing the fire department access road.
33 Water Supply Fire Flow Requirements Required water supply. An approved water supply capable of supplying the required fire flow for fire protection shall be provided to premises upon which facilities, buildings or portions of buildings are hereafter constructed or moved into or within the jurisdiction. Fire-flow when sprinklers are present: B105.3 Water supply for buildings equipped with an automatic sprinkler system. For buildings equipped with an approved automatic sprinkler system, the water supply shall be capable of providing the greater of: 1. The automatic sprinkler system demand, including hose stream allowance. 2. The required fire-flow.
34 How is fire-flow determined? SECTION B105 FIRE-FLOW REQUIREMENTS FOR BUILDINGS B105.1 One- and two-family dwellings, Group R-3 and R- 4 buildings and townhouses. The minimum fire-flow and flow duration requirements for oneand two-family dwellings, Group R-3 and R-4 buildings and townhouses shall be as specified in Tables B105.1(1) and B105.1(2). B105.2 Buildings other than one- and two-family dwellings, Group R-3 and R-4 buildings and townhouses. The minimum fire-flow and flow duration for buildings other than one- and two-family dwellings, Group R-3 and R-4 buildings and townhouses shall be as specified in Tables B105.2 and B105.1(2).
37 Benefit for Sprinklers Required fire flow can be reduced based on the presence of sprinklers. Need to use Table B105.2 to determine the required fire flow. This must be compared to the fire flow per B105.3 to confirm actual required fire flow.
38 Example: Fire Flow for Townhomes 5 row homes (townhomes) 2,200 ft² each 11,000 ft² total building area Wood frame (type V-b construction) Non-sprinklered Vs Sprinklered
39 Example: Fire Flow for Commercial Building Commercial office building 45,000 ft² total building area Non-sprinklered Wood frame (Type V-B construction) Vs Type II A
40 Example: Fire Flow for Commercial Building Commercial office building 45,000 ft² total building area Sprinklered NFPA 13 Wood frame (Type V-B construction) Vs Type II A 3,000 gpm *.25 = 750 gpm (but can t be lower than 1,000 gpm - footnote a) for 3 hours 5,750 gpm *.25 = 1440 gpm for 4 hours
41 Performance Alternatives Type of Construction Non-combustible construction when wood frame is allowed Sprinkler Protection NFPA 13 when NFPA 13R is required Access limitations Aerial access limitations
42 Example of An Alternative Design Multi-building lot A skywalk node A multi-purpose commercial building Restaurant 1 st floor (A-2) Office (B) 2 nd & 3 rd floors 5-6 story residential Two buildings will exceed 30 and require aerial access Lot is intended to be divided to allow buildings to be owned and financed separately. There is an elevation change North to South on the lot that prevents through access on the site.
44 Alternative Design Discussion Unable to meet the Aerial Access Requirements No inter-site aerial access Alternative Design All buildings on the site non-combustible construction Potentially the 3 Story commercial could have been combustible construction Potentially the residential building could have been Podium style construction NFPA 13 sprinkler systems Potential for unsprinklered 3-story Potential for 13R sprinkler system in the Residential occupancy
45 Odds & Ends
46 Odds & Ends Address Identification Undeveloped areas hydrants per Appendix C Adding on to an Existing Building Tanks and Impact protection High-Rise Specific Requirements Using Autoturn to Verify Access during construction Phased projects (temporary turn-arounds)
47 Address Identification Delete Code Section: IFC Replace with the following language: Address identification. New and existing buildings shall have approved address numbers, building numbers or approved building identification placed in a position that is plainly legible and visible from the street or road fronting the property. These numbers shall be black or white and shall contrast with their background. Where required by the fire code official, address numbers shall be provided in greater dimension or additional approved locations to facilitate emergency response. Address numbers shall be Arabic numbers or alphabetical letters. Numbers and letters shall be a minimum height and a minimum stroke width as dictated by Table Where access is by means of a private road and the building cannot be viewed from the public way, a monument, pole or other sign or means shall be used to identify the structure. Address numbers shall be maintained.
48 Address Identification Table Minimum Height and Stroke Widthᵃ ᵇ Distance from the centerline of the Public Way (ft) Minimum Height (in) Minimum Stroke Width (in) Less than / / For each additional 100 Increase 2 Increase 1/2 ᵃ Exterior suite identification, minimum height shall be 4 inches and stroke width shall be ½ inch. ᵇ Interior suite identification, minimum height shall be 2 inches and stroke width shall be ¼ inch.
