1 Duct smoke housing, 2-wire D340/D340P en Installation manual
3 Duct smoke housing, 2-wire Notices en 3 1 Notices These instructions cover the installation of the D340 Duct smoke housing and D340P Duct smoke kit in a fire system supervised by a fire alarm control panel (FACP) or a combination Burglary/Fire control panel. Before installing the module, become familiar with the Installation and Operation Guide for the control panel you are using.! Warning! Follow these instructions to avoid personal injury and damage to equipment. Install, test and maintain the module according to these instructions, NFPA codes, local codes, and the authority having jurisdiction (AHJ). Failure to follow these instructions can result in failure of a detector to initiate an alarm event. Bosch Security Systems, Inc. is not responsible for improperly installed, tested or maintained devices. NFPA 72 requires that you perform a complete system wide functional test following any modifications, repair, upgrades or adjustments made to the system s components, hardware, wiring, programming and software/firmware. Trademarks All hardware/software product names used in this document are likely to be registered trademarks and must be treated accordingly. Bosch Security Systems, Inc. Installation manual F.01U
4 4 en Description Duct smoke housing, 2-wire 2 Description 2.1 Overview The D340 Duct smoke housing is designed to mount to the ducts of heating, ventilation, and air-conditioning (HVAC) systems to monitor the presence of smoke in the conditioned air. It operates on a two wire loop, and requires a smoke detector head. Use the housing with the D285DH Duct smoke head (provided separately or with the D340P kit). The detector is combined with an efficient housing design to sample the air passing through a duct and detect potentially hazardous conditions. When it detects smoke, the detector sends an alarm signal to the control panel. The control panel initiates the necessary action to shut off fans and blowers or to switch to other air handling systems. Test the system by placing an external magnet on the housing or by turning the D344 RT s key switch to TEST. Reset control requires a 24 V supply from the control panel or an external power supply. You can reset the detector by shutting down zone power. If your system has a D344 RT Remote test/indicator plate, you can reset the system using the key switch. The D340 includes: One housing, power card, and cover assembly Two #10-24 x 1 in. machine screws for mounting Two #10-24 jack nuts One exhaust tube Two tube clamps with four screws Two foam gaskets Two air filters One drilling template One cover gasket The D340P also includes a smoke detector head and 1.5 ft (0.5 m) tube. 2.2 Compatibilities Bosch Security Systems, Inc. (Bosch) makes no claim either written, oral, or implied that the D340 Duct smoke housing with its associated D285DH Duct smoke head works with any control panel other than those listed in the Two wire Smoke Detectors Technical Service Note that covers the following products: D285, D285TH, D285DH, D286, D263, D263TH, D263THC, D263THS smoke detectors D603, D604, D605 heat detectors D340 Duct smoke detector housing Two wire smoke detector compatibility information is available in the documents for this product on our website ( The D340 Duct smoke housing with its associated D285DH Duct smoke head are compatible with the following accessory products: Accessory products Active: D Sample tube, duct 1.5ft/45.7cm D344-3 Sample tube, duct 3ft/91.4cm D344-5 Sample tube, duct 5ft/152cm D344-RL Remote indicator plate F.01U Installation manual Bosch Security Systems, Inc.
5 Duct smoke housing, 2-wire Description en 5 Accessory products D344-RT Remote test/indicator plate, 24V D344-TF Duct tube filters, 20pcs DRA-5 Remote indicator plate, 5V PAM-4 Relay module, form C, 10A 12/24V Legacy:* D306 Remote Indicator Plate D307 Remote Test and Indicator Plate SMK-TM Smoke Test Magnet * Legacy products are not available for purchase. 2.3 Setting the jumpers For the locations of the tamper jumper and reset jumper on the power card, see the following figure. Figure 2.1: Jumper locations 1 Power card 2 Tamper jumper 3 Reset jumper The tamper jumper enables or disables the housing cover tamper switch. When this jumper is enabled, a trouble is indicated if the cover is removed. The reset Jumper enables or disables the remote reset (D344-RT keyswitch). The power off reset from the control panel zone functions normally regardless of the jumper setting. Notice! Disable the reset jumper whenever you are not using the D344-RT (D307). Bosch Security Systems, Inc. Installation manual F.01U
6 6 en Description Duct smoke housing, 2-wire For enabled and disabled jumper positions, see the following figure. Figure 2.2: Jumper settings 1 Disabled 2 Enabled F.01U Installation manual Bosch Security Systems, Inc.
