1 Duct smoke housing, 2-wire D340/D340P en Installation manual
3 Duct smoke housing, 2-wire Notices en 3 1 Notices These instructions cover the installation of the D340 Duct smoke housing and D340P Duct smoke kit in a fire system supervised by a fire alarm control panel (FACP) or a combination Burglary/Fire control panel. Before installing the module, become familiar with the Installation and Operation Guide for the control panel you are using.! Warning! Follow these instructions to avoid personal injury and damage to equipment. Install, test and maintain the module according to these instructions, NFPA codes, local codes, and the authority having jurisdiction (AHJ). Failure to follow these instructions can result in failure of a detector to initiate an alarm event. Bosch Security Systems, Inc. is not responsible for improperly installed, tested or maintained devices. NFPA 72 requires that you perform a complete system wide functional test following any modifications, repair, upgrades or adjustments made to the system s components, hardware, wiring, programming and software/firmware. Trademarks All hardware/software product names used in this document are likely to be registered trademarks and must be treated accordingly. Bosch Security Systems, Inc. Installation manual F.01U
4 4 en Description Duct smoke housing, 2-wire 2 Description 2.1 Overview The D340 Duct smoke housing is designed to mount to the ducts of heating, ventilation, and air-conditioning (HVAC) systems to monitor the presence of smoke in the conditioned air. It operates on a two wire loop, and requires a smoke detector head. Use the housing with the D285DH Duct smoke head (provided separately or with the D340P kit). The detector is combined with an efficient housing design to sample the air passing through a duct and detect potentially hazardous conditions. When it detects smoke, the detector sends an alarm signal to the control panel. The control panel initiates the necessary action to shut off fans and blowers or to switch to other air handling systems. Test the system by placing an external magnet on the housing or by turning the D344 RT s key switch to TEST. Reset control requires a 24 V supply from the control panel or an external power supply. You can reset the detector by shutting down zone power. If your system has a D344 RT Remote test/indicator plate, you can reset the system using the key switch. The D340 includes: One housing, power card, and cover assembly Two #10-24 x 1 in. machine screws for mounting Two #10-24 jack nuts One exhaust tube Two tube clamps with four screws Two foam gaskets Two air filters One drilling template One cover gasket The D340P also includes a smoke detector head and 1.5 ft (0.5 m) tube. 2.2 Compatibilities Bosch Security Systems, Inc. (Bosch) makes no claim either written, oral, or implied that the D340 Duct smoke housing with its associated D285DH Duct smoke head works with any control panel other than those listed in the Two wire Smoke Detectors Technical Service Note that covers the following products: D285, D285TH, D285DH, D286, D263, D263TH, D263THC, D263THS smoke detectors D603, D604, D605 heat detectors D340 Duct smoke detector housing Two wire smoke detector compatibility information is available in the documents for this product on our website ( The D340 Duct smoke housing with its associated D285DH Duct smoke head are compatible with the following accessory products: Accessory products Active: D Sample tube, duct 1.5ft/45.7cm D344-3 Sample tube, duct 3ft/91.4cm D344-5 Sample tube, duct 5ft/152cm D344-RL Remote indicator plate F.01U Installation manual Bosch Security Systems, Inc.
5 Duct smoke housing, 2-wire Description en 5 Accessory products D344-RT Remote test/indicator plate, 24V D344-TF Duct tube filters, 20pcs DRA-5 Remote indicator plate, 5V PAM-4 Relay module, form C, 10A 12/24V Legacy:* D306 Remote Indicator Plate D307 Remote Test and Indicator Plate SMK-TM Smoke Test Magnet * Legacy products are not available for purchase. 2.3 Setting the jumpers For the locations of the tamper jumper and reset jumper on the power card, see the following figure. Figure 2.1: Jumper locations 1 Power card 2 Tamper jumper 3 Reset jumper The tamper jumper enables or disables the housing cover tamper switch. When this jumper is enabled, a trouble is indicated if the cover is removed. The reset Jumper enables or disables the remote reset (D344-RT keyswitch). The power off reset from the control panel zone functions normally regardless of the jumper setting. Notice! Disable the reset jumper whenever you are not using the D344-RT (D307). Bosch Security Systems, Inc. Installation manual F.01U
6 6 en Description Duct smoke housing, 2-wire For enabled and disabled jumper positions, see the following figure. Figure 2.2: Jumper settings 1 Disabled 2 Enabled F.01U Installation manual Bosch Security Systems, Inc.