49 Additions to Existing Buildings All additions must meet access, hydrant, and other IFC site plan requirements. Additionally, when possible, existing nonconforming situations should be remedied, alleviated, or improved. At a minimum the addition must not make an existing nonconforming situation worse vis-à-vis access. Additions of sprinklers to existing buildings may not trigger the requirement for the FDC to be located within 100 of a hydrant.
51 Impact Protection Posts. Guard posts shall comply with all of the following requirements: 1. Constructed of steel not less than 4 inches (102 mm) in diameter and concrete filled. 2. Spaced not more than 4 feet (1219 mm) between posts on center. 3. Set not less than 3 feet (914 mm) deep in a concrete footing of not less than a 15-inch (381 mm) diameter. 4. Set with the top of the posts not less than 3 feet (914 mm) above ground. 5. Located not less than 3 feet (914 mm) from the protected object.
53 High-Rise Specific Requirements Redundant FDC Redundant Water Supply
54 Using Autoturn to Verify The template to use for DMFD apparatus is available on our website: ts/fire/pdf/apparatus%20specific ations%20for%20auto%20turn.pdf
56 Access During Construction Insert New Code Section: IFC Section Language: Section Construction Site Access. Approved fire apparatus access roads shall be provided for every facility, building or portion of a building as soon as construction commences. The fire apparatus access road shall comply with the requirements of Section and this section and shall extend to within 100 feet ( mm) of all portions of the facility and all portions of the exterior walls of the first story of the building as measured by an approved route around the exterior of the building or facility. Exception: The fire code official is authorized to increase the dimension of 100 feet ( mm) where: 1. The building is equipped throughout with an approved automatic sprinkler system that is fully functional and installed in accordance with Section , or Fire apparatus access roads cannot be installed because of location on property, topography, waterways, nonnegotiable grades or other similar conditions, and an approved alternative means of fire protection is provided.
57 Phased Projects If a dead-end is created (beyond 150 feet) then a turn-around is required Even if future connection will allow for a through access
Amendments for 2015 IFC CHAPTER 1 SCOPE AND ADMINISTRATION Section 101.2.1 Appendices. All appendices to be adopted Section 113.2 Schedule of permit fees. Is AMENDED to read: A fee for each permit shall
PASS / RESUBMIT Rancho Santa Fe Fire Protection District P.O. Box 410 18027 Calle Ambiente Rancho Santa Fe California 92067-0410 Tel. (858) 756-5971 Fax (858) 756-4799 FIRE PLAN CHECK CORRECTION List for
Established 1949 FIRE PREVENTION OFFICE Placer Hills Fire Protection District NEW PROJECT GUIDELINES The following are guidelines for new development. Any submitted plans must comply with these guidelines,
New Construction Fire Inspection Process This document is intended to provide the Owner, Designer, and/or Contractor of new construction with an outline of required fire inspections and with the specific
July 1, 2010 SANTA ROSA FIRE DEPARTMENT FIRE PREVENTION BUREAU STANDARD STANDPIPE SYSTEMS PURPOSE This standard outlines the general requirements for the installation of standpipe systems. CODE REFERENCES
DEPARTMENT OF PUBLIC SAFETY FIRE MARSHAL S OFFICE 9611 SE 36 TH ST Mercer Island, WA 98040 (206) 236-3515 direct; (206) 236-3622 FAX Rod Mandery, Fire Marshal Updated version: 03-19-2002 Fire & Life Safety