7 Duct smoke housing, 2-wire Mounting en 7 3 Mounting 3.1 Preparing the duct Before installing the duct detector, you must verify the duct air flow and velocity. The detector is designed for use in air handling systems with air velocities between 300 ft/min and 4000 ft/ min (1.5 m/s to 20.3 m/s). Check the HVAC engineering specifications to ensure the air velocity in the duct falls within these parameters. If necessary, use a velocity meter to check the air velocity in the duct. 3.2 Determining mounting location To obtain a representative air sample, avoid stratification and dead air space. These conditions can be caused by return duct openings, sharp turns, connections, or long, uninterrupted runs. For this reason, place the duct housing in the range of six to ten times the width of the duct from any uninterrupted run (see the following figure). Figure 3.1: Typical duct detector placement 1 Bend or other obstruction 2 6 to 10 times the width oft he duct 3 Width of duct 4 Return air inlet The D340 can be mounted in any direction of 90 increments without regard to the air flow direction (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
8 8 en Mounting Duct smoke housing, 2-wire Figure 3.2: Mounting positions 1 Air flow 2 Acceptable mounting positions 3 Unacceptable mounting positions 3.3 Preparing sample tubes The sample tubes must extend across the width of the duct. The three sizes of sample tubes are: D (1.5 ft [0.46 m]) D344-3 (3 ft [0.91 m]) D344-5 (5 ft [1.52 m]) Sample tubes include an end plug that must be installed in the narrow end of the tube (see the following figure). Figure 3.3: Sample tube 1 Set screw 2 End plug When using the D in installations where the duct width is between 12 in. (31 cm) and 18 in. (46 cm), cover some of the sample holes. The D has 19 sample holes, but only 12 are required for normal installations. Depending on the length, you might have to cover some of the holes with duct tape. Use even spacing when covering the sample holes to allow an even sample across the width of the duct (see the following figure). Figure 3.4: Covering sample tube holes F.01U Installation manual Bosch Security Systems, Inc.
9 Duct smoke housing, 2-wire Mounting en 9 1 Place tape over these sample holes You can combine or cut sample tubes to make different lengths. A sample tube can be a maximum length of 10 ft (3 m) or a minimum length of 1 ft (0.3 m). For example, you can join a 3 ft (1 m) and a 5 ft (1.5 m) to make an 8 ft (2.4 m) sample tube. Notice! Sample tubes must have at least 12 sample holes within the duct. Do not cut a sample tube to less than 12 sample holes. Notice! Sample tubes over 3 ft (1 m) must be supported at the end opposite the duct detector. The support hole should be 1 in. to 2 in. (2.5 cm to 5 cm) below the entry hole to allow for possible moisture drainage (see the figure following step 4 of the following procedure). To combine sample tubes: 1. Remove the roll pin and set screw from one of the sample tubes. 2. Remove the end plug from the other sample tube. 3. Push the flared end over the sample tube you want to lengthen. 4. Align the holes, insert the set screw, and reinstall the end plug. For example, if you want a 7 ft (2 m) sample tube, combine a 3 ft (1 m) sample tube and a 5 ft (1.5 m) sample tube. Then cut 1 ft (0.3 m) from the narrow end to get the necessary length. Figure 3.5: Support hole position 1 1 in. to 2 in. (2.5 cm to 5 cm) 5. Seal the gap between duct and sample tube. You can remove up to 6 in. (15 cm) from the D for 1 ft (0.3 m) duct installations. 3.4 Mounting the detector 1. Locate the D340 mounting template and remove it from its backing. Place the template over the desired location on the duct (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
10 10 en Mounting Duct smoke housing, 2-wire Figure 3.6: Mounting template placement 1 Duct 2 Mounting template in. (40.8 cm) 4 Two in. (9.5 mm) holes for mounting the housing to the duct 5 Two 1.75 in. (45 mm) diameter holes for the sample tubes in. (16.6 cm) 2. Drill out the required holes and remove any remaining debris. 3. Remove the template. 4. Place a #10 24 jack nut (see the following figure) in each of the 3/8 in. (9.5 mm) holes. Figure 3.7: Jack nuts 5. Insert the #10-24 x 1 in. machine screws into the jack nuts and firmly tighten. This attaches the jack nuts to the duct. You might have to hold the jack nuts with a installer wrench or a pair of pliers while tightening the screws to stop the jack nut from spinning in the hole. Remove the screws for later use. 6. Place the two foam gaskets over the sample and exhaust ports on the back of the housing (see the following figure) F.01U Installation manual Bosch Security Systems, Inc.