7 Duct smoke housing, 2-wire Mounting en 7 3 Mounting 3.1 Preparing the duct Before installing the duct detector, you must verify the duct air flow and velocity. The detector is designed for use in air handling systems with air velocities between 300 ft/min and 4000 ft/ min (1.5 m/s to 20.3 m/s). Check the HVAC engineering specifications to ensure the air velocity in the duct falls within these parameters. If necessary, use a velocity meter to check the air velocity in the duct. 3.2 Determining mounting location To obtain a representative air sample, avoid stratification and dead air space. These conditions can be caused by return duct openings, sharp turns, connections, or long, uninterrupted runs. For this reason, place the duct housing in the range of six to ten times the width of the duct from any uninterrupted run (see the following figure). Figure 3.1: Typical duct detector placement 1 Bend or other obstruction 2 6 to 10 times the width oft he duct 3 Width of duct 4 Return air inlet The D340 can be mounted in any direction of 90 increments without regard to the air flow direction (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
8 8 en Mounting Duct smoke housing, 2-wire Figure 3.2: Mounting positions 1 Air flow 2 Acceptable mounting positions 3 Unacceptable mounting positions 3.3 Preparing sample tubes The sample tubes must extend across the width of the duct. The three sizes of sample tubes are: D (1.5 ft [0.46 m]) D344-3 (3 ft [0.91 m]) D344-5 (5 ft [1.52 m]) Sample tubes include an end plug that must be installed in the narrow end of the tube (see the following figure). Figure 3.3: Sample tube 1 Set screw 2 End plug When using the D in installations where the duct width is between 12 in. (31 cm) and 18 in. (46 cm), cover some of the sample holes. The D has 19 sample holes, but only 12 are required for normal installations. Depending on the length, you might have to cover some of the holes with duct tape. Use even spacing when covering the sample holes to allow an even sample across the width of the duct (see the following figure). Figure 3.4: Covering sample tube holes F.01U Installation manual Bosch Security Systems, Inc.
9 Duct smoke housing, 2-wire Mounting en 9 1 Place tape over these sample holes You can combine or cut sample tubes to make different lengths. A sample tube can be a maximum length of 10 ft (3 m) or a minimum length of 1 ft (0.3 m). For example, you can join a 3 ft (1 m) and a 5 ft (1.5 m) to make an 8 ft (2.4 m) sample tube. Notice! Sample tubes must have at least 12 sample holes within the duct. Do not cut a sample tube to less than 12 sample holes. Notice! Sample tubes over 3 ft (1 m) must be supported at the end opposite the duct detector. The support hole should be 1 in. to 2 in. (2.5 cm to 5 cm) below the entry hole to allow for possible moisture drainage (see the figure following step 4 of the following procedure). To combine sample tubes: 1. Remove the roll pin and set screw from one of the sample tubes. 2. Remove the end plug from the other sample tube. 3. Push the flared end over the sample tube you want to lengthen. 4. Align the holes, insert the set screw, and reinstall the end plug. For example, if you want a 7 ft (2 m) sample tube, combine a 3 ft (1 m) sample tube and a 5 ft (1.5 m) sample tube. Then cut 1 ft (0.3 m) from the narrow end to get the necessary length. Figure 3.5: Support hole position 1 1 in. to 2 in. (2.5 cm to 5 cm) 5. Seal the gap between duct and sample tube. You can remove up to 6 in. (15 cm) from the D for 1 ft (0.3 m) duct installations. 3.4 Mounting the detector 1. Locate the D340 mounting template and remove it from its backing. Place the template over the desired location on the duct (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
10 10 en Mounting Duct smoke housing, 2-wire Figure 3.6: Mounting template placement 1 Duct 2 Mounting template in. (40.8 cm) 4 Two in. (9.5 mm) holes for mounting the housing to the duct 5 Two 1.75 in. (45 mm) diameter holes for the sample tubes in. (16.6 cm) 2. Drill out the required holes and remove any remaining debris. 3. Remove the template. 4. Place a #10 24 jack nut (see the following figure) in each of the 3/8 in. (9.5 mm) holes. Figure 3.7: Jack nuts 5. Insert the #10-24 x 1 in. machine screws into the jack nuts and firmly tighten. This attaches the jack nuts to the duct. You might have to hold the jack nuts with a installer wrench or a pair of pliers while tightening the screws to stop the jack nut from spinning in the hole. Remove the screws for later use. 6. Place the two foam gaskets over the sample and exhaust ports on the back of the housing (see the following figure) F.01U Installation manual Bosch Security Systems, Inc.