OXNARD FIRE DEPARTMENT 360 West Second Street Oxnard, CA 93030 (805) 385-7722 Fax (805) 385-8009 REQUIREMENTS FIRE HYDRANT STANDARDS Fire hydrants and required access roads shall be provided prior to and
CHAPTER 1 SCOPE AND ADMINISTRATION 102.7 Referenced codes and standards. The codes and standards referenced in this code shall be those that are listed in Chapter 45 47 and such codes and standards shall
Local Amendments 2009 International Fire Code By the following jurisdictions: Black Forest Fire & Rescue Cimarron Hills Fire Department Wescott Fire Department Falcon Fire Department Security Fire Department
FIRE SPRINKLER SYSTEMS POLICY Revised 1/1/17 DESIGN AND SUBMITTAL REQUIREMENTS All new and existing fire sprinkler systems within the jurisdiction of the City Fire Department shall meet all of the applicable
Menlo Park Fire Protection District Bureau of Fire Prevention and Life Safety 170 Middlefield Rd. Menlo Park, CA 94025 650-688-8425 Bureau of Fire Prevention and Life Safety SECTION 101.6 POLICY MANUAL
I. General II. III. Richardson Fire Department 136 N. Greenville Avenue, Richardson, TX 75081 Telephone: 972-744-5750 Fax: 972-918-0971 www.cor.net/fire Security Gates - Policy [revised 10/03/2017] Submittals
Table of Contents CHAPTER 10 ADMINISTRATIVE RULES FOR CERTIFICATION OF CHILD CARE FACILITIES FIRE STANDARDS FOR FAMILY CHILD CARE HOME Section No. Subject Page No. 1 Authority and Purpose 10-1 2 Definitions
RESIDENTIAL CARE USER GUIDE UPDATES TO MANITOBA BUILDING/FIRE CODE: Manitoba Regulation 221/2015 and Manitoba Regulation 222/2015 DATE: MARCH 17, 2016 1. INTRODUCTION On April 1, 2016, new building and
Chapter 1 Worksheet 1. When the present code requires certain safety to life requirements for existing buildings, those requirements shall. a. be void b. apply c. be approved d. be grand-fathered 2. The
SUBTITLE X Chapter 20.200 BUILDING CODE Sections: 20.200.010 Building codes adopted by reference. 20.200.011 Local amendments of International Building Code. 20.200.012 Local amendments of International
Guidelines: The goal of the Denison Fire Department is to assist its customers in understanding our submittal, plan review and inspection process and policies, as they pertain to new construction. Familiarity
This information is intended to assist you in preparation for the annual high-rise inspection. This is not a complete list and the Inspector may identify other conditions or issues in the building that
Consumer Fireworks Retail Sales (CFRS) Facility Requirements. Site Plan. The site plan for tents shall show the location of the tent on the site and indicate the minimum separation distances required by
2.11 Submittal Guidelines for Emergency Evacuation Signs (2016) Reference: California Code of Regulations, Title 19, Section 3.09, the California Health and Safety Code Section 13220, the SFFC, Section
St. Number Dir Street Name Street Type Inspected Time of Day to be Re-inspected Zip Code Occupancy Type Emergency Contact Phone (Inc. Area Code) Building Owner Building Owner Mailing Address Bldg. Owner
210 N CHURCH ST CHARLOTTE NC 28202-2256 MECKLENBURG COUNTY RISK ID: 32 NC99 040235 ON-SITE SURVEY: 4/1/2009 LAST UPDATE: 4/1/2009 SUMMARY Building receiving sprinkler credit: SPRINKLERED Grade: 68 Percent
COUNTY OF SACRAMENTO DEPARTMENT OF COMMUNITY DEVELOPMENT BUILDING PERMITS & INSPECTION DIVISION Document # GI-16 Page 1 of 7 Large Family Day Care Homes Large family day care homes are licensed for day
Section 20.945.040 General Design Standards for Surface Parking Areas. A. Review Authority. Parking lot design and drainage shall be subject to review and approval of the City Transportation Manager. B.