11 Duct smoke housing, 2-wire Mounting en Figure 3.8: Foam gaskets 1 Sample/exhaust tube posts 2 Foam gaskets 7. Mount the housing to the jack nuts using the supplied machine screws (see the following figure). Remember that over tightening the screws can cause excessive bowing of the duct. Figure 3.9: Mounting the housing 1 Duct 2 Housing 3 Machine screws (supplied) 8. Determine and remove the appropriate wire knockouts for power and for any remote indicator wiring (see the following figure). Bosch Security Systems, Inc. Installation manual F.01U
12 12 en Mounting Duct smoke housing, 2-wire Figure 3.10: Wiring knockouts and earth ground 1 Wiring knockouts 2 Earth ground screw 9. Locate the sample and exhaust tubes (see the following figure). Ensure the sample tube has a plug installed at the narrow end of the assembly. Figure 3.11: Exhaust/sample tubes 1 Exhaust tube 2 Sample tube 3 Leave end open 4 Insert plug 10. Note the direction of the airflow in the duct. The sampling holes in the sample tube must face into the air flow (see the first figure below). The exhaust tube must exhaust downwind from the sample tube (see the second figure below) F.01U Installation manual Bosch Security Systems, Inc.
13 Duct smoke housing, 2-wire Mounting en 13 Figure 3.12: Airflow direction 1 Sample tube 2 Airflow direction 3 Sampling holes Figure 3.13: Exhaust/sample tube placement 1 Exhaust tube 2 Sample tube 3 Airflow direction 11. Insert the sample and exhaust tubes into the housing, ensuring the sample tube holes face into the air flow. Ensure the tube alignment point set into the housing. 12. Secure the tubes in place using the tube clamps provided (see the following figure). Figure 3.14: Mounting tubes in housing Bosch Security Systems, Inc. Installation manual F.01U
14 14 en Mounting Duct smoke housing, 2-wire 1 Exhaust tube 2 Sample tube 3 Housing 4 Tube clamps 13. Place the tube filters over the open ends of the sample and exhaust tubes (see the following figure). Figure 3.15: Tube filters 1 Exhaust tube 2 Sample tube 3 Housing 4 Tube filters F.01U Installation manual Bosch Security Systems, Inc.
15 Duct smoke housing, 2-wire Wiring en 15 4 Wiring The housing/detector is designed for a two wire loop power ranging from 8.5 VDC to 32 VDC. For use with the D344-RT Remote test/indicator plate or The DRA-5 Remote indicator plate, you must use an external 24 VDC/VAC that can supply a minimum of 170 ma. For terminals for power wiring, see the following figure. Figure 4.1: D340 terminal wiring 1 Optional external power (24 VAC/VDC) 2 Remote LED 3 Loop (+) 4 Loop (-) 4.1 Wiring to the D344-RT Notice! NFPA Requirement NFPA-72 requires that where in duct smoke detector housings are installed in concealed locations more than 10 ft (3 m) above the finished floor or in arrangements where the detector s alarm indicator is not visible to responding personnel, the detectors have remote alarm indicators. Notice! Do not exceed 500 ft (152 m) between the D344-RT (D307) Remote test/indicator plate and the D340 housing. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire. Bosch Security Systems, Inc. Installation manual F.01U
16 16 en Wiring Duct smoke housing, 2-wire Figure 4.2: D340 to D344-RT wiring 1 Voltage in (+) 2 Voltage out (-) 3 Yellow LED 4 Voltage monitor 5 Ground (-) 6 Remote test 7 Green LED 8 Red LED 9 D D344-RT (D307) 4.2 Wiring to the D344-RL Notice! Do not exceed a distance of 500 ft (152 m) between the D344-RL (D306) Remote indicator plate and the D340. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire F.01U Installation manual Bosch Security Systems, Inc.