11 Duct smoke housing, 2-wire Mounting en Figure 3.8: Foam gaskets 1 Sample/exhaust tube posts 2 Foam gaskets 7. Mount the housing to the jack nuts using the supplied machine screws (see the following figure). Remember that over tightening the screws can cause excessive bowing of the duct. Figure 3.9: Mounting the housing 1 Duct 2 Housing 3 Machine screws (supplied) 8. Determine and remove the appropriate wire knockouts for power and for any remote indicator wiring (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
12 12 en Mounting Duct smoke housing, 2-wire Figure 3.10: Wiring knockouts and earth ground 1 Wiring knockouts 2 Earth ground screw 9. Locate the sample and exhaust tubes (see the following figure). Ensure the sample tube has a plug installed at the narrow end of the assembly. Figure 3.11: Exhaust/sample tubes 1 Exhaust tube 2 Sample tube 3 Leave end open 4 Insert plug 10. Note the direction of the airflow in the duct. The sampling holes in the sample tube must face into the air flow (see the first figure below). The exhaust tube must exhaust downwind from the sample tube (see the second figure below) F.01U Installation manual Bosch Security Systems, Inc.
13 Duct smoke housing, 2-wire Mounting en 13 Figure 3.12: Airflow direction 1 Sample tube 2 Airflow direction 3 Sampling holes Figure 3.13: Exhaust/sample tube placement 1 Exhaust tube 2 Sample tube 3 Airflow direction 11. Insert the sample and exhaust tubes into the housing, ensuring the sample tube holes face into the air flow. Ensure the tube alignment point set into the housing. 12. Secure the tubes in place using the tube clamps provided (see the following figure). Figure 3.14: Mounting tubes in housing Bosch Security Systems, Inc. Installation manual F.01U
14 14 en Mounting Duct smoke housing, 2-wire 1 Exhaust tube 2 Sample tube 3 Housing 4 Tube clamps 13. Place the tube filters over the open ends of the sample and exhaust tubes (see the following figure). Figure 3.15: Tube filters 1 Exhaust tube 2 Sample tube 3 Housing 4 Tube filters F.01U Installation manual Bosch Security Systems, Inc.
15 Duct smoke housing, 2-wire Wiring en 15 4 Wiring The housing/detector is designed for a two wire loop power ranging from 8.5 VDC to 32 VDC. For use with the D344-RT Remote test/indicator plate or The DRA-5 Remote indicator plate, you must use an external 24 VDC/VAC that can supply a minimum of 170 ma. For terminals for power wiring, see the following figure. Figure 4.1: D340 terminal wiring 1 Optional external power (24 VAC/VDC) 2 Remote LED 3 Loop (+) 4 Loop (-) 4.1 Wiring to the D344-RT Notice! NFPA Requirement NFPA-72 requires that where in duct smoke detector housings are installed in concealed locations more than 10 ft (3 m) above the finished floor or in arrangements where the detector s alarm indicator is not visible to responding personnel, the detectors have remote alarm indicators. Notice! Do not exceed 500 ft (152 m) between the D344-RT (D307) Remote test/indicator plate and the D340 housing. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire. Bosch Security Systems, Inc. Installation manual F.01U
16 16 en Wiring Duct smoke housing, 2-wire Figure 4.2: D340 to D344-RT wiring 1 Voltage in (+) 2 Voltage out (-) 3 Yellow LED 4 Voltage monitor 5 Ground (-) 6 Remote test 7 Green LED 8 Red LED 9 D D344-RT (D307) 4.2 Wiring to the D344-RL Notice! Do not exceed a distance of 500 ft (152 m) between the D344-RL (D306) Remote indicator plate and the D340. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire F.01U Installation manual Bosch Security Systems, Inc.