CHAPTER 23.45 LOCAL AMENDMENTS TO THE INTERNATIONAL FIRE CODE 2012 EDITION Sections 23.45.100... Local amendments to the International Fire Code, 2012 Edition.... 2 220.127.116.11.2 Information on construction
REQUIREMENTS FOR NFPA 13 SYSTEM Building Inspections Sprinkler Permit Applications A complete application for a Sprinkler Permit will comply with the requirements of Chapter 8 of NFPA 13. Hydraulic calculations
CHAPTER 14 FIRE SAFETY DURING CONSTRUCTION, ALTERATION AND DEMOLITION SECTION FC 1401 GENERAL 1401.1 Scope. This chapter shall govern fire safety measures during the construction, alteration, or demolition
ARTICLE I. GENERAL PROVISIONS CHAPTER 530 SITE PLAN REVIEW Community Planning and Economic Development Development Services Division 250 South 4 th Street, Room 300 Minneapolis MN 55415-1316 612-673-3000
Department of Fire Rescue & Emergency Services Fire Marshal s Office Dania Beach District 103 West Dania Beach Blvd. Dania Beach, Florida 33004 Office: (954)342-4262 Fax: (954)342-4265 FIRE SPRINKLER SHOP
CHAPTER 9 FIRE PROTECTION SYSTEMS > SECTION 901 GENERAL 901.1 Scope. The provisions of this chapter shall specify where fire protection systems are required and shall apply to the design, installation,
Fire Department Fees. North Liberty Fire Department 25 W. Cherry St., North Liberty, IA Phone: (319) 626-5717 Fax: (319) 626-3238 Fire Department Fee Schedule Council Members, I just wanted to take a moment
Code Reference NFPA 1 18.104.22.168 Florida Specific Amendment Anytime a reference is made to NFPA 1 or NFPA 101 within this code it shall be the Florida specific version of NFPA 1 and NFPA 101. Reason for Amendment
City of Chilliwack Bylaw No. 3464 A bylaw to regulate fire prevention and the protection of life and property NOW THEREFORE the Council of the City of Chilliwack in open meeting assembled enacts as follows:
LANDSCAPE AND IRRIGATION PLAN PREPARATION GUIDELINES The Parks Planning and Development Division of the City of Modesto s Parks, Recreation and Neighborhoods Department is responsible for the task of reviewing
DEPARTMENT OF PLANNING JEFFERSON PARISH, LOUISIANA DESIGN REVIEW REPORT : CPZ-3-1 : (S) Cynthia Lee-Sheng AT LARGE: A Chris Roberts B Elton M. Lagasse ADVERTISING DATES: 06/03/1 06/10/1 06/17/1 PAB PUBLIC
2010 FIRE CODE OF NEW YORK STATE CHAPTER 14 FIRE SAFETY DURING CONSTRUCTION AND DEMOLITION SECTION 1401 GENERAL 1401.1 Scope. This chapter shall apply to structures in the course of construction, alteration,
EXIT ROUTES, EMERGENCY ACTION PLANS, AND FIRE PREVENTION PLANS PART 1: INTRODUCTION Applicability of This Module Use the following General Applicability Checklist to determine whether a rulebook and its
AMENDMENTS TO THE BUILDING AND FIRE CODE FOR THE CITY AND COUNTY OF DENVER The 2016 Denver Building and Fire Code includes the following codes except as amendment herein. 2015 IBC (Building) 2015 IFC (Fire)
780 CMR: MASSACHUSETTS AMENDMENTS TO THE INTERNATIONAL BUILDING CODE 2009 CHAPTER 9: FIRE PROTECTION SYSTEMS 901.1 Add these notes: Note 1. Throughout Chapter 9, when reference to the International Plumbing
EULESS FIRE DEPARTMENT FIRE MARSHAL S OFFICE INFORMATION LINE: Revised 8/2004 Fire Chief Lee Koontz Fire Marshal Paul Smith EFD-FMO 3-1 2003 International Fire & Building Code as Amended NFPA Standards
2. The Group F occupancy has have an a combined occupant load of 500 or more above or below the lowest level of exit discharge. Exception: Manual fire alarm boxes are not required where the building is
Taming the Health Care Building Codes NFPA vs. The International and Chicago Building Codes Comparing the Codes: NFPA 101 Life Safety Code (2000) (NFPA) International Building Code (2012) (IBC) Chicago
ORDINANCE CHAPTER 26-ORDINANCES FIRE PREVENTION REGULATIONS DATE PASSED 74-024 Establish Fire Prevention Bureau 02.05.74 76-037 Word "Director" changed to "Fire Marshal", addition of Article 5 - Life Safety
A well designed landscape, when made an integral part of a development plan, provides aesthetic appeal and makes an important contribution to the health, safety, and general welfare of the community by:
NB12-0304 NBIC Part 1 SUPPLEMENT 3 INSTALLATION OF LIQUID CARBON DIOXIDE STORAGE VESSELS S3.1 SCOPE This section provides requirements for the installation of Liquid Carbon Dioxide Storage Vessels (LCDSV
Josephine County, Orego n Community Development Planning Division 700 NW Dimmick, Suite C / Grants Pass, OR 97526 (541) 474-5421 / Fax (541) 474-5422 E-mail: firstname.lastname@example.org Dear Property Owner:
BEST PRACTICES: PARKING MANAGEMENT & DESIGN Planning for Parking December 2015 The provision of parking is an essential part of planning and site design. However, parking is often associated with negative
ARLINGTON COUNTY, VIRGINIA County Board Agenda Item Meeting of January 27, 2007 DATE: January 12, 2007 SUBJECT: U-3101-04-2 Use Permit Review for drive-through facilities; premises known as 5222 Lee Highway
To: Planning and Zoning Commission From: City Staff Date: November 15, 2016 Re: Case #16026 Raymore Activity Center Site Plan GENERAL INFORMATIONaaaaaaaaaaaaaaaaaaaaaaaaaaaaaaaa Applicant/ Property Owner:
The following are the Proposed Amendments to 2015 edition of the Life Safety Code (NFPA 101): 1.1.1 Title. NFPA 101, Life Safety Code, shall be known as the Life Safety Code, is cited as such, and shall
TOWN OF CARY Lochmere PUD Amendment -Greensview Tract 00-REZ-31 FINAL CONDITIONS APPLICANT(S) OWNER(S) OWNER(S) Preston Creative School, LLC c/o Mr. Jim Fauver 110 Preston Grande Way Morrisville, NC 27560
Changes in NFPA 72-2002 2002 Oregon Fire Code Committee November 25, 2003 Michael B. Baker, SET Automatic Fire Alarm Association MikeBaker@afaa.org 2003 Michael B. Baker 1 Table of Contents 1. Administration
Section 5a MONTECITO FIRE PROTECTION DISTRICT FIRE PROTECTION PLAN Residential Automatic Fire Sprinkler System Installations I Automatic Fire Sprinkler System Standards 1. Definition and Standard: An automatic
Short Term Accommodations Fire Code Requirements 1 Foreward The following is a comprehensive reference to Retrofit 9.3 of Division B of the Ontario Fire Code (OFC). Retrofit provisions were developed to
SECTION 21. MU-VS MIXED USE VIRGINIA SQUARE DISTRICTS The purpose of the MU-VS Mixed Use Virginia Square classification is to encourage coordinated mixed-use development of medium-density residential and
CHAPTER 4 EMERGENCY PLANNING AND PREPAREDNESS SECTION 401 GENERAL 401.1 Scope. Reporting of emergencies, coordination with emergency response forces, emergency plans and procedures for managing or responding
SECTION 21 13 13 WET-PIPE SPRINKLER SYSTEMS PART 1 - GENERAL 1.1 SCOPE OF WORK A. Design, installation and testing shall be in accordance with NFPA 13 except for specified exceptions. B. The demolition
Sec. 8-3066. Visual buffers and screening. (a) Generally. Buffers shall be provided as set forth herein to effectively protect all property from the adverse effects of adjacent land use activity of a more
REZONING APPLICATION MPD SUPPLEMENT For Staff Use Only: DATE/TIMESTAMP: ZA# RECEIVED BY: The intent of the Master Planned District (MPD) designation is to allow flexibility in the design and construction
OPTIONAL INFORMATION Name of School: Date of Inspection: Vocational Program/Course/Room: Signature of Inspector: PORTABLE FIRE EXTINGUISHERS Guidelines: This checklist covers the "Uniform Fire Code" regulations
Sidewalk Café Guidelines The following Guidelines provide standards for the design, establishment and maintenance of Sidewalk Cafés in Edmonton. The intent is to encourage the use of public spaces to advance
CITY OF MONTRÉAL BY-LAW 95-065 BY-LAW AMENDING THE BUILDING BY-LAW (B-1) At the Montréal city council meeting of April 10, 1995, it was enacted that: 1. Article 3 of the Building By-law (R.B.C.M., chapter
5.01- Fire Department Recognized 5.02- Organization 5.03- Membership 5.04- Fire Chief 5.05- Chief Fire Inspector 5.06- Assistant Fire Chief, Fire Inspector, Captain, Lieutenant, Fire Fighters, EMS Personnel