17 Duct smoke housing, 2-wire Wiring en 17 Figure 4.3: D340 to D344-RL wiring 1 D340 power card 2 D344-RL (D306) 3 Yellow wire 4 Violet wire 5 Black wire [ground (-)] 6 Terminal 6 is not used 7 Green wire 8 Red wire 4.3 Wiring to the DRA-5 Notice! Do not exceed a distance of 500 ft (150 m) between the DRA-5 Remote indicator plate and the D340 housing. Use 18 AWG (ISO 0.75 mm 2 ) or larger wire. Figure 4.4: D340 to DRA-5 wiring 1 Optional external power (24 VAC/VDC) 2 Remote LED 3 Loop (+) 4 Loop (-) 5 DRA-5 6 White wire 7 Red wire Bosch Security Systems, Inc. Installation manual F.01U
18 18 en Wiring Duct smoke housing, 2-wire 4.4 Wiring to the FACP Figure 4.5: D340 to FACP wiring 1 FACP 2 Alarm initiating loop 3 EOL resistor 4.5 Wiring for external power Notice! Connect the ground wire to the screw on the ground plate when using grounded three-wire AC wiring (see step 8 of the mounting procedure in Mounting the detector, page 9). Figure 4.6: Wiring D340 to FACP and external power 1 FACP 2 Alarm initiating loop 3 External power (24 VAC/VDC) 4 EOL resistor F.01U Installation manual Bosch Security Systems, Inc.
19 Duct smoke housing, 2-wire Testing and maintenance en 19 5 Testing and maintenance 5.1 Testing the installation Verify the airflow to ensure the system is properly operating. Use a manometer to verify the correct velocity pressure readings ranging from 300 ft/min to 4000 ft/min (1.5 m/s to 20 m/s). The pressure differential between sampling tubes is a minimum of 0.01 in. (0.25 mm) of water to a maximum of 1.8 in. (45.7 mm) of water. 1. Check the wiring from the control panel to the last duct detector on each run for proper polarity and continuity. 2. Ensure each run terminates with an EOL resistor as specified by the control panel manufacturer. 3. Apply power to the system, and check for alarms. Note which smoke detectors are in alarm (if any) and shut down the system. Remove these detectors from their duct housing and recheck the duct housing for proper wiring. If the problems persist, replace the affected smoke detectors or swap them with known good units. This determines if the problem is caused by the detector or the duct housing. If there is a system alarm with no detector alarms present, remove all smoke detectors and check the wiring at each duct housing. Pay close attention to the wiring of each EOL resistor. 4. When the system is free of alarms, check each detector to ensure the red LED indicator flashes approximately every 4 sec for the D285DH. This verifies the detector is receiving power and properly operating. 5. Test each detector to ensure it causes a control panel alarm. Reset the control panel after each test. Test the detectors by doing one of the following: Place a magnet against the duct housing s test point notch on the front cover (see the following figure). Figure 5.1: Testing the detector 1 Magnet 2 Test point notch 3 Detector 4 Housing Bosch Security Systems, Inc. Installation manual F.01U
20 20 en Testing and maintenance Duct smoke housing, 2-wire Switch a signal from a D344-RT (D307) Remote test/indicator plate. Notice! When a detector alarms, the red LED indicator activates and latches to the ON position. Clear the alarm before proceeding to the next detector. 5.2 Maintenance 6. You can reset the detector by momentarily removing power. 7. For duct detectors with the D344-RT (D307) Remote test/indicator plate installed, reset by moving the keyswitch to the appropriate position and observing the alarm LED. 8. Check the overall loading of the alarm loop by measuring the voltage across each EOL resistor. This voltage should equal or exceed the minimum specified by the control panel manufacturer. Notice! NFPA Requirement NFPA-72 requires a semi annual visual inspection of detector housings. Clean or replace the tube filters at this time. If replacement filters are needed, order the D344-TF. Notice! Notify all concerned parties before and after completing maintenance on or testing of the fire alarm system. Clean the detector and base annually using a vacuum or with clean, dry compressed air F.01U Installation manual Bosch Security Systems, Inc.