17 Duct smoke housing, 2-wire Wiring en 17 Figure 4.3: D340 to D344-RL wiring 1 D340 power card 2 D344-RL (D306) 3 Yellow wire 4 Violet wire 5 Black wire [ground (-)] 6 Terminal 6 is not used 7 Green wire 8 Red wire 4.3 Wiring to the DRA-5 Notice! Do not exceed a distance of 500 ft (150 m) between the DRA-5 Remote indicator plate and the D340 housing. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire. Figure 4.4: D340 to DRA-5 wiring 1 Optional external power (24 VAC/VDC) 2 Remote LED 3 Loop (+) 4 Loop (-) 5 DRA-5 6 White wire 7 Red wire Bosch Security Systems, Inc. Installation manual F.01U
18 18 en Wiring Duct smoke housing, 2-wire 4.4 Wiring to the FACP Figure 4.5: D340 to FACP wiring 1 FACP 2 Alarm initiating loop 3 EOL resistor 4.5 Wiring for external power Notice! Connect the ground wire to the screw on the ground plate when using grounded three-wire AC wiring (see step 8 of the mounting procedure in Mounting the detector, page 9). Figure 4.6: Wiring D340 to FACP and external power 1 FACP 2 Alarm initiating loop 3 External power (24 VAC/VDC) 4 EOL resistor F.01U Installation manual Bosch Security Systems, Inc.
19 Duct smoke housing, 2-wire Testing and maintenance en 19 5 Testing and maintenance 5.1 Testing the installation Verify the airflow to ensure the system is properly operating. Use a manometer to verify the correct velocity pressure readings ranging from 300 ft/min to 4000 ft/min (1.5 m/s to 20 m/s). The pressure differential between sampling tubes is a minimum of 0.01 in. (0.25 mm) of water to a maximum of 1.8 in. (45.7 mm) of water. 1. Check the wiring from the control panel to the last duct detector on each run for proper polarity and continuity. 2. Ensure each run terminates with an EOL resistor as specified by the control panel manufacturer. 3. Apply power to the system, and check for alarms. Note which smoke detectors are in alarm (if any) and shut down the system. Remove these detectors from their duct housing and recheck the duct housing for proper wiring. If the problems persist, replace the affected smoke detectors or swap them with known good units. This determines if the problem is caused by the detector or the duct housing. If there is a system alarm with no detector alarms present, remove all smoke detectors and check the wiring at each duct housing. Pay close attention to the wiring of each EOL resistor. 4. When the system is free of alarms, check each detector to ensure the red LED indicator flashes approximately every 4 sec for the D285DH. This verifies the detector is receiving power and properly operating. 5. Test each detector to ensure it causes a control panel alarm. Reset the control panel after each test. Test the detectors by doing one of the following: Place a magnet against the duct housing s test point notch on the front cover (see the following figure). Figure 5.1: Testing the detector 1 Magnet 2 Test point notch 3 Detector 4 Housing Bosch Security Systems, Inc. Installation manual F.01U
20 20 en Testing and maintenance Duct smoke housing, 2-wire Switch a signal from a D344-RT (D307) Remote test/indicator plate. Notice! When a detector alarms, the red LED indicator activates and latches to the ON position. Clear the alarm before proceeding to the next detector. 5.2 Maintenance 6. You can reset the detector by momentarily removing power. 7. For duct detectors with the D344-RT (D307) Remote test/indicator plate installed, reset by moving the keyswitch to the appropriate position and observing the alarm LED. 8. Check the overall loading of the alarm loop by measuring the voltage across each EOL resistor. This voltage should equal or exceed the minimum specified by the control panel manufacturer. Notice! NFPA Requirement NFPA-72 requires a semi annual visual inspection of detector housings. Clean or replace the tube filters at this time. If replacement filters are needed, order the D344-TF. Notice! Notify all concerned parties before and after completing maintenance on or testing of the fire alarm system. Clean the detector and base annually using a vacuum or with clean, dry compressed air F.01U Installation manual Bosch Security Systems, Inc.