Code Reference NFPA 101 22.214.171.124 (2009 126.96.36.199 (2012 1.1.7 (New) 188.8.131.52 Florida Specific Amendment Anytime a reference is made to NFPA 1 or NFPA 101 within this Code, it shall be the Florida specific version
LC00 01 -- S S T A T E O F R H O D E I S L A N D IN GENERAL ASSEMBLY JANUARY SESSION, A.D. 01 A N A C T RELATING TO HEALTH AND SAFETY - FIRE SAFETY Introduced By: Senator Ryan W. Pearson Date Introduced:
(Bill No. 160462) AN ORDINANCE Amending Subcode A (The Philadelphia Administrative Code), Subcode F (The Philadelphia Fire Code) and Subcode PM (The Philadelphia Property Maintenance Code) of Title 4 of
CHAPTER 13 PERFORMANCE COMPLIANCE METHODS SECTION 1301 GENERAL 1301.1 Scope. The provisions of this chapter shall apply to the alteration, repair, addition and change of occupancy of existing structures,
Fire Flow Water Consumption In Sprinklered and Unsprinklered Buildings: An Assessment of Community Impacts Prepared by: Code Consultants, Inc. The Fire Protection Research Foundation One Batterymarch Park
Moreno Valley Fire Department Fire Prevention Bureau Residential Based Care Facility Guidelines Approved and Authorized By: Randall Metz, Fire Marshal Issued: January 1, 2011 Residential Based Care Facilities
Introduction / Written Statement McDonald s Restaurant - Purcellville McDonald s Corporation is proposing to redevelop the existing McDonald s eating establishment with a drive-through located at 121 N
180 ZONING 180 ARTICLE XLII STREETSCAPE ENHANCEMENT OVERLAY ( SEO ) DISTRICT [Added 4-6-2016 Ord. No. 1086] 180.145. SEO DISTRICT 180.145.1. Intent. The SEO DISTRICT Regulations are intended to address
LOS ANGELES MISSION COLLEGE MASTER PLAN DESIGN & DEVELOPMENT PRINCIPLES 34 Quality Learning Along the Arroyo PROGRAM SUMMARY BY PROJECT The following are program summaries for each of the projects planned
FIRE FIGHTER II APPLICATION PENNSYLVANIA VOLUNTARY FIRE SERVICE CERTIFICATION PROGRAM NFPA 1001 2008 Edition SECTION I Last Name First Name M.I. SSN (last four digits required) Street Address City State
6 STANDARDS THAT APPLY TO ALL OR SOME DEVELOPMENT PROJECTS WITH RESIDENTIAL USES STANDARDS THAT APPLY TO ALL OR SOME DEVELOPMENT PROJECTS WITH RESIDENTIAL USES 6-1 Figure 6-1: Parking Stall Width 9 Stall
Temporary LPG Heat for Construction Sites Work At Risk and Inspection Information Packet Colorado Springs Fire Department Division of the Fire Marshal December 2013 W:\Packets\Haz Mat\IFC2009_Work_At_Risk_Temp_LPG_Heat
SOCIAL ACCOUNTABILITY ACCREDITATION SERVICES To: All SAAS Accredited Certification Bodies Subject: Clarification to Emergency and Health & Safety Requirements in the SA8000 Standard Background: After an
City of Fairfax, Virginia City Council Work Session Agenda Item # WS 2 City Council Meeting 7/5/2016 TO: FROM: SUBJECT: Honorable Mayor and Members of City Council Robert Sisson, City Manager Request of
INTRODUCTION AND ACKNOWLEDGMENTS This manual is designed as a basic guide to be used by paver laying contractors. The format of the manual and much of the information contained herein are taken from the
CHAPTER 12 COMPLIANCE ALTERNATIVES SECTION 1201 GENERAL 1201.1 Scope. The provisions of this chapter are intended to maintain or increase the current degree of public safety, health, and general welfare
ORDINANCE NO. 2005-02 ADOPTING FIRE PREVENTION REGULATIONS FOR THE PURPOSE OF GOVERNING CONDITIONS HAZARDOUS TO LIFE AND PROPERTY FROM FIRE OR EXPLOSION, AND ESTABLISHING A BUREAU OF FIRE PREVENTION BE
COMMERCIAL SITE PLAN SUMMARY & DEVELOPMENT GUIDE DEPARTMENT CONTACT: York County Development Coordinating Center (c/o Bea McCarter) 1070 Heckle Boulevard, Suite 107 Rock Hill, South Carolina 29732 Phone
Terry E. Branstad Governor Kim Reynolds Lt. Governor Department of Public Safety Roxann M. Ryan Commissioner Liquid Propane Informational guide to submitting plans Plans are to be submitted to: State Fire
Moab Municipal Code Chapter 17.32 SAR, SENSITIVE AREA RESORT ZONE Page 1 of 8 Sections: 17.32.010 Objectives and characteristics. 17.32.020 Use regulations. Chapter 17.32 SAR, SENSITIVE AREA RESORT ZONE