21 Duct smoke housing, 2-wire Specifications en 21 6 Specifications Electrical Current (alarm) Maximum RMS Ripple Power-up time Voltage, operating Dependent on the control panel that must limit the alarm current to 100 ma maximum. 25% of DC input 22 sec maximum 8.5 VDC to 32 VDC from two-wire loop. Optional 24 VDC/VAC from control panel or external supply. D340 with D344-RT, D344-RL, and External Power Loop power External power 8.5 V to 32 V 24 V Condition Alarm Current limit to 100 ma 170 ma in remote test Standby < ma 5 ma Trouble < ma ma D340 with D344-RT, D344-RL without External Power Loop power 8.5 V to 32 V Condition Alarm Current limit to 100 ma Standby < ma Trouble < ma D340 without D344-RT, D344-RL without External Power Loop power 8.5 V to 32 V Condition Alarm Current limit to 100 ma Standby < ma Trouble < ma Environmental Air velocity Relative humidity Temperature, operating 300 ft./min to 4000 ft./min (1.5 m/s to 20.3 m/s) 0% to 95%, non-condensing +32F to +120 F (0 C to +49 C). For UL listed requirements, the operating temperature range is +32 F to +100 F (0 C to C). Bosch Security Systems, Inc. Installation manual F.01U
22 22 en Specifications Duct smoke housing, 2-wire Mechanical Package Dimensions (LxWxH) Product Dimensions (LxWxH) Material Weight Gross Net 18.9 in. x 7.5 in. X 7.8 in. (48 cm x 19 cm x 19.8 cm) 15.5 in. x 4.3 in. x 6.5 in. (39.5 cm x 11 cm x 16.5 cm) High impact fire retardant polymer plastic 4.23 lb. (1.92 kg) 3.84 lb. (1.74 kg) F.01U Installation manual Bosch Security Systems, Inc.
24 Bosch Security Systems, Inc. 130 Perinton Parkway Fairport, NY USA Bosch Security Systems, Inc., 2017 Bosch Sicherheitssysteme GmbH Robert-Bosch-Ring Grasbrunn Germany
Duct smoke housings, 4-wire D341/D341P and D342/D342P en Installation manual Duct smoke housings, 4-wire Notices en 3 1 Notices These instructions cover the installation of the D341/D342 Duct smoke housings
D E Installation Instructions Air Duct Smoke Housing D Installation Instructions.0 Overview. Trademarks ational Fire Alarm Code is a trademark of the ational Fire Protection Association, Inc. ife Safety
D85DH EN Installation Instructions Photoelectric Duct Smoke Detector D85DH Installation Instructions.0 Introduction FCC Notice The D85DH Photoelectric Duct Smoke Detector complies with Part 5 of the Federal
Battery charger modules D8132 and D8132LT en Installation manual Battery charger modules Notices en 3 1 Notices These instructions cover the installation of the D8132 Battery Charger and the D8132LT Battery
Multiplex Eight Input Remote Modules 1.0 Introduction These instructions cover the installation of the D7042/D7042B Eight Input Remote Modules in a fire system supervised by an FPD-7024 Fire Alarm Control
Notification Appliance Circuit Module D192G en Installation guide Notification Appliance Circuit Module Notices en 3 1 Notices These instructions cover the installation of the D192G Notification Appliance
INSTALLATION AND MAINTENANCE DH100ACDCIA & DH100ACDCPA Air Duct Smoke Detector Before Installing ULC standard CAN/ULC-S524-M91 Standard For The Installation Of Fire Alarm Systems should be referenced for
INSTALLATION AND MAINTENANCE INSTRUCTIONS Ionization Air Duct Smoke Detector Before Installing Please thoroughly read the System Sensor Guide for Proper Use of Smoke Detectors in Duct Applications (A05-1004),
Installation Instructions Notice Addressable NAC Output Module D327A These instructions cover the installation of the D327A Addressable NAC Output Module in an analog system controlled by a Bosch D8024,
INSTALLATION AND MAINTENANCE INSTRUCTIONS Air Duct Smoke Detector with Extended Air Speed Range A Division of Pittway 825 Ohio Avenue, St. Charles, Illinois 60174 1-800-SENSOR2, FAX: 60-77-6495 The Innovair