21 Duct smoke housing, 2-wire Specifications en 21 6 Specifications Electrical Current (alarm) Maximum RMS Ripple Power-up time Voltage, operating Dependent on the control panel that must limit the alarm current to 100 ma maximum. 25% of DC input 22 sec maximum 8.5 VDC to 32 VDC from two-wire loop. Optional 24 VDC/VAC from control panel or external supply. D340 with D344-RT, D344-RL, and External Power Loop power External power 8.5 V to 32 V 24 V Condition Alarm Current limit to 100 ma 170 ma in remote test Standby < ma 5 ma Trouble < ma ma D340 with D344-RT, D344-RL without External Power Loop power 8.5 V to 32 V Condition Alarm Current limit to 100 ma Standby < ma Trouble < ma D340 without D344-RT, D344-RL without External Power Loop power 8.5 V to 32 V Condition Alarm Current limit to 100 ma Standby < ma Trouble < ma Environmental Air velocity Relative humidity Temperature, operating 300 ft./min to 4000 ft./min (1.5 m/s to 20.3 m/s) 0% to 95%, non-condensing +32F to +120 F (0 C to +49 C). For UL listed requirements, the operating temperature range is +32 F to +100 F (0 C to C). Bosch Security Systems, Inc. Installation manual F.01U
22 22 en Specifications Duct smoke housing, 2-wire Mechanical Package Dimensions (LxWxH) Product Dimensions (LxWxH) Material Weight Gross Net 18.9 in. x 7.5 in. X 7.8 in. (48 cm x 19 cm x 19.8 cm) 15.5 in. x 4.3 in. x 6.5 in. (39.5 cm x 11 cm x 16.5 cm) High impact fire retardant polymer plastic 4.23 lb. (1.92 kg) 3.84 lb. (1.74 kg) F.01U Installation manual Bosch Security Systems, Inc.
24 Bosch Security Systems, Inc. 130 Perinton Parkway Fairport, NY USA Bosch Security Systems, Inc., 2017 Bosch Sicherheitssysteme GmbH Robert-Bosch-Ring Grasbrunn Germany
Notification Appliance Circuit Module D192G en Installation guide Notification Appliance Circuit Module Notices en 3 1 Notices These instructions cover the installation of the D192G Notification Appliance
INSTALLATION AND MAINTENANCE INSTRUCTIONS Ionization Air Duct Smoke Detector Before Installing Please thoroughly read the System Sensor Guide for Proper Use of Smoke Detectors in Duct Applications (A05-1004),
Installation Instructions Notice Addressable NAC Output Module D327A These instructions cover the installation of the D327A Addressable NAC Output Module in an analog system controlled by a Bosch D8024,
INSTALLATION AND MAINTENANCE INSTRUCTIONS Air Duct Smoke Detector with Extended Air Speed Range A Division of Pittway 825 Ohio Avenue, St. Charles, Illinois 60174 1-800-SENSOR2, FAX: 60-77-6495 The Innovair
D EN Installation Instructions Multiplex Dual Input Module D Installation Instructions Notices Notices Figure : D Features These instructions cover the installation of the D Multiplex Dual Input Module
D EN Installation Instructions Multiplex Single Input Module D Installation Instructions Notices Notices These instructions cover the installation of the D Multiplex Single Input Module in a fire system,
Installation Manual: PAD100-DUCTR Analog Addressable Duct Detector NOTICE TO THE INSTALLER This manual provides an overview and the installation instructions for the PAD100-DUCTR module. This module is
D EN Installation Instructions Multiplex Input/Output Module D Installation Instructions Notices Notices These instructions cover the installation of the D Multiplex Input/Output Module in a fire system
TEST LOG Detector Identification Information Manufacturer and Serial Date Detector Model: Number: Installed: Description of Detector Location: Test Results and Maintenance Data Date Test Test Maintenance