INSTALLATION AND MAINTENANCE INSTRUCTIONS Ionization Air Duct Smoke Detector Before Installing Please thoroughly read the System Sensor Guide for Proper Use of Smoke Detectors in Duct Applications (A05-1004),
INSTALLATION AND MAINTENANCE INSTRUCTIONS DH100LP Air Duct Smoke Detector with Extended Air Speed Range 3825 Ohio Avenue, St. Charles, Illinois 60174 1-800-SENSOR2, FAX: 630-377-6495 The Innovair DH100LP
D EN Installation Instructions Multiplex Dual Input Module D Installation Instructions Notices Notices Figure : D Features These instructions cover the installation of the D Multiplex Dual Input Module
Photobeam 5000 ISC-FPB-W60QS, ISC-FPB-W20QS, ISC-FPB-W200QS en Installation and Operation Guide Photobeam 5000 Table of Contents en 3 Table of contents Introduction 4. About documentation 4.2 Bosch Security
INSTALLATION AND MAINTENANCE INSTRUCTIONS TRN100BPT, TRN100BP, and TRN100BPC Air Duct Smoke Detector with Extended Air Speed Range 825 Ohio Avenue, St. Charles, Illinois 60174 1-800-SENSOR2, FAX: 60-77-6495
D EN Installation Instructions Multiplex Single Input Module D Installation Instructions Notices Notices These instructions cover the installation of the D Multiplex Single Input Module in a fire system,
Installation Manual: PAD100-DUCTR Analog Addressable Duct Detector NOTICE TO THE INSTALLER This manual provides an overview and the installation instructions for the PAD100-DUCTR module. This module is
D350PL INTELLIGENT PHOTOELECTRONIC DUCT SMOKE WITH EXTENDED AIR SPEED RANGE INSTALLATION AND MAINTENANCE INSTRUCTIONS I56-1975-004R Before installing detectors, please thoroughly read the NEMA Guide for
TEST LOG Detector Identification Information Manufacturer and Serial Date Detector Model: Number: Installed: Description of Detector Location: Test Results and Maintenance Data Date Test Test Maintenance
INSTALLATION AND MAINTENANCE INSTRUCTIONS DH400 Air Duct Smoke Detector Before Installing Please thoroughly read System Sensor s Guide for Proper Use of Smoke Detectors in Duct Applications (I56-473-XX),
D EN Installation Instructions Multiplex Input/Output Module D Installation Instructions Notices Notices These instructions cover the installation of the D Multiplex Input/Output Module in a fire system
INSTALLATION AND MAINTENANCE INSTRUCTIONS D2E Duct Smoke Detector Specifications Operating Temperature: 20 to 60 C Storage Temperature: 20 to 60 C Humidity: 0% to 93% Relative Humidity Non-condensing Air
D0A/D/D6AW/D80A/D90 Series EN Installation Instructions / Smoke/Heat Detector Bases EN. D0A/D/D6AW/D80A/D90 Series Installation Instructions.0 Trademarks M Weatherban is a trademark of M. All rights reserved.
D326A/D334A/D339A EN Installation Instructions Point Contact Modules D326A/D334A/D339A Installation Instructions 1.0 Description Notice Use these instructions to install the D326A, D334A, and D339A Point
E-PDD Duct Smoke Installation Sheet E-PDD operation The duct smoke detector's primary purpose is to provide early warning of an impending fire and shut down the HVAC unit in order to prevent smoke from
INSTALLATION AND MAINTENANCE INSTRUCTIONS DH200RPL Intelligent Air Duct Smoke Detector with Extended Air Speed Range 3825 Ohio Avenue, St. Charles, Illinois 60174 800/736-7672, FAX: 630-377-6495 Before
Commercial Series riech Motion Detector en Reference Guide Commercial Series riech Motion Detector able of contents en 3 able of contents 1 Safety 4 Introduction 5.1 About documentation 5. Bosch Security
Photobeam 5000 ISC-FPB-W60QF, ISC-FPB-W0QF, ISC-FPB-W00QF en Installation and Operation Guide Photobeam 5000 Table of Contents en 3 Table of contents Introduction 4. About documentation 4. Bosch Security