Commercial Series riech Motion Detector en Reference Guide Commercial Series riech Motion Detector able of contents en 3 able of contents 1 Safety 4 Introduction 5.1 About documentation 5. Bosch Security
Photobeam 5000 ISC-FPB-W60QF, ISC-FPB-W0QF, ISC-FPB-W00QF en Installation and Operation Guide Photobeam 5000 Table of Contents en 3 Table of contents Introduction 4. About documentation 4. Bosch Security
INSTALLATION AND MAINTENANCE INSTRUCTIONS DH200PL Intelligent Air Duct Smoke Detector with Extended Air Speed Range 3825 Ohio Avenue, St. Charles, Illinois 60174 800/736-7672, FAX: 630-377-6495 www.systemsensor.com
Cautions and Warnings DO NOT INSTALL ANY SIMPLEX PRODUCT THAT APPEARS DAMAGED. Upon unpacking your Simplex product, inspect the contents of the carton for shipping damage. If damage is apparent, immediately
ISC-PDL1-W18G-H EN Installation Instructions Professional Series Dual Detector 1.0 General Information 1.1 Unlock and remove the cover The ISC-PDL1-W18x Professional Series TriTech Detectors are exceptionally
INSTALLATION AND MAINTENANCE INSTRUCTIONS I56-3642-000R DNR-AUS Duct Smoke Detector Specifications Operating Temperature: 20 to 70 C ( 4 to 158 F) 0 C to 49 C (32 F to 120 F) with module installed in the
Microwave/PIR Intrusion Detector with POPIT Interface ZX970 Installation Instructions 1.0 Specifications Input Power: 9 to 15 VDC, 6 ma nominal (35 ma with LED on) Zonex Current Draw: 500 ma Standby Power:
574-776 Rev. C 4098-9685, -9686, -9688, -9755, -9756 Duct Detector/Sensor Installation Instructions Blank Page Cautions and Warnings DO NOT INSTALL ANY SIMPLEX PRODUCT THAT APPEARS DAMAGED. Upon unpacking
D96/D97 EN Installation Instructions Long-Range Beam Smoke Detectors D96/D97 Installation Instructions.0 Description FCC Compliance Notice This equipment was tested and complies with the limits for a Class
EN Operators Guide Universal Timer Module Operators Guide Notices EN Copyright Notice Unless otherwise indicated, this publication is the copyright of Bosch Security Systems, Inc. ( Bosch ). All rights
Fire Alarm Control Panels FPD-7024 en Release Notes Fire Alarm Control Panels Table of contents en 3 Table of contents 1 Short description 4 2 Release notes for v1.06.01 5 2.1 New Features 5 2.2 Issues
Installation PS6 SERIES Power Supplies PS6 SERIES Power Supplies c/w Fire Panel Interface, EOL Trigger and Standby Power Option Installation and Specifications Manual ISDPS6_SERIES 08121590 PCN15016 R05/15GR
AIR PRODUCTS AND CONTROLS You in Control AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SERIES DUCT SMOKE DETECTORS -N 4-Wire, Ionization Type -P 4-Wire, Photoelectric Type
CRSMKKIT002A00 CRSMKSEN002A00 FIELDINSTALLEDSMOKEDETECTORS FOR MEDIUM ROOFTOP UNITS 15 to 25 TONS Installation Instructions TABLE OF CONTENTS PACKAGE CONTENTS... 1 SAFETY CONSIDERATIONS... 1 GENERAL...
Installation and Maintenance Instructions I56-900-005 MMF-0-6 Six Zone Interface Module SPECIFICATIONS Normal Operating Voltage: 5- VDC Stand-By Current: ma Alarm Current: 40 ma (assumes all six LEDs solid
DS3MX-E-I EN Installation Guide 3 Mini Control Panel DS3MX-E-I Installation Guide 1.0 General Information EN 2 1.0 General Information The DS3MX is a three zone mini control panel, which can be installed
AIR PRODUCTS AND CONTROLS You in Control AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SERIES PLENUM DUCT SMOKE DETECTORS NO-FLOW LOW-FLOW SPECIAL APPLICATION -N -P PRODUCT
FACTORY INSTALLED SMOKE DETECTORS FOR SMALL AND MEDIUM ROOFTOP UNITS 2TO25TONS Application Data TABLE OF CONTENTS PAGE SAFETY CONSIDERATIONS... 1 PART NUMBERS... 1 APPLICABLE UNITS... 1 GENERAL... 2 DESCRIPTIONS...
DS160/161 Request To Exit PIR sensors Installation Instructions 1.0 Description The DS160/161 is a passive-infrared (PIR) detector designed for request to exit (REX) interior applications. It is UL Listed
TS EMR WITH SMOKE GENERAL DESCRIPTION Each TS EMR series unit contains a door closer, hold open electromagnet and smoke detector. The unit can be used as a single installation or as a series of singles
- + - + - + 1. Description This document provides instructions for mounting and wiring the Detector Bases PAD100-, PAD100-RB and PAD100-SB. The following detectors are compatible with Detector Bases PAD100-,
II 1400-2 ACSI 1406-04-AO ELECTRIC LATCH RETRACTION CONTROLLER INSTALLATION INSTRUCTIONS I.D. 1089, REV. F INSTALLATION Transformer Model BE31763001 by Basler Electric, Transformer Model 2010028 by Galaxy
D1255RB/D1256RB/D1257RB EN Installation Instructions Fire Keypads and Fire Alarm Annunciator D1255RB/D1256RB/D1257RB Installation Instructions Listings and Approvals Listings and Approvals UL 365 UL 609
PNC 1000 SERIES 2, 4, 8 Zone Fire Alarm Control Panel INSTALLATION, OPERATION AND MAINTENANCE MANUAL Version: CN-PM-1000.VER1.1-12/2012 EN54 INFORMATION In accordance with EN 54-2 clause 13.7, the maximum
INSTALLATION PDD-8PCI PDD-8PCI Power Distribution Board With Supervised Interface Installation and Specifications Manual Details The PDD-8PCI board is a power distribution/control interface. This board
HE220, HE260 Humidifier Installation Kit WELCOME To the comfortable world of humidified air. When you use your Honeywell humidifier, you notice that your skin is not as dry, and that your scratchy throat
Installation Instructions Azatrax Dual Infrared Model Train Detector MRD2 'Turnout' Edition What it is: The MRD2 'turnout' edition is a two-channel model train detector. It can detect model trains at two
Specification/ Data Sheet TRITON RP Agent Release Control Panel FEATURES Agent Release Control Panel designed specifically for suppression release operation with: Four initiating device circuits (IDCs)
Control Panels D9412GV4/D7412GV4/D7212GV4 en Approved Applications Compliance Guide GV4 Series Approved Applications Compliance Guide Listings and Approvals GV4 Listings and Approvals Fire UL The D9412GV4
General Routing Interface Features The General Routing Interface Card is an optional module to provide Fire and Fault Routing Outputs compliant with BSEN54-2: 1998 Clauses 7.9 and 8.9 and BS5839-1: 2002.
AL600ULADA NAC Power Extender Installation Guide Rev. 122000 AL600ULADA - NAC Power Extender Overview: The Altronix AL600ULADA is an extremely cost effective 6.5 amp voltage regulated remote power supply/battery
SAFE A N D SECURE Cornell 100 Elmwood Ave. Crestwood Industrial Park Mountaintop, PA 18707 Tel 800.233.8366 Fax 800.526.0841 Email: email@example.com O W N E R S M A N U A L M O D E L F I R E G A
AIR PRODUCTS AND CONTROLS You in Control AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SM-501 SERIES DUCT SMOKE DETECTORS SM-501-N 4-Wire, Ionization Type SM-501-P 4-Wire,
HE360 Humidifier Installation Kit INSTALLATION INSTRUCTIONS WELCOME To the comfortable world of humidified air. When you use your Honeywell humidifier, you notice that your skin is not as dry, and that
SECTION 16721 FIRE ALARM SYSTEMS PART 1 - GENERAL 1.01 RELATED DOCUMENTS A. The general provisions of the contract including General and Special Conditions and General Requirements shall apply to all work
LASER ASPIRATED SMOKE DETECTOR LASD1 (Single Channel) INSTALLATION, OPERATION & MAINTENANCE INSTRUCTIONS (CE) 1 INTRODUCTION The LASD1 utilises one or two high-sensitivity laser point detectors in an aspirated
Cookson Company 1901 South Litchfield Road Goodyear, AZ 85338 Phone: 800-294-4358 www.cooksondoor.com O W N E R S M A N U A L MODEL FIREFLY III EXTENDED PERFORMANCE RELEASE DEVICE TABLE OF CONTENTS INTRODUCTION