INSTALLATION AND MAINTENANCE INSTRUCTIONS DH200PL Intelligent Air Duct Smoke Detector with Extended Air Speed Range 3825 Ohio Avenue, St. Charles, Illinois 60174 800/736-7672, FAX: 630-377-6495 www.systemsensor.com
Cautions and Warnings DO NOT INSTALL ANY SIMPLEX PRODUCT THAT APPEARS DAMAGED. Upon unpacking your Simplex product, inspect the contents of the carton for shipping damage. If damage is apparent, immediately
Installation Guide for AL600ULM Multi-Output Access Control Power Supply Charger Rev. 091800 1 AL600ULM - Multi-Output Access Control Power Supply/Charger Overview: The AL600ULM multi-output access control
FORM ASX-40020 INSTALLATION, OPERATING AND MAINTENANCE INSTRUCTIONS SL-2000 Series Smoke Detectors, Model EXSAA and EXSAB (Ionization), EXSAG and EXSAH (Photoelectric) Air Specialties Express, 448 S. Main
INSTALLATION AND MAINTENANCE INSTRUCTIONS I56-3642-000R DNR-AUS Duct Smoke Detector Specifications Operating Temperature: 20 to 70 C ( 4 to 158 F) 0 C to 49 C (32 F to 120 F) with module installed in the
ISC-PDL1-W18G-H EN Installation Instructions Professional Series Dual Detector 1.0 General Information 1.1 Unlock and remove the cover The ISC-PDL1-W18x Professional Series TriTech Detectors are exceptionally
RF80THS EN Installation Instructions Wireless (RF) Photoelectric Smoke Detectors RF80THS Installation Instructions Trademarks Trademarks Chamber Check is a registered trademark of Bosch Security Systems
Commercial Series riech+ Motion Detector with ISC-CDL1-WA15G, ISC-CDL1-WA15G-CHI, ISC-CDL1-WA15H, ISC-CDL1-WA15K, ISC-CDL1-WA1G, ISC-CDL1-WA1G-CHI en Reference Guide Commercial Series riech+ Motion Detector
Microwave/PIR Intrusion Detector with POPIT Interface ZX970 Installation Instructions 1.0 Specifications Input Power: 9 to 15 VDC, 6 ma nominal (35 ma with LED on) Zonex Current Draw: 500 ma Standby Power:
D96/D97 EN Installation Instructions Long-Range Beam Smoke Detectors D96/D97 Installation Instructions.0 Description FCC Compliance Notice This equipment was tested and complies with the limits for a Class
574-776 Rev. C 4098-9685, -9686, -9688, -9755, -9756 Duct Detector/Sensor Installation Instructions Blank Page Cautions and Warnings DO NOT INSTALL ANY SIMPLEX PRODUCT THAT APPEARS DAMAGED. Upon unpacking
FORM ASX-40021 INSTALLATION, OPERATING AND MAINTENANCE INSTRUCTIONS SM-501 Series Smoke Detectors, Model EXSAC and EXSAD (Ionization), EXSAJ and EXSAK (Photoelectric) Air Specialties Express, 448 S. Main
DS9400 Series EN Release Notes for Firmware V2.07 Fire Alarm Control Panel DS9400 Series Release Notes for Firmware V2.07 Trademarks Trademarks Gentex is a trademark of Gentex Corporation, Fire Protection
Fire Door Release MODEL AR-D2 MANUAL RESET ALARM RELEASE INSTRUCTION MANUAL AR-D2 GENERAL INFORMATION 1. Review all installation instructions, procedures, cautions and warnings contained within this manual
4100U City and Relay Cards Installation Instructions Introduction This publication describes the installation procedure for the following: 4100-6031/6032 City Circuit Cards 4100-6033 Alarm Relay Card Inspecting
AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SM-501 SERIES DUCT SMOKE DETECTORS SM-501-N SM-501-P PRODUCT APPLICATION SM-501 Series duct smoke detectors provide early detection
Installation PS6 SERIES Power Supplies PS6 SERIES Power Supplies c/w Fire Panel Interface, EOL Trigger and Standby Power Option Installation and Specifications Manual ISDPS6_SERIES 08121590 PCN15016 R05/15GR
Fire Door Release MODEL AR-D MANUAL RESET ALARM RELEASE INSTRUCTION MANUAL AR-D GENERAL INFORMATION 1. Review all installation instructions, procedures, cautions and warnings contained within this manual
EN Operators Guide Universal Timer Module Operators Guide Notices EN Copyright Notice Unless otherwise indicated, this publication is the copyright of Bosch Security Systems, Inc. ( Bosch ). All rights
Fire Alarm Control Panels FPD-7024 en Release Notes Fire Alarm Control Panels Table of contents en 3 Table of contents 1 Short description 4 2 Release notes for v1.06.01 5 2.1 New Features 5 2.2 Issues
Installation Guide for AL400ULM Multi-Output Access Control Power Supply Charger R AL400ULM - Multi-Output Access Control Power Supply/Charger Rev. 072500 Overview: The AL400ULM multi-output access control
Deluge Devices 270a 1. PRODUCT NAME VIKING PAR-3 Available since 1991 2. MANUFACTURED FOR: THE VIKING CORPORATION 210 N. Industrial Park Road Hastings, Michigan 49058 U.S.A. Telephone: (269) 945-9501 (877)
Honeywell 12 Clintonville Road Northford, CT 06472 http://www.honeywellpower.com HP600ULM Access Control Power Supply/Charger with Power Distribution Controller PN 52393:A 1/05/06 ECN 04-350 Product Installation
MANUAL RESET ALARM RELEASE BOX (For 100~240VAC or 24VAC or 24VDC) INSTRUCTION MANUAL WARNING 1. CAUTION: Review all installation instructions, procedures, cautions and warnings contained within this manual
Installation Guide for AL300ULM Multi-Output Access Control Power Supply Charger R AL300ULM - Multi-Output Access Control Power Supply/Charger Overview: The AL300ULM multi-output access control power supply/charger
INSTALLATION AND MAINTENANCE INSTRUCTIONS IDP-Zone-6 Six Zone Interface Module BEFORE INSTALLING If the modules will be installed in an existing operational system, inform the operator and local authority
CRSMKKIT002A00 CRSMKSEN002A00 FIELDINSTALLEDSMOKEDETECTORS FOR MEDIUM ROOFTOP UNITS 15 to 25 TONS Installation Instructions TABLE OF CONTENTS PACKAGE CONTENTS... 1 SAFETY CONSIDERATIONS... 1 GENERAL...
AIR PRODUCTS AND CONTROLS You in Control AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SERIES DUCT SMOKE DETECTORS -N 4-Wire, Ionization Type -P 4-Wire, Photoelectric Type
Installation Instructions Model AD-HR Air Duct Monitoring Housing INTRODUCTION The SIEMENS Model AD-HR is a sampling tube, air duct monitoring housing. When used with a compatible smoke detector, smoke
INSTALLATION AND MAINTENANCE INSTRUCTIONS SC-6 Six Supervised Control Module SPECIFICATIONS Normal Operating Voltage: Stand-By Current: Alarm Current: Temperature Range: Humidity: Dimensions: Accessories:
Fire Alarm Acceptance Testing & On-Going Maintenance with The Joint Comm. Standards / Reporting Prepared Especially for : OSFM TEC 2016 Acceptance Testing 11-2008 Agenda Before you begin Completing the
Installation and Maintenance Instructions I56-900-005 MMF-0-6 Six Zone Interface Module SPECIFICATIONS Normal Operating Voltage: 5- VDC Stand-By Current: ma Alarm Current: 40 ma (assumes all six LEDs solid
TrueAlarm Analog Sensing UL, ULC Listed* Addressable Duct Sensor Housings with TrueAlarm Photoelectric Sensor; Available with Multiple Relay Features Compact air duct sensor housing with clear cover to
AIR PRODUCTS AND CONTROLS You in Control AIR PRODUCTS AND CONTROLS INC. INSTALLATION AND MAINTENANCE INSTRUCTIONS FOR SERIES PLENUM DUCT SMOKE DETECTORS NO-FLOW LOW-FLOW SPECIAL APPLICATION -N -P PRODUCT
DS3MX-E-I EN Installation Guide 3 Mini Control Panel DS3MX-E-I Installation Guide 1.0 General Information EN 2 1.0 General Information The DS3MX is a three zone mini control panel, which can be installed
CAUTION Wiring Instructions 0--00-0 (0-0) Power Track Series with Single Point Hold-Open Electromechanical Releasing Device with Multi-Point Hold- Open TO PREVENT ELECTRICAL SHOCK AND EQUIPMENT DAMAGE,