Class A and Expansion NAC Modules Installation Instructions Introduction This publication describes the installation procedure for the following: 4100-1245 Flex Amplifier Expansion NAC (XNAC) 4100-1246
DT8050A DUAL TEC Motion Sensor with Anti-Mask - Installation Instructions QUICK LINKS Mounting Location Guidelines Open the Sensor Mount the Sensor Sensor Components and Settings Wire the Sensor Wiring
ZNS MICROPROCESSOR BASED CONVENTIONAL FIRE ALARM CONTROL PANEL Installation & Operation Manual The Gamewell Company 60 Pleasant Street Part No. 71774 Ashland, MA 01721 Issue 4 12/4/98 PROPRIETARY MATERIAL
End To End Optical Beam Smoke Detector Additional Information EN 1. Multiple Zone Wiring When using more than one System Controller on a single zone of a conventional Fire Control Panel (FCP), it is important
R IPS CARBO STEEL PIPE FIRE PROTECTIO PRODUCTS Electric Release Panel Wiring Tips 30.4 VICTAULIC IS A ISO 900 CERTIFIED COMPAY Model PDRP-00 Releasing Panels are compact single enclosure units containing
UL, ULC Approved* LifeAlarm Fire Alarm Controls 4009 IDNet NAC Extender for Control with IDNet Communications or Conventional NACs Features Provides additional notification appliance circuit (NAC) capacity
12 Clintonville Road Northford, CT 06472 (203) 484-7161 FAX: (203) 484-7118 LDM Series Lamp Driver Modules For Graphic Annunciation and Control Used with the System 500, System 5000, AM2020/AFP1010 and
Purpose/Application National and local safety standards and codes recognize the ability of air duct systems to transfer smoke, toxic gases, and flame from area to area. Sometimes smoke can be of such quantity
Control Panel D9412GV4/D7412GV4 v2.00 en UL Installation Instructions Control Panel Table of Contents en 3 Table of contents 1 Introduction 4 1.1 About documentation 4 1.2 Determine Bosch Security Systems,
PME Series Enclosures Battery Enclosure (BE) Field Upgrade Installation Instructions Effective: January, 2004 Alpha Technologies Power Alpha Technologies. Protecting The Power in Communications. Preface
Conventional Fire Alarm System 2014 V1.2 Product Overview Control Panel 2 Conventional Fire Panel GST102A 2 zone Fire panel GST104A 4 zone Fire panel GST108A 8 zone Fire panel GST116A 16 zone Fire Panel
Reflective Optical Beam Smoke Detector User Guide 1. Installation IMPORTANT NOTE: The infrared beam path MUST be kept clear of obstructions at all times! Failure to comply may result in the system initiating
Fire Alarm Systems Bosch EVAX System - High-rise Applications Bosch EVAX System - High-rise Applications Master panel with capability for multiple distributed panels Operates as stand alone or connected
UNC100 Integra Manual New Generation Building Security July 30, 2014 V1.2 Copyright Notice Copyright 1995-2014 by All rights reserved Worldwide. Printed in Canada. This publication has been provided pursuant
Introduction The CO Transmitter uses an electrochemical sensor to monitor the carbon monoxide level and outputs a field-selectable 4-20 ma or voltage signal. The voltage signal may also be set to 0-5 or
R 12 Clintonville Road, Northford, CT 06472 Phone: (203) 484-7161 FAX: (203) 484-7118 Instruction Manual for the MS-4012/4024 and CMS-4012/4024 Fire Alarm Control Panels Document 15586 5/11/93 Revision:
Easy Series Control Panel ICP-EZM2 en Quick Installation Guide Easy Series Control Panel Table of contents en 3 Table of contents 1 Install the Enclosure 4 2 Wire the Control Panel 6 3 Configure the System
Important: Read and save these instructions. This guide to be left with equipment. MES2 Installation and Operation Manual Includes installation, operation maintenance and troubleshooting information for
FireFlex 1230 description The FireFlex 1230 integrated system consists of a clean agent fire extinguishing system, factoryassembled in a cabinet and integrating all the components necessary for a